We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byEden Pinkerman
Modified over 2 years ago
© P2Power Solutions Pvt. Ltd P2 Power Solutions Active Filter on DG – Newspaper Printing
An Innovative Engineering Solutions company focused on ensuring high Power Quality for its customers Promoted by a group of IIT Kharagpur graduates State of the art production facilities at Noida & Kharagpur An ISO 9001:2008 certified company Currently delivering products (CE certified) and services catering to the power and energy demands of the industry Dedicated R&D activities in collaboration with IIT Kharagpur to improve and expand the current range of products and services © P2Power Solutions Pvt. Ltd Company Profile
© P2Power Solutions Pvt. Ltd Measurement errors in metering equipments Spurious operation of fuses, circuit-breakers and other protective devices Voltage glitches in computers systems resulting in lost data Electromagnetic interference with TV, radio, communication & telephone Malfunctioning of standby generators and associated AVR control equipments Excessive temperature rise in motors, transformers Failure of Power Factor correction equipments Malfunctioning of precision equipments Low Power Quality - Symptoms
© P2Power Solutions Pvt. Ltd Case Study – Client Details Sector - Newspaper Printing DG Rating- 380kVA Peak Demand- 330A Load Profile- 2x135kW DC drives 15kW Compressor Lighting Loads iTHD- 28% PF- 0.76
© P2Power Solutions Pvt. Ltd Case Study – Client Details The backup Diesel Generator started hunting whenever the load current demand went beyond 200A. The client wasnt able to carry out production in full capacity using the backup generator P2 Power Solutions audited the site and found the current harmonic distortions to be significantly higher than recommended limits The power factor was also low due to which the peak apparent current demand on the DG was high We recommended the installation of a P2 Power Active filter for harmonic mitigation and power factor correction
© P2Power Solutions Pvt. Ltd Load Profile – Apparent Power AF OFF peak kVA: 208 PF: 0.76 AF ON peak kVA: 191 PF: 0.94
© P2Power Solutions Pvt. Ltd Load Profile – Harmonics AF OFF AF ON iTHD: 28% 5 th : 23% 11 th : 6.5% iTHD: 12% 5 th : 10% 11 th : 4.5%
© P2Power Solutions Pvt. Ltd P2 Powers Active Filter reduced the peak kVA demand on the DG by improving the Power Factor without any risk of over compensation It reduced current harmonic distortions to 12% The client was able to run the press at full capacity on DG with our solution Post Installation Condition
© P2Power Solutions Pvt. Ltd Active Filter – Working Principle LOAD 4 wire – Active Filter CT1 CT2 CT3 L1 L2 L3 Supply L1 L2 L3 LN
© P2Power Solutions Pvt. Ltd Iactive Ireactive Iharmonic ILoad Ireactive IharmonicIneutral IAF Active Filter – Working Principle
© P2Power Solutions Pvt. Ltd ID.G IAF ILoad AF Load D.G active reactive + harmonic + neutral Active Filter – Working Principle
© P2Power Solutions Pvt. Ltd Active Filter - Advantage Ultra Fast Response No Risk of Over Compensation No Risk of Resonance Step less Correction Small FootprintProgrammable
Optimum capacity utilization Reduction in Peak current demand Reduced losses Reduced heating Efficient loading © P2Power Solutions Pvt. Ltd Active Filter – Benefits Optimum Utilization of Generator Capacity
© P2Power Solutions Pvt. Ltd COMPARISON SHEET Active Power ConditionerHybrid PF CompensatorSubstitute Technology P2 Power Active FilterP2 Power Hybrid CompensatorAPFC, RTPFC PERFORMANCE Speed< 0.2 milli seconds Response time in seconds TechnologyStepless current compensation Stepped kVAR compensation EffectivenessEffective with highly fluctuating loads Ineffective with fluctuating loads Power Factor (PF) CorrectionTrue PF compensationDisplacement PF compensation Leading/Lagging PFBoth Leading/Lagging PF compensation Lagging PF compensation only Load BalancingNegative sequence current injection No load balancing Harmonic CompensationHarmonic compensationNo Harmonic Compensation Neutral Correction Possible with 4 wire systemNot possibleNot Possible FOOTPRINT Size Advantages Smallest FootprintSmallLargest Footprint COST Installation (per Ampere) ` 3400 ~` 4200 ` 2300~ ` 2800 `1000~`1800 Resource IntensiveSmallest space requirementLow on space requirementsIncreases cost of space Capital CostReduced failures Can increase failures due to resonance Operating CostLow operating cost Recurring cost of capacitor replacement Returns on Investment High High with non fluctuating loads Improved PF Ineffective with fluctuating loads Better voltage profile Introduces voltage transients Reduced failures Can increase failure due to resonance MAINTENANCE Maintenance requirements Modular design Easy Maintenance Spare parts requirements Virtually maintenance free Recurring cost of capacitors/contactors
© P2Power Solutions Pvt. Ltd Thanks!
© P2Power Solutions Pvt. Ltd P2 Power Solutions Neutral Compensation - Hospitality.
© P2Power Solutions Pvt. Ltd P2 Power Solutions Diesel Generator Primer.
POWER QUALITY BACKGROUND & ELEC-SAVER TVSS Power Quality Background Why is it Such a Concern –Many people blame the power utility for degrading power.
QUALITY AND TECHNOLOGY quality of the. POLYLUX has developed a series of electromagnetic filters for the elimination of harmonics named ‘Compensators’.
Power Quality Mike Thornton National Sales Manager.
Presented by. What is Power Factor? Power Factor is the percentage of current delivered from the utility that is needed to perform the actual work. For.
The Bottom Line In Energy Cost Reduction Energy Automation Systems, Inc. EASI.
KW Sentry ® Energy Controller (EC) It is a Desired & a Simple Solution for… RISING ENERGY COSTS It is a Desired & a Simple Solution for… RISING ENERGY.
1 POWER QUALITY -- Bhanu Bhushan -- June, How close is the supply voltage waveform to sinusoidal, and how close are the supply voltage and frequency.
Introduction to ElectroFlow TM System Dhaka, March 8, 2003 Mahmuduzzaman Khan Green Power Canada.
PowaSava Energy Saving Systems A truly green system that is proven to reduce electric energy consumption Managing your energy, saving you money We won’t.
Energy Savings Through Power Factor Correction
Plant Utility System (TKK-2210) 14/15 Semester 4 Instructor: Rama Oktavian Office Hr.: M-F
Power Distribution Harmonics Case Study of 285-3F Chiller Plant Michael W. Harmon Principle Engineer Savannah River Nuclear Solutions, LLC Savannah River.
DC Machine & Transformer Made By: Parallel Operation of Transformer Excitation Phenomenon in Transformer Harmonics in Transformer.
COST EFFECTIVE SOLUTION TO REDUCING YOUR ENERGY BILL’S POWER MASTER Power Master, LLC, 2040 E. Ridge Rd, Rochester, NY, 14622,
Presented by:-SWAGAT KUMAR GURU Regd. No: Roll No:-09EE055 Under the guidance of Ms. Samprati Mohanty (Advisor) 1.
TECHNICAL SEMINAR REPORT-2004 Presented by :- AJAY KUMAR DAS (EE ) POWER FACTOR IN ELECTRICAL ENERGY MANAGEMENT Prepared by: Ajay Kumar Das EE
1 11/17/2015 Power Quality Correction. 2 11/17/2015 Power Quality Correction.
American Control Technologies,Inc Power Factor Correction Technology 1152 West 2400 South Suite ‘C’ Salt Lake City, Utah
Circuit Master Circuit Master™ uses three PROVEN technologies* – Capacitor (reduces DEMAND) – Harmonic Filter (harmful frequencies) – Surge Protection.
F. Ferrandis_SP_ALPHA 2_BLOCK 2_Paper 35_Presentation Barcelona May POWER FACTOR CORRECTION WITHIN INDUSTRIAL SITES EXPERIENCES REGARDING.
REACTIVE POWER COMPENSATION REACTIVE POWER COMPENSATION.
T H E U N I N T E R R U P T I B L E P O W E R P R O V I D E R SineWave - Installation rules.
Management and Organisation of Electricity Use Electrical System Optimisation Belgrade November 2003.
PowerGUARD Energy Saving for inductive loads Saving 8%-15% Protection Power Quality.
InnovationValueTeamwork SHENZHEN INVT ELECTRIC CO., LTD.
Power Engineering Society Chicago Chapter Reactive Power: Sources and Solutions 12 February 2003 David E. Mertz, PE Burns & McDonnell Engineers, Inc.
ND Metering Solutions, Bradford, UK Metering the Supermarkets Leaders through Innovation.
© 2012 MITSUBISHI HEAVY INDUSTRIES – MAHAJAK AIR CONDITIONERS CO., LTD. All Rights Reserved. 22 March 2013 BASIC INVERTER TECHNOLOGY.
Steve Craker K-12 Team Lead Geoff Overland IT and Data Center Focus on Energy Increase IT Budgets with Energy Efficiency.
G.E. UPS Productline. Uninterruptible Power Supplies | 1 Phase Delivering reliable power in a compact footprint LP11 / LP31T / LP31 Series Application.
1 Training Session on Energy Equipment Electricity Presentation from the “Energy Efficiency Guide for Industry in Asia” ©
Power Factor Correction. What is "Power Factor?" Power factor is a measure of how efficiently, or inefficiently, that electrical power is used by a.
Energy Management Practices: Rolling Mills 1. Contents Introduction Energy Intensive Processes & Reduction in Energy Expenditure through Innovative Practices.
Lift Operations Top Drive Lifts Harmonics Filtering Rate Structure and Peak Shaving Energy Efficient Motor Selection Heating and Lighting in.
Siemens Building Technologies Building Technologies Variable Frequency Drives VFD Basics.
The EnergyMizer Power Reduction & Conditioning System ®
ALPHA POWER SOLUTIONS Presented by Eric Solot An Introduction to Power Factor Correction.
KW Energy Solutions, LLC Increasing Energy Efficiency Increasing Energy Effectiveness.
7/08/2002PP.AFD.07 Harmonic Quality1 of 49 Yaskawa Electric America Harmonic Currents, Voltages and Your Building Power System.
SUSTAINABLE ENERGY REGULATION AND POLICY-MAKING FOR AFRICA Module 14 Energy Efficiency Module 14: DEMAND-SIDE MANAGEMENT.
Copyright© 2005 Avaya Inc. All rights reserved Avaya UPS Training powerware.com/avaya.
LP33 Series UPS kVA 400Vac/CE September 2004.
LOGO LINEAR CIRCUIT ANALYSISSAJID HUSSAIN QAZI MEHRAN U.E.T, KHAIRPUR CAMPUS A.C POWERS AND POWER FACTOR.
Push ECO for a greener FUTURE PushECO has developed a selection of effective and easy-to-use energy-saving products which utilizes the.
PRODUCTS TRANSFORMERS ENERGY SAVING TRANSFORMERS (EST) TRANSFORMER RECTIFIER UNITS 3 rd HARMONIC REJECTION TRANSFORMERS (HRT) ULTRA HIGH ISOLATION TRANSFORMERS.
1 Applied Harmonics Control of Harmonics. 2 IEEE Standard Limit harmonic current injections from end users so that harmonic voltage distortion.
© Power Grid Company profile C ONDENSATOR D OMINIT Power Grid Company profile.
VLT ® Low Harmonic Drive. | Property of Danfoss Drives A/S | Tuesday, 15 September 2015 | 2 Acoustic noise Planes, trains, automobiles, busses, construction.
© 2017 SlidePlayer.com Inc. All rights reserved.