Download presentation

Presentation is loading. Please wait.

Published byVaughn Gills Modified about 1 year ago

1
QUALITY AND TECHNOLOGY quality of the

2
POLYLUX has developed a series of electromagnetic filters for the elimination of harmonics named ‘Compensators’. These equipments are based on the cancellation and compensation of magnetic fluxes The main advantage of the Compensator is the absence of electronic components and capacitors. The Compensators are therefore maintenance free, have an extremely long lifetime compared with other types of filters and are compatible with any electrical installation HARMONIC PROBLEMS

3
Phase current Neutral current L1 L2 L3 N Distribution panel HARMONIC PROBLEMS IN OFFICE BUILDINGS UPS Computer equipment in office buildings generate elevated levels of harmonics which cause important problems in the electrical installation The triplen harmonics (3rd, 9th...) are especially harmful as these sum in the neutral conductor and generate a high neutral current causing serious failures and damages in the installation Computer equipment 3rd, 5th, 7th, 9th 3rd, 9th

4
L1 L2 L3 N Distribution panel UPS Computer equipment 3rd, 5th, 7th, 9th 3rd, 9th HARMONIC PROBLEMS IN OFFICE BUILDINGS There is no phase shift between the 3rd harmonic currents therefore in the neutral you get the sum of all 3rd harmonic currents There is a 120º phase shift between fundamental currents, the sum in the neutral is therefore practically zero in a balanced system Phase Currents Neutral Current Why such a high neutral current? Neutral current can be higher than the phase current. For example, having fundamental 100A and 3rd harmonic 60A in each phase, you will have 180A 3rd harmonic in the neutral The neutral current is the sum of all phase currents L1+L2+L3

5
Malfunctioning and failure in computer equipment Overheating of neutral conductors Low efficiency and overheating of UPS, transformers and cables of the installation Tripping of protections without apparent reason Interferences in communication networks Incremented power consumption Low quality electrical energy. Elevated harmonic voltage distortion Elevated neutral – earth voltage High harmonic distortion in the current Excessive levels of 3 rd and 9 th harmonics in the neutral conductor Elevated true RMS current in the phases Low power factor due to harmonics Elevated losses in the electrical installation PROBLEMSCAUSES HARMONIC PROBLEMS IN OFFICE BUILDINGS

6
HARMONIC PROBLEMS IN OFFICE BUILINGS Phase current Neutral current L1 L2 L3 N Distribution panel UPS The C20D Compensator provides a very good cost-filtering relation. It gives a strong reduction of the triplen harmonics and eliminates the overload in the neutral conductor and the high neutral – earth voltage The C20D Compensator has to be installed with the C10D Impedance Adapter to obtain the most optimised filtering Computer equipment 3rd, 5th, 7th, 9th, 15th5th, 7th Compensator C20D 3rd, 9th, 15th COMPENSATOR C10D + C20D Elimination of the 3rd, 9th, 15th harmonic HARMONIC PROBLEMS IN OFFICE BUILDINGS Impedance Adapter C10D

7
HARMONIC PROBLEMS IN OFFICE BUILDINGS COMPENSATOR C10D + C20D Elimination of the 3rd, 9th, 15th harmonic Reduction of the neutral current and neutral – earth voltage up to 75% Reduction of phase currents up to 15% Reduction of voltage and current distortion up to 45% Obtain power factor up to 0,80 FILTERING RESULTS:

8
HARMONIC PROBLEMS IN OFFICE BUILINGS Phase current Neutral current L1 L2 L3 N Distribution panel UPS The C22D Compensator offers elevated filtering of the 3rd, 5th, 7th, 9th, 15th, 17th, 19th harmonics, solving all problems caused by harmonics. The C22D+C10D is used in combination with the C20D + C10D, each of these supplies 50% of the load to be filtered Computer equip. 50% load Compensator C22D COMPENSATOR C10D+C20D AND C22D+C10D Elimination of harmonic 3, 5, 7, 9, 15, 17, 19 HARMONIC PROBLEMS IN OFFICE BUILDINGS Computer equip. 50% load 3rd, 5th, 7th, 9th, 15th Impedance Adapter C10D -5th, -7th 5th, 7th Compensator C20D Impedance Adapter C10D The C20D and C22D have to be installed with C10D Impedance Adapters for optimised filtering

9
HARMONIC PROBLEMS IN OFFICE BUILDINGS Reduction of the neutral current and neutral – earth voltage up to 80% Reduction of phase currents up to 40% Reduction of voltage and current distortion up to 75% Obtain power factor up to 0,95 FILTERING RESULTS: COMPENSATOR C10D+C20D AND C22D Elimination of harmonic 3, 5, 7, 9, 15, 17, 19

10
Phase current Neutral current L1 L2 L3 N Distribution panel UPS The C25D Compensator is totally eliminating the triplen harmonics (3rd, 9th, 15th), avoiding any type of overload in the neutral as well as a high neutral-earth voltage produced by harmonics Thanks to its galvanic isolation, the C25D Compensator represents the ideal solution in case of a high level of 3rd harmonic voltage. Additional advantages are: reduction of the electromagnetic disturbances coming from the supply network, optional voltage adaptation and the possibility to use independent earths as the neutral is isolated from the mains Computer equipment 3rd, 5th, 7th, 9th, 15th5th, 7th Compensator C25D COMPENSATOR C25D Elimination of the 3rd, 9th, 15th harmonic HARMONIC PROBLEMS IN OFFICE BUILDINGS

11
COMPENSATOR C25D Elimination of the 3rd, 9th, 15th harmonic Reduction of the neutral current and neutral – earth voltage up to 90% Reduction of phase currents up to 15% Reduction of current distortion up to 45% Reduction of voltage distortion up to 40% Obtain power factor up to 0,80 FILTERING RESULTS:

12
Phase current Neutral current L1 L2 L3 N Distribution panel UPS The C25D Compensator is available in two versions offering different phase shifts (0º and 180º) for the 5th and 7th harmonic. By combining both versions, elimination of the 3rd, 5th, 7th, 9th, 15th 17th and 19th is obtained Computer equipment 50% load Compensator C25D COMPENSATOR C25D + C25D-180º Elimination of harmonic 3, 5, 7, 9, 15, 17, 19 HARMONIC PROBLEMS IN OFFICE BUILDINGS Computer equipment 50% load 3rd, 5th, 7th, 9th, 15th, 17th, 19th Compensator C25D-180º 5th, 7th, 17th, 19th -5th, -7th, -17th, -19th Distribution panel Distribution panel

13
HARMONIC PROBLEMS IN OFFICE BUILDINGS COMPENSATOR C25D + C25D-180º Reduction of the neutral current and neutral – earth voltage up to 90% Reduction of phase currents up to 45% Reduction of voltage and current distortion up to 85% Obtain power factor up to 0,96 FILTERING RESULTS: Elimination of harmonic 3, 5, 7, 9, 15, 17, 19

14
HARMONIC PROBLEMS IN OFFICE BUILINGS Phase current Neutral current L1 L2 L3 N Distribution panel UPS The C30D Compensator achieves the highest filtering level. It eliminates the 3 rd, 5 th, 7 th, 9 th, 15 th, 17 th and 19 th harmonic and provides additional advantages like: reduction of electromagnetic disturbances, optional voltage adaptation and the use of independent earths Computer equipment 50% load Compensator C30D COMPENSATOR C30D HARMONIC PROBLEMS IN OFFICE BUILDINGS Computer equipment 50% load 3rd, 5th, 7th, 9th, 15th, 17th, 19th Distribution panel Elimination of harmonic 3, 5, 7, 9, 15, 17, 19

15
HARMONIC PROBLEMS IN OFFICE BUILDINGS COMPENSATOR C30D Reduction of the neutral current and neutral – earth voltage up to 90% Reduction of phase currents up to 45% Reduction of voltage and current distortion up to 85% Obtain power factor up to 0,96 FILTERING RESULTS: Elimination of harmonic 3, 5, 7, 9, 15, 17, 19

16
Voltage Current HARMONIC PROBLEMS IN INDUSTRY Transformer Frequency converters and variable speed drives which are usual in today’s industrial installations generate harmonic currents that reduce the quality of the electrical energy The frequency converters generate mainly 5 th and 7 th harmonic currents as well as voltage notches and transients (spikes). Computer 5th, 7th, 11th, 13th Capacitor bank 5th, 7th, 11th, 13th PLC Motor Frequency converter

17
Malfunctioning and failure in electronic equipment Overheating and failure in transformers and cables Overload and failure in capacitor banks Low efficiency of transformers and cables Tripping of protections without apparent reason Overload and failure in motors Interferences in communication networks Low quality electrical energy. Elevated harmonic voltage distortion Notches and transients in the voltage caused by power converters Elevated harmonic distortion in the current Resonance in capacitor banks Elevated true RMS current in the phases Low power factor due to harmonics PROBLEMSCAUSES HARMONIC PROBLEMS IN INDUSTRY

18
Voltage Current HARMONIC PROBLEMS IN INDUSTRY Transformer The RTL line inductors provide the most optimised cost- filtering relation of all harmonic filtering solutions available in the market. It features a very significant filtering of the whole harmonic spectrum Additionally it eliminates the notches and transients generated by the power converters avoiding mal-functioning and failure in electronic devices Computer 5th, 7th, 11th, 13th Capacitor bank 5th, 7th, 11th, 13th PLC Motor Frequency converter Frequency converter Reduction of harmonic 5, 7, 9, 11, 13, 15, 17, 19 RTL line inductor RTL line inductor RTL LINE INDUCTORS

19
LINE INDUCTOR RTL Reduction of phase currents up to 30% Reduction of voltage and current distortion up to 60% Obtain power factor up to 0,93 FILTERING RESULTS: HARMONIC PROBLEMS IN INDUSTRY Reduction of harmonic 5, 7, 9, 11, 13, 15, 17, 19

20
Voltage Current HARMONIC PROBLEMS IN INDUSTRY Transformer The C10F Compensator is used in case a high filtering level is requested. The C10F is installed in such a way that it supplies 50% of the load to be filtered while the other 50% is supplied directly For optimised filtering and elimination of voltage notches, RTL line inductors should be installed as well, especially for power converters above 5 kW Computer 5th, 7th, 17th, 19th Capacitor bank 5th, 7th, 17th, 19th PLC 50% load Elimination of harmonic 5, 7, 17, 19 Compensator C10F COMPENSATOR C10F 50% load -(5th, 7th, 17th, 19th) 5th, 7th, 17th, 19th

21
C10FC10F + RTL Reduction of phase currents up to 20%35% Reduction of voltage and current distortion up to 60%85% Obtain power factor up to 0,950,98 FILTERING RESULTS: HARMONIC PROBLEMS IN INDUSTRY COMPENSATOR C10F Elimination of harmonic 5, 7, 17, 19

22
Voltage Current HARMONIC PROBLEMS IN INDUSTRY Transformer The C20F Compensator achieves the highest protection level for industrial installations, featuring a high filtering level and galvanic isolation of the load. The C20F has two outputs, each supplying 50% of the load For optimised filtering and elimination of voltage notches, RTL line inductors should be installed as well, especially for power converters above 5 kW Computer 5th, 7th, 17th, 19th Capacitor bank 5th, 7th, 17th, 19th PLC 50% load Elimination of harmonic 5, 7, 17, 19 Compensator C20F COMPENSATOR C20F 50% load

23
C20FC20F + RTL Reduction of phase currents up to 20%35% Reduction of voltage and current distortion up to 60%85% Obtain power factor up to 0,950,98 FILTERING RESULTS: HARMONIC PROBLEMS IN INDUSTRY COMPENSATOR C20F Elimination of harmonic 5, 7, 17, 19

24
HARMONIC FILTERING The Advantages High level of harmonic filtering Economic No electronics or capacitors, therefore maintenance free and an extremely long lifetime No generation of high frequency distortions Easy selection, no exhaustive study of the installation is necessary COMPENSATORS

25
HARMONIC FILTERING Installation QUICK SELECTION GUIDE Harmonics Galvanic isolation? 3 rd 9 th 15 th … YES NOC10D + C20D YES NO YES NO Compensators election 3 rd 5 th 7 th 9 th … 5 th 7 th 17 th … C25D-180 C25D-0 C30D C25D-0+C25D-180 C10D+C20D + C10D+C22D C20F C10F Combination with RTLX NO YES Note: For filtering of the 5 th and 7 th harmonics, the load should be divided in two groups (see application guides)

Similar presentations

© 2017 SlidePlayer.com Inc.

All rights reserved.

Ads by Google