We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published bySierra Piersall
Modified over 2 years ago
© P2Power Solutions Pvt. Ltd P2 Power Solutions Neutral Compensation - Hospitality
An Innovative Engineering Solutions company focused on ensuring high Power Quality for its customers Promoted by a group of IIT Kharagpur graduates State of the art production facilities at Noida & Kharagpur An ISO 9001:2008 certified company Currently delivering products (CE certified) and services catering to the power and energy demands of the industry Dedicated R&D activities in collaboration with IIT Kharagpur to improve and expand the current range of products and services © P2Power Solutions Pvt. Ltd Company Profile
© P2Power Solutions Pvt. Ltd Measurement errors in metering equipments Spurious operation of fuses, circuit-breakers and other protective devices Voltage glitches in computers systems resulting in lost data Electromagnetic interference with TV, radio, communication & telephone Malfunctioning of standby generators and associated AVR control equipments Excessive temperature rise in motors, transformers Failure of Power Factor correction equipments Malfunctioning of precision equipments Low Power Quality - Symptoms
© P2Power Solutions Pvt. Ltd Case Study – Client Details Client- 5 star Hotel Sector - Hospitality Peak Load- 950A Neutral Current- 230A iTHD- 14% Triplen Harmonics- 8% PF (uncompensated) Point of Correction-Utility Panel, Lighting loads
© P2Power Solutions Pvt. Ltd Case Study – Client Details The client had 4 utility panels for lighting loads. The peak load in each panel ~180A Neutral current in these panels ~120A To reduce the problem of heavy neutral currents, we recommended the installation of P2 Power Active filter (4 wire configuration) at each utility panel. The results have been summarized in the following slides.
© P2Power Solutions Pvt. Ltd Case Study – Client SLD TransformerUtility Panel #1 P2 Power Active Filter (100A, 4wire) Utility Panel #2 P2 Power Active Filter (100A, 4wire) Utility Panel #3 P2 Power Active Filter (100A, 4wire) Utility Panel #4 P2 Power Active Filter (100A, 4wire)
© P2Power Solutions Pvt. Ltd Unit Off Utility Panel – Lighting Loads Unit On Neutral Current ~ 63% 100A Neutral Compensation Unit
© P2Power Solutions Pvt. Ltd Line Current - Harmonics ~ 33%~ 20% iTHD ~ 33% ~ 26% Triplen ~ 9.5%~ 26%~ 9% ~ 21% Triplen Harmonics add up in the Neutral Filter : OFF Filter : ON
© P2Power Solutions Pvt. Ltd Neutral Current neutral current ~ 42A~ 115A~ 43A Filter : OFF Filter : ON
© P2Power Solutions Pvt. Ltd Neutral Compensation - Filter Output L1 ~ 25A L2 ~ 25A L3 ~ 27A Ln ~ 78A Filter : ON Filter : OFF
© P2Power Solutions Pvt. Ltd Active Filter – Working Principle LOAD 4 wire – Active Filter CT1 CT2 CT3 L1 L2 L3 Supply L1 L2 L3 LN
© P2Power Solutions Pvt. Ltd Active Filter – Working Principle LOAD 4 wire – Active Filter CT1 CT2 CT3 L1 L2 L3 Supply L1 L2 L3 LN The P2 Power Active filter in 4 wire configuration senses the 3 line currents and calculates the neutral current using Kirchoffs Current Law. Once the required neutral current has been calculated, the digital signal processor uses advanced closed loop control logic to compensate the same. This way the heavy neutral current does not reach the main tranformer. The 4 wire configuration can integrate harmonic compensation, stepless power factor correction and active load balancing along with neutral compensation.
© P2Power Solutions Pvt. Ltd Iactive Ireactive Iharmonic ILoad Ireactive IharmonicIneutral IAF Active Filter – Working Principle
© P2Power Solutions Pvt. Ltd Igrid IAF ILoad AF Load I grid active reactive + harmonic + neutral Active Filter – Working Principle
© P2Power Solutions Pvt. Ltd Active Filter - Advantage Ultra Fast Response No Risk of Over Compensation No Risk of Resonance Step-less Correction Small FootprintProgrammable
Optimum capacity utilization Reduction in Peak current demand Reduced losses Reduced heating Efficient loading © P2Power Solutions Pvt. Ltd Active Filter – Benefits
© P2Power Solutions Pvt. Ltd COMPARISON SHEET Active Power ConditionerHybrid PF CompensatorSubstitute Technology P2 Power Active FilterP2 Power Hybrid CompensatorAPFC, RTPFC PERFORMANCE Speed< 0.2 milli seconds Response time in seconds TechnologyStepless current compensation Stepped kVAR compensation EffectivenessEffective with highly fluctuating loads Ineffective with fluctuating loads Power Factor (PF) CorrectionTrue PF compensationDisplacement PF compensation Leading/Lagging PFBoth Leading/Lagging PF compensation Lagging PF compensation only Load BalancingNegative sequence current injection No load balancing Harmonic CompensationHarmonic compensationNo Harmonic Compensation Neutral Correction Possible with 4 wire systemNot possibleNot Possible FOOTPRINT Size Advantages Smallest FootprintSmallLargest Footprint COST Installation (per Ampere) ` 3400 ~` 4200 ` 2300~ ` 2800 `1000~`1800 Resource IntensiveSmallest space requirementLow on space requirementsIncreases cost of space Capital CostReduced failures Can increase failures due to resonance Operating CostLow operating cost Recurring cost of capacitor replacement Returns on Investment High High with non fluctuating loads Improved PF Ineffective with fluctuating loads Better voltage profile Introduces voltage transients Reduced failures Can increase failure due to resonance MAINTENANCE Maintenance requirements Modular design Easy Maintenance Spare parts requirements Virtually maintenance free Recurring cost of capacitors/contactors
© P2Power Solutions Pvt. Ltd Thanks!
© P2Power Solutions Pvt. Ltd P2 Power Solutions Active Filter on DG – Newspaper Printing.
© P2Power Solutions Pvt. Ltd P2 Power Solutions Diesel Generator Primer.
POWER QUALITY BACKGROUND & ELEC-SAVER TVSS Power Quality Background Why is it Such a Concern –Many people blame the power utility for degrading power.
QUALITY AND TECHNOLOGY quality of the. POLYLUX has developed a series of electromagnetic filters for the elimination of harmonics named ‘Compensators’.
Power Quality Mike Thornton National Sales Manager.
F. Ferrandis_SP_ALPHA 2_BLOCK 2_Paper 35_Presentation Barcelona May POWER FACTOR CORRECTION WITHIN INDUSTRIAL SITES EXPERIENCES REGARDING.
1 POWER QUALITY -- Bhanu Bhushan -- June, How close is the supply voltage waveform to sinusoidal, and how close are the supply voltage and frequency.
Power Engineering Society Chicago Chapter Reactive Power: Sources and Solutions 12 February 2003 David E. Mertz, PE Burns & McDonnell Engineers, Inc.
PowaSava Energy Saving Systems A truly green system that is proven to reduce electric energy consumption Managing your energy, saving you money We won’t.
InnovationValueTeamwork SHENZHEN INVT ELECTRIC CO., LTD.
Circuit Master Circuit Master™ uses three PROVEN technologies* – Capacitor (reduces DEMAND) – Harmonic Filter (harmful frequencies) – Surge Protection.
American Control Technologies,Inc Power Factor Correction Technology 1152 West 2400 South Suite ‘C’ Salt Lake City, Utah
PowerGUARD Energy Saving for inductive loads Saving 8%-15% Protection Power Quality.
© 2012 MITSUBISHI HEAVY INDUSTRIES – MAHAJAK AIR CONDITIONERS CO., LTD. All Rights Reserved. 22 March 2013 BASIC INVERTER TECHNOLOGY.
Energy Management Practices: Rolling Mills 1. Contents Introduction Energy Intensive Processes & Reduction in Energy Expenditure through Innovative Practices.
Presented by. What is Power Factor? Power Factor is the percentage of current delivered from the utility that is needed to perform the actual work. For.
Efficiency ranges % with respect to size of thermal plant, age of plant and capacity utilization Step-up to 400 / 800 Kv to enable EHV transmission.
Training manual Lighting concepts – Ballasts and Lighting Controls Ballasts and Lighting Controls Training manual Chapter 3.
Presented by:-SWAGAT KUMAR GURU Regd. No: Roll No:-09EE055 Under the guidance of Ms. Samprati Mohanty (Advisor) 1.
Power Distribution Harmonics Case Study of 285-3F Chiller Plant Michael W. Harmon Principle Engineer Savannah River Nuclear Solutions, LLC Savannah River.
Steve Craker K-12 Team Lead Geoff Overland IT and Data Center Focus on Energy Increase IT Budgets with Energy Efficiency.
Siemens Building Technologies Building Technologies Variable Frequency Drives VFD Basics.
The Bottom Line In Energy Cost Reduction Energy Automation Systems, Inc. EASI.
04/ Benefits of Using a Power Analyzer: Easily Identify Power Quality Issues Generate Detailed Reports Outlining Power Problems Utilize Smart Power.
WELCOME. M/S. E Map Tec. manufactures low voltage Electrical and power panel including motor control centers, Power Control Centers, APFC Panels, VFD.
Energy Savings Through Power Factor Correction
TECHNICAL SEMINAR REPORT-2004 Presented by :- AJAY KUMAR DAS (EE ) POWER FACTOR IN ELECTRICAL ENERGY MANAGEMENT Prepared by: Ajay Kumar Das EE
KW Sentry ® Energy Controller (EC) It is a Desired & a Simple Solution for… RISING ENERGY COSTS It is a Desired & a Simple Solution for… RISING ENERGY.
Plant Utility System (TKK-2210) 14/15 Semester 4 Instructor: Rama Oktavian Office Hr.: M-F
Introduction to ElectroFlow TM System Dhaka, March 8, 2003 Mahmuduzzaman Khan Green Power Canada.
1 Applied Harmonics Control of Harmonics. 2 IEEE Standard Limit harmonic current injections from end users so that harmonic voltage distortion.
3-1 Electrónica de Potência © 2008 José Bastos Chapter 3 Basic Electrical and Magnetic Circuit Concepts Chapter 3 Review of Basic Electrical and Magnetic.
1 of 25 © 2007 Ideal Industries Power Quality At the Plug IDEAL INDUSTRIES Author: Patrick Elliott Application Guide to Power Quality.
Siemens Building Technologies Building Technologies Variable Frequency Drives Bypass Options.
T H E U N I N T E R R U P T I B L E P O W E R P R O V I D E R SineWave - Installation rules.
LP33 Series UPS kVA 400Vac/CE September 2004.
Khaled Mostafa, ABB Electrical Industries, Nov New Trends in process Automation Power of Integration.
Power Analyser Fundamentals Power Analysis and Harmonics.
Prepared By :. Introduction Techniques Used Case Study Advantages Application Conclusion OUTLINE.
1 March 2001 EPCOS FK PM PFC Basics of Power Factor Correction BASICS OF POWER FACTOR CORRECTION.
ND Metering Solutions, Bradford, UK Metering the Supermarkets Leaders through Innovation.
The EnergyMizer Power Reduction & Conditioning System ®
Push ECO for a greener FUTURE PushECO has developed a selection of effective and easy-to-use energy-saving products which utilizes the.
Bryan Underwood Advisor: Prof. Gutschlag Alternating Current Power Factor Monitoring and Correction.
Module- optimizer ECOD. Feigin Electric solution-Module Optimizer “ECOD” New product which allows you to optimize the voltage within the norms laid down.
L.T Circuit Breakers. L.T Circuit Breaker A circuit breaker is an automatically- operated electrical switch designed to protect an electrical circuit.
REACTIVE POWER COMPENSATION REACTIVE POWER COMPENSATION.
1 Engine Protector Safe Rider Vehicle Technologies (Pty) Ltd PO Box 11376, Rynfield South Africa Tel./ fax Cell:
Intro to Pre-Electrical Engineering The fundamentals of electricity and electrical science 1.
The Gas Advantage ! Information contained in this document is the intellectual property of Venus Gas Products & Services (Mysore) Pvt. Ltd. (VGPSPL) and.
© 2017 SlidePlayer.com Inc. All rights reserved.