We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byLeah Graham
Modified over 3 years ago
UPS QUASAR 3-Phase In 3Phase Out 40KVA
Double conversion technology. >>> RealibilityDouble conversion technology >>> Realibility (most reliable topology) Trasformer Less technology >>> Effiency (highest efficiency ) Trasformer Less technology >>> Cost (Lowest cost ) Full Digital Control in one device >>> FPGA comp. Realibility / Flexibility design IGBT-Power Section >>> Effiency / Realibility / Noise HF PWM on Power Devices >>> Effiency / Realibility / Noise Up to 8 UPS working in parallel >>> Power Extension / Redundancy Low THD input Current >>> 12PH / 12PH+5% option
Trafo Less ConfigurationInput > Diode Booster > N.1 IGBT DC-Bus > 750Vdc BUS Inverter > IGBT Bridge
Trafo Less Configuration Desisgner Evaluation
Input Configuration StandardBoost Diodebridge/IGBT rectifier POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
Input Configuration Low DistortionPOWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
Input Configuration Low Distortion
Input Configuration Low Distortion
Quasar KVA 530 950 1220 POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
LCD Display UPS Operating Parameters Command Mode Event & HistoryOperating Language Clock UPS Configuration POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
Internal Battery CompartmentModels: 10 to 40 kVA POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel – For up to 4 strings of 32blocks of 7/9AH
Breaker Layout Models: 10 to 40 kVA Mains Breaker Bypass BreakerMaintenance Bypass Breaker Output Breaker Battery Fuse POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
Component Layout POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
Inverter and Rectifier/boosterComponent Layout Models: 10 to 40 kVA Inverter and Rectifier/booster Power Supply Board Logic Board Monitoring Board POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel –
POWERTRONIX SpA – Headquarter: St.Abruzzi,1 Grezzago (MI/Italy) – tel – 3-Phase In 3Phase Out KVA UPS ATLAS.
LP Series 400V CE GE Consumer & Industrial September 2004.
LP33 Series UPS kVA 400Vac/CE
CL100D series DSP controlled Uninterruptible power supplies.
RACK Mountable & Modular Continuous Power Protection Availability
Copyright © 2008 Rockwell Automation, Inc. All rights reserved. Direct-to-Drive Technology Product Feature Overview.
LP Series 11/31T - Uninterruptible Power Supply Product Management GE Consumer & Industrial Power Protection.
MarsⅡ On-Line UPS Series
UPS Topologies and Multi-Module Configurations
1 Presentation Protect ph ~ / 3 ph ~ transformerless 3 ph ~ / 1 ph ~ 3 ph ~ / 3 ph ~ PROTECT PROTECT PROTECT PROTECT
PowerScale 10-50kVA Ed Maximize your availability.
SitePro UPS 400Vac / CE GE Consumer & Industrial August 2004.
BORRI Company and Products 2012
Delta Confidential DES UPS introduction UPS training June 2006 Markus Schwab.
PV String Monitoring Solution
DS|POWER DS300 series New generation DSP controlled Uninterruptible power supplies.
UPS series PROTECT 1.M Scalable UPS in n+x technology Modularity with double conversion UPS modules True sine wave - output.
1 Powerware kVA The modular, scalable, redundant UPS for midrange applications.
Newave SA, Switzerland – - 28/02/ Conceptpower Modular 80 and 100kVA THE BEST WAY TO PREDICT THE FUTURE IS TO INVENT.
DPA TM UPScale Best-in-class modular UPS for maximum availability.
UPS SG-CE Series 300 kVA. SG-CE Series kVA S1 Sales presentation SAP_SGS_XCE_M16_M30_1GB_V011.ppt 2 Product portfolio CE Marked, 3x380/400/415V.
UPS H series introduction UPS training June 2006 Markus Schwab.
AC Power Supplies Applications –Standby source for “critical” loads (computer) –Primary source when normal ac not available Uninterrupted Power Supply.
TLE Series UPS kW CE. Page 2 TLE Series kVA/kW CE Product Range TLE Series UPS kVA/KW 160,200,320,400 kW High efficiency UPS Introducing.
LP-31 Series Uninterruptible Power Supply Product Management GE Consumer & Industrial Power Protection.
There are three distinct types of isolation in a UPS system: the galvanic isolation between input and output, the input isolation between mains and battery,
LP Series U Technical presentation ISO 9001 UL CUL FCC Class A CE.
POWER PLANT USED IN TELECOM
Chloride Australia Welcomes Stowe Australia To A Power Protection Seminar.
GE Critical Power © 2010 General Electric Company. All Rights Reserved. This material may not be copied or distributed in whole or in part, without prior.
NT series introduction UPS training June 2006 Markus Schwab.
Power Protection Stowe Australia Welcomes QESTnet Data Centre Construction Workshop Seminar Stowe Australia Welcomes QESTnet Data Centre Construction Workshop.
© 2011 Eaton Corporation. All rights reserved. Eaton 9E UPS New Product Introduction October 2011.
INVERTER FOR CCFL ELECTRICAL Requirements
Consult + Engineer + Commission Creating Exceptional Environments © All Rights Reserved January 18, 2011 UNINTERRUPTIBLE POWER SYSTEM (UPS)
Grid Connect Inverters NUER 19
Technical Panel Session. Sunday January 11, DC System Failure Modes IEEE PES SBC Winter Meeting. January 11 – 15, New Orleans, LA Part 3.
Model W Wall Mount Static Transfer Switch. Why choose a model W static transfer switch? Increases power availability. Integrated maintenance bypass. True.
Professor Sung-Yeul Park
© 2011 Eaton Corporation. All rights reserved. Configuring BladeUPS™
AC backup solutions for business continuity. Secure your business, Stay on!
Team LIT Scott Butler Kristin Haeusler Michael Hatt Brock Smith.
Bridge Rectifier Circuit with Working Operation and Their Types.
Model H Free Standing Static Transfer Switch. Why choose a model H static transfer switch? Increases power availability. True solid state. Rugged, reliable.
AEON 4000 Including the SMPS 4000 rectifier and the AEON Gold Alarm & Monitoring Unit.
Electronics for PS and LHC transformers Grzegorz Kasprowicz Supervisor: David Belohrad AB-BDI-PI Technical student report.
A DSP based on on-line UPS R.Padamaja G.Mamatha Reddy EEE EEE S.V.C.E S.V.C.E BY.
DC/DC Switching Power Converter with Radiation Hardened Digital Control Based on SRAM FPGAs F. Baronti 1, P.C. Adell 2, W.T. Holman 2, R.D. Schrimpf 2,
© 2017 SlidePlayer.com Inc. All rights reserved.