We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byMike Wagg
Modified over 2 years ago
111 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Overview Testing Troubleshooting Certification Documentation
222 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Steps Testing Troubleshooting Certification Documentation Testing Testing verifies that all wires are working so that the customer does not find that there are problems later Testing is for functionality, that is, it determines if the wire can carry the signal from end to end
333 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Common Test Errors Wire-mapping errors – Wires in a multi-pair cable do not terminate at the appropriate contacts in the connector at the far end Opens – Wires in cables fail to make a continuous path from end to end. This is usually due to improper termination or breakage. Occasionally it is due to faulty cable Shorts – Wires in cables touch each other, thus shorting the circuit Split pairs – Wires are mixed among pairs Phases of testing
444 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase - Common Test Errors
555 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Common Testers tone generators cable and jack testers telephone test sets multimeters TDR and OTDR Two methods of testing Channel Test Link Test Channel Test The channel test goes truly end-to-end from the workstation or telephone to the device in the TR The channel test includes the line cord from the jack to the user equipment
666 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Channel Test Goes from workstation/phone to the TR device The channel test includes the patch cord from the patch panel to the communications equipment Officially eliminated by TIA/EIA-568-B.1 Link Test Tests cable from the wall back to the patch panel There are two types: basic and permanent Only permanent link test is acceptable per TIA/EIA- 568-B.1 Permanent Link Test Excludes the cable portions of the adapters, but includes the mated connection at each end
777 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Permanent Link Test Allows for a consolidation point, which is desirable for open office cabling installations and is therefore more practical The problems that should be tested for are foreign voltage, shorts, reversals, split pairs, and crosstalk Testing for Foreign Voltage A voltage that does not belong on the wire Sources of foreign voltage can be dangerous Cross-connects, insulation failures, static electricity Inductive currents formed by routing signal wires too close to wires carrying large voltages Multimeters can test for foreign voltage.
888 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Testing for Shorts A short is formed when the two wires in a pair touch each other Tests to determine if there is a short measure the continuity or resistance between the wires Make these measurements with an ohmmeter using a low-resistance scale Testing for Reversals A cable tester is needed to determine reversals A reversal occurs when the tip (or ring) side of a pair is terminated on the ring (or tip) position at the opposite end of the wire
999 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Testing for Split Pairs Split pairs happen when wires are mixed Test for splits with an ohmmeter & tone generator
10 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Testing for Crosstalk Crosstalk occurs when the signal from a transmitting pair is coupled to the receiving pair or other pairs in the cable Cable testers are used to detect crosstalk
11 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Fiber-optic Testing Fiber-optic cables are tested using a calibrated light source and an optical power meter to measure the loss in the cable being tested
12 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Testing Grounding Systems Grounding systems tests are generally performed using a special purpose instrument - a megger Megger checks performance of grounding and bonding The NEC states that if the grounding systems resistance to ground is 25 ohms or greater The installer has to add a second ground rod Reading of 5 ohms or less is considered commercially acceptable Troubleshooting Copper Connections Hard faults Problems that make communication virtually impossible Are relatively easy to identify and clear Opens, split pairs, and shorts are examples of hard faults
13 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Troubleshooting Copper Connections Intermittent faults Come and go and cause problems such as: Dropped packets Packets with errors Often, these problems are caused by crosstalk Troubleshooting Fiber-optics Most problems are found with the connectors Fiber connector end faces can become scratched: With repeated connecting and disconnecting Dirt and dust on the end faces of the connectors can also add attenuation that will impede a fiber- optic signal
14 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Certification The certification process forms a baseline measurement for the cabling system It allows the installer to say unequivocally that at a certain day and time the cables performed Any later change in cable performance must be attributable to some cause it will be easier to troubleshoot Minimum Test Results To pass, cables must meet the minimum grade test results The difference between the actual test results and the minimum test results is known as headroom. If the results show lots of headroom There should be less cable maintenance needed in the future More tolerant of poor grade patch cords and equipment cables
15 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Certification Testing is for functionality, that is, it determines if the wire can carry the signal from end to end. Certification, or performance testing, is a statement about cable performance Performance test systems usually use a receiver on the far end that communicates over the wire to the main test unit. Category 5e cable is tested at 100 MHz and Category 6 at 250 MHz. Performance testing per TIA/EIA-568-B
16 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase - Certification Testing
17 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Common Test Specifications Specified Frequency Range Attenuation Near End Crosstalk (NEXT) Return Loss Propagation Delay Delay Skew Documentation After the cabling has been tested and certified, documentation is created These are called as-built documents As-builts show the client and future technicians exactly the layout of the cable installation.
18 © 2002, Cisco Systems, Inc. All rights reserved. Finish Phase Documentation These are called as-built documents It may vary from the original plans since obstacles or problems may have occurred during installation Diagrams showing the cable runs, locations of outlets, and identity of each outlet should be created and presented to the client
1 © 2004, Cisco Systems, Inc. All rights reserved. CCNA 1 v3.1 Module 4 Cable Testing.
1 © 2003, Cisco Systems, Inc. All rights reserved. CCNA 1 v3.0 Module 4 Cable Testing.
DCN286 Introduction to Data Communication Technology Session 5.
1 Guide to Network Cabling Fundamentals Chapter 8.
1 Telecom Cabling Testing and cable certification.
Network+ Guide to Networks, Fourth Edition Chapter 12 Troubleshooting Network Problems.
1 Discovery 2, Ch 4 Notes. 222 Cabling Standards Standards ensure that networks perform to expectations US—IEEE & ANSI/TIA/EIA Canada—CSA (Canadian Standards.
Waves Measuring Frequency The amplitude of an electrical signal represents height and is measured in volts. The period is the amount of time to complete.
1 Troubleshooting. 2 Introduction This section provides you with the necessary skills to effectively troubleshoot the DIRECTV System.
Semester 1 v CCNA 1 Module 4: Cable Testing.
Measuring Frequency The amplitude of an electrical signal represents height and is measured in volts. The period is the amount of time to complete one.
Bits (0s and 1s) need to be transmitted from one host to another. Each bit is placed on the cable as an electrical signal or pulse. On copper cable the.
Cisco 1 - Networking Basics Perrine. J Page 19/3/2015 Chapter 3 Which of the following correctly describes the type of signal that the network media carries?
1 © 2004, Cisco Systems, Inc. All rights reserved. CCNA 1 v3.1 Module 3 Networking Media.
1 CISCO NETWORKING ACADEMY PROGRAM (CNAP) SEMESTER 1/ MODULE 4 Cable Testing.
Cable Testing. Introduction Networking media is the backbone of network. Networking media is the backbone of network. Inferior quality of network cabling.
NESCOT CATC1 Cable Testing CCNA 1 v3 – Module 4. NESCOT CATC2 Waves 1. The _________ of the waves is the amount of time between each wave, measured in.
Copyright CCNA 1 Chapter 4, Part 1 Cable Testing By Your Name.
1 © 2004, Cisco Systems, Inc. All rights reserved. CCNA 2 v3.1 Module 1 WANs and Routers.
+ Straight-Through Cable Construction Lab 4. + Data Transmission In data transmission system, the transmission medium is the physical path between transmitter.
Pursuit of Better testing Instrument Let's go in the grandway......
1 Telephone Connection. 2 Introduction The section instructs you on how to install a required phone line to every receiver.
Troubleshooting Tools Cable Performance Testers Voltage Event Recorders Butt Set Crossover Cable Tone Generator & Locator Multimeter Cable Continuity Tester.
1 © 2004, Cisco Systems, Inc. All rights reserved. CCNA 1 v3.1 Module 7 Ethernet Technologies.
SUNY Ulster Cisco Semester 1 Unit 4 – Cable Testing K. Wick CCAI.
EQUIPO 2 Cabling system components. The cable Horizontal Cables Horizontal cables run between a cross-connect panel in a wiring closet and a wall jack,
Testing. Permanent Link Definition –Horizontal cabling extending from the wall plate to the cross connect WORK AREA TELECOMMUNICATIONS CLOSET Horizontal.
Physical Transmission Media 8 5/9/ Modified by: Brierley.
Lecture 8 Cable Certification & Testing:. Cable Distribution Cable Distribution Equipment UTP (Unshielded Twisted Pair) UTP Cable Termination Tools UTP.
Software and Hardware Tools COMP 316. Software Tools.
1 CCNA SEMESTER 1 V 3.0 CHAPTER 4 – Cable testing.
Landing and Taxi Lights Anti-collision Lights Navigation Lights Cockpit and Cabin Lights Instrument Panel Lights Click on a System Link to Start.
Old Telephone cabling 4 wire RJ 11 Color code Used in commercial and residence NEW.
Physical Transmission Media Chapter 8. Objectives In this chapter, you will learn to: Identify the characteristics of wireline transmission Describe the.
Switches Antonio González Torres. Hierarchical Network Design The design of larger LANs includes identifying the following: An access layer that connects.
Oct-03 ©Cisco Systems CCNA Semester 1 Version 3 Comp11 Mod4 – St. Lawrence College – Cornwall Campus, ON, Canada – Clark slide 1 Cisco Systems CCNA Version.
Click to edit Master subtitle style Chapter 18: Software and Hardware Tools Instructor:
TRANSMISSION MEDIA T.Najah Al-Subaie Kingdom of Saudi Arabia Prince Norah bint Abdul Rahman University College of Computer Since and Information System.
Sep-03 ©Cisco SystemsCCNA Semester 1 Version 3 Comp11 Mod4 – St. Lawrence College – Cornwall Campus – Clark slide 1.
LOCATION OF CABLE FAULTS INTRODUCTION: Cable fault is referring to something that occurs current can’t flow smoothly. It is because open circuit or short.
CCNA 1 Module 4 Cable Testing. 2 Waves Frequency: Frequency: –the number of waves per second Period: Period: –the amount of time that it takes to complete.
1 Introduction to Network. 2 Computer Networks Primary purposes of network is to increase productivity. The minimum requirements for setting up a network.
111 © 2002, Cisco Systems, Inc. All rights reserved. Trim out phase steps Cutting cables to length Labeling cables Dressing cables Terminating cables Installing.
1 © 2004, Cisco Systems, Inc. All rights reserved. CCNA 1 v3.1 Module 6 Ethernet Fundamentals.
Many Roads To Home. LAN Roads UTP STP Coaxial Fiber Optics.
NETWORK DESIGN Customer requirements Network topologies Cable choice Hardware TSB 75 TSB72.
1 © 2004, Cisco Systems, Inc. All rights reserved. CCNA 1 v3.1 Module 11 TCP/IP Transport and Application Layers.
Chapter 12: Troubleshooting Networking Problems Network+ Guide to Networks Third Edition.
OBJECTIVE INTRODUCTION OF OPTICAL FIBER CONSTRUCTION OF OPTICAL FIBER PRINCIPLE OF OPTICAL FIBER TYPES OF OPTICAL FIBER OPTICAL FIBER FAULTS.
© 2016 SlidePlayer.com Inc. All rights reserved.