Presentation on theme: "Presented By – The Grapple Hook Group Distributors of Iron Ox Products"— Presentation transcript:
1Presented By – The Grapple Hook Group Distributors of Iron Ox Products Corrosion Conversion and Prevention Program for UST Sumps & Leak DetectorsPresented By – The Grapple Hook GroupDistributors of Iron Ox ProductsAll Products areNonflammableMinimal Power ToolsRequired
2Corrosion on Copper as well. Good idea to remove water Before TreatmentCorrosion on Copper as well. Good idea to remove water
3Multiple types of corrosion Before Treatment –Multiple types of corrosion
4Before Treatment –Removal of blue oxidation on copper is important. Brush lightly. Wear mask.
6Or Sometimes Full of Wet Corroded Muck! Before Treatment –Or Sometimes Full of Wet Corroded Muck!
7Before You Start – Supplies and Tools Gloves Mask Multiple RagsSafety Glasses Vest Cup of Water Coveralls
8Before You Start – Supplies and Tools Non Sparking Brass Scrapers & available at Grainger
9Before You Start – Supplies and Tools Non Sparking Brass Brushes – Available at Auto & Builder Supply Stores
10Before You Start – Supplies and Tools Disposable Paint Brushes - 1” and 3” and Disposable Paint Cups.Do not put chemical back into bottle. C Stores have cups if you forget.
11Before You Start – Supplies and Tools To Speed Up Spraying – We recommend using a Milwaukee SprayerModel A. If you plan to use, you will need portable air supply. Sprayer is used for final coat of 24/7 Plus - Corrosion Inhibitor and Lubricant. If no sprayer is available , product can be brushed.
12Before You Start – Supplies and Tools One Pint of Iron Ox Steel Curtain Per STP Motor & AssemblyOne Can of Iron Ox 24 / 7 Per STP Motor & Assembly
13Before You Start – Supplies and Tools Six to Seven Feet of ¾ or 1” PVC Pipe for each sump. + PVC cutting tool
14Before You Start – Supplies and Tools One Iron Ox Vapor Emitter Bulb and Four 6-8” plastic tie wraps per stick
15Barriers set with cones and tape Typical Station ViewBarriers set with cones and tape
16Open Lid Safely / Remove Water Ventilate Sump Area - Expose Air.Remove any water bottom with rags or hand pump.
17Check with Safety Manager for Company Policy and Gear For Confined Space Entry. Any power tools used should be UL approved & Intrinsically Safe
18Removing Rust with Brass and Plastic Scraper and Brush Double Click If NecessaryDebris on floor can be removed manually or approve d vacuum
19Removing Rust with Brass and Plastic Scraper and Brush cont. Segment 2 -Double Click If NecessaryJust The Gross and Rust Scale – Ok to leave Surface Rust.
20Post Scraping with all loose rust / flakes removed. Wipe down with damp cloth after scraping to remove any dust / debris.Remove debris from floor with rag.
21Rust Conversion Process with Steel Curtain Segment 1 -Double Click If NecessaryApply Steel Curtain liberally to all metal surfaces in sump area with paint brush. Only metal components with rust will turn dark. One pint per STP assembly.
22Rust Conversion Process with Steel Curtain Segment 2 -Double Click If NecessaryTwo Coats Recommended. Wait 30 Minutes Between Coats.Be Patient! Let it dry.
23Post Rust Conversion. Rusted Surfaces Have Turned Darker. Steel Curtain only affects areas with rust. No harm to plastics or other surfaces. No Polymer to interfere with future maintenance procedures.
24Apply 24/7 Plus Corrosion Inhibitor Treatment With Sprayer @ 80psi + Double Click if NecessaryTwo Coats. Apply first coat with paint brush on all Metal components. Wait minutes . Apply second Coat with from sprayer with wide mist pattern from above the STP. Use entire contents for one STP / Leak Detector.
25Surfaces will have light tackiness and wet look. ResultsSurfaces will have light tackiness and wet look.
26Surfaces will have light tackiness and wet look. ResultsSurfaces will have light tackiness and wet look.
27Surfaces will have light tackiness and wet look. ResultsSurfaces will have light tackiness and wet look.
28Throw away old bulb. Non Hazardous. Vapor Emitter StickAttached Vapor Bulb to PVC Pipe. Make sure bulb is as close to lid as possible.Lean or tie in place. Mark date on bulb and replace with new one in 6 months.Throw away old bulb. Non Hazardous.
30Maintenance and Inspection Wet Look will wear off first. Expect darker colored components.24/7 Corrosion Inhibitor will eventually wear off due to environment.
31Maintenance and Inspection We recommend repeat treatment in six months at time of vapor bulb replacement.2nd Treatment will be much easier, less labor than first.Wipe down copper tube with 24/7 at every opportunity.
32Questions 813-877-4665 www.theironox.com The Grapple Hook GroupHome of the Iron Ox Productsfor Maintenance, Repair and OverhaulDisclaimer:The suggested solutions for converting and preventing rust with Iron Ox products are provided as excellent solutions based on lab / field testing and customer experiences. However, no guarantee as to any outcome is offered. Additionally, the buyer accepts all responsibility for the end results concerning paint adhesion. The Grapple Hook Groups, its owners, employees or other entities involved will not be held liable for any coating failures, corrosive material use or disposal of any materials involved.Consult With the MANUFACTURER of your COATINGS and follow their pre-paint prep instructions to the letter.Consult with your safety director to ensure all safety policies and procedures are followed when using Iron Ox Products.Because the variables of rust corrosion and applying coatings on metal are so extreme, The Grapple Hook Group can make no guarantee of success as to the longevity of the system against rusting. However, by following the guidelines provided, you will go a long way to having metal surfaces correctly prepared for rust control and top coatings.GHG /042214