Presentation on theme: "TIS Bus Connection Topology & Addresses Course 20 Minutes Test 10 Minutes TIS Training Program 2012, Rev 1.1 www.tissmarthome.com."— Presentation transcript:
TIS Bus Connection Topology & Addresses Course 20 Minutes Test 10 Minutes TIS Training Program 2012, Rev 1.1
What is TIS Bus? What is Bus?
What is TIS Bus?
TIS Smart Bus is Advanced RS485 Topology Using Cat5e Data Cable to connect between all TIS devices
Street No 1 BLD 1 BLD 2 BLD 3 TIS Smart Bus Network The Data is moving in Bus (Cat5e cable) between Buildings (Devices)
We can use any Topology to connect…
Each device has unique address Each address consist of Subnet ID & Device ID
Device ID 1 Subnet ID 1 Device ID
On Subnet ID 1 Device ID Device ID 101
Subnet ID Device ID 91 Subnet ID Device ID 52 Subnet ID Device ID 51 Subnet ID Device ID 124 OnNo Power Off OnOff Loster Dim 60 % Apajor Dim 40 % Lamp Dim 80 %
All TIS devices work with 24 V so how many power supply we need? TIS Power Supply output is 24V DC /1.5A Average consumption for each device is 50 mA So we need 1 power supply for every 30 devices in the same network
How many devices can be connected to the same TIS-BUS Line? We can connect maximum 60 Devices
How we can connect more than 60 devices in same network? You can use TIS-IP-Port gateway to connect different networks This is the recommended way to connect different apartments, offices or hotel rooms