Download presentation

Presentation is loading. Please wait.

Published byZoie Surgener Modified over 3 years ago

1
Infiltration/Ventilation HVAC 7a CNST 305 Environmental Systems 1 Dr. Berryman

2
Infiltration Types of heat losses? Types of heat gains?

3
Calculating Infiltration Crack method Air change method Effective leakage-area method Sensible BH = 1.08 x T x CFM Latent BH = 0.68 x G x CFM Equations w/ Air Constants

4
Air Crack Method Divide by 60 min for CFM Lower pressure differentials mean tighter construction

5
Crack Example (winter) EXAMPLE Given: 3 o 5 o Double Hung Window No added humidification IA conditions: DB=75 o F OA conditions: DB=-5 o F Medium Construction How many BTUH are lost due to frame wall infiltration?

6
Air Change Converts equation to cubic feet Equals one room change Designer will use 0.3 to 2.0 room changes per hour Occupancy Climatic condition (i.e. winter vs. summer) Construction (tight or loose) Least accurate of the three methods BH sens = 1.08 x T x CF 60

7
Air Change Example EXAMPLE Given: 20’ x 60’ x 10’ room Winter - 0.35 RCH No added humidification IA conditions: DB=75 o F OA conditions: DB=-5 o F How many BTUH lost due to infiltration?

8
Ventilation + pressure 1600 CFM 200 CFM 1400 CFM FA SA RA

9
Calculating Ventilation CFM per Person Use ASHARE chart Room Air Change per Hour 0.5 – 2.0 RCH Sensible BH = 1.08 x T x CFM Latent BH = 0.68 x G x CFM Equations w/ Air Constants

10
Determining Ventilation Requirements Determinates Building Application # Occupants

11
Ventilation - CFM per Person EXAMPLE Given: 2000 SF Coin Operated Laundry Winter design No added humidification IA conditions: DB=75 o F OA conditions: DB=-5 o F How many BTUH lost due to ventilation?

12
Ventilation - Room Change Given: 2000 SF Coin Operated Laundry - 10’ walls Winter design 2.0 RCH No added humidification IA conditions: DB=75 o F OA conditions: DB=-5 o F How many BTUH lost due to ventilation?

13
Summer Conditions - CFM per Person Given: 2000 SF Coin Operated Laundry 15 CFM/person summer IA conditions: DB=75 o F 40%RH OA conditions: DB= 95 o F WB=80 o F How many BTUH gained due to ventilation? BH sens = 1.08 x T x CFM BH lat = 0.68 x G x CFM

14
In Class: Given: 2000 SF Coin Operated Laundry 10’ walls 1.5 RCH IA conditions: DB=75 o F 40%RH OA conditions: DB= 95 o F WB=80 o F How many BTUH gained due to ventilation? Summer Conditions - Room Change

15
Next Time Heat Gains Chapter 2.6 – 2.8 (Toa)rooflights equipme nt floor exteriorwall glass solar glass conductio n infiltration people

Similar presentations

Presentation is loading. Please wait....

OK

Environmental Controls I/IG

Environmental Controls I/IG

© 2018 SlidePlayer.com Inc.

All rights reserved.

Ads by Google

Ppt on group development phases Ppt on business etiquettes training programs Download ppt on biomass power plant Interactive ppt on the writing process Ppt on various operations on sets and venn diagrams Ppt on mbti personality test Ppt on pi in maths lesson Ppt on generating electricity by walking Ppt on solar based traffic light control system Ppt on centring ig