Presentation on theme: "Submitted by debadatta patro (090101eer024)"— Presentation transcript:
1 Power Factor Correction using Power Factor Transducer and Microcontroller Submitted bydebadatta patro (090101eer024)madhu sudan samantray bhuyan (090101eer041)g. Anil kumar (090101eer059)Anil kumar sahu (090101eer012)subhransu kumar sahu (090101eer001)project guideAsst. prof. suchita lakra
2 INTRODUCTIONPower factor (PF) is a measurement by which we can measure the efficiency of the electrical equipments as well as ac electric power system on the basis of electrical energy consumption. It determines power quality.Due to inductive loads, the apparent power becomes greater than the real power that increases the phase difference between voltage and current. So, the power factor drops below unity and the system becomes less efficient.Our project deals with correcting the power factor to make it closer to unity.
3 WHAT IS A POWER FACTORIt Is a measure of how effectively the current is being converted into useful work outputIt Is a good indicator of the effect of the load current on the efficiency of the supply system.Power factor = cosѲ, where ‘Ѳ’ is the phase anglepower factor=P/S, where p=real power, s=apparent power.
5 Cause of low power factor Since power factor is defined as the ratio of KW to KVA, we see that low power factor results when KW is small in relation to KVA.Inductive loads are responsible for high KVAR resulting a low power factor.KVA KVAR KVAKVAR KW KWSo , inductive loads (with large KVAR) result in low power factor.
6 What Is Power Factor Correction? A high power factor is generally desirable in a transmission system to reduce transmission losses .Generally power factor correction is for two type of loads :linear load, Non linear load.Power factor correction brings the power factor of an AC power circuit closer to 1 by supplying reactive power.
7 (Block Diagram of the existing system) Overview of the SystemIncandescent bulbsPower supplyPower lineCurrent transformerCapacitor bankSwitching drivesPower factor transducer: LTPFUrelayMicrocontrollerAtmega 32LCD display(Block Diagram of the existing system)(Block Diagram of the proposed system)
8 Equipments required for hardware implementation Power Factor TransducerPower Factor Transducers measure the power Factor in 1 Phase and 3 Phase electrical systems. The resulting output signal is directly proportional to the system power factor. The output can be connected to Recorders for display, analysis or control.In our project we are using a power factor transducer of model: LTPFU.
9 Configuration Of Power Factor Transducer CircuitI/P VoltageI/P CurrentFrequencyOutputAux. PowerABCY1 f 2 W3 f 3 W3 f 4 WOther110V220V1A5A50Hz60HzDEF0~10mA DC0~20mA DC4~20mA DC0~5V DC1~5V DC0~10V DCNAC 110/220V (Dual Power)DC 24VDC 110VDC 125V* Self-Power Mode
10 MICROCONTROLLERHere we are using a atmega16 microcontroller
11 CAPACITOR BANKWhen power factor improvement capacitor banks are designed and arranged properly, the PF correction scheme becomes efficient. The capacitor bank is comprised of individual capacitor elements.salient features of PF correction capacitor banks are extremely high reliability with self-healing capabilities; capable of controlling the requirement of kVARs to achieve PF as close as unity; compact, efficient and long service life; protected against over-voltage, over-current, over temperature, switching surges.
15 Here soldering were done on 16 Here soldering were done on 16*2 LCD for interface with microcontroller 16 pin of LCD were connected with AVR burner.Pin1-GND,Pin2-VCC,Pin3-GND,Pin4-PD0.4(5th pin PORT D), Pin5-PD0.5(6th pin PORT D), Pin6-PD0.6(7th pin PORT D), Pin7-PA0.0(1th pin PORT A), Pin8-PA0.1(2th pin PORT A),Pin9-PA0.2(3th pin PORT A), Pin10- PA0.3(4th pin PORT A), Pin11- PA0.4(5th pin PORT A),Pin12- PA0.5(6th pin PORT A), Pin13- PA0.6(7th pin PORT A), Pin14PA0.7(8th pin PORT A),Pin15-VCC- (9th pin PORT C), Pin16- GND-(10th pin PORT A)Connection were done as per the function of the LCD and microcontroller . Then we build the program in AVR-4 Software with no error and we got the output