Presentation on theme: "ANSI SIA CP-01 CONTROL PANEL STANDARDS COMBATING ALARM DISPATCHES."— Presentation transcript:
ANSI SIA CP-01 CONTROL PANEL STANDARDS COMBATING ALARM DISPATCHES
ALL ASSOCIATIONS PARTICIPATED AIREF Alarm Industry Research & Education Foundation CSAA Central Station Alarm Association NBFAA National Burglar & Fire Alarm Association SIA Security Industry Association CANASA Canadian Alarm Security Association
UL COMPLIANT UL Local Burglar Alarm UL 611 & Central Station BA UL Mercantile & Bank UL Fire Protective Signals UL 985 & Household Fire, BA UL Digital BA Communicators UL Residential Systems
WHY NEW STANDARDS? Meeting of Industry Professionals... Need for further reductions... Need for standardization... Based on known solutions... Based on HIGH user error... MOST Panel Manufacturers Participated!
False Dispatch Elimination Most User Errors - During Entry/Exit: User Arms - Exits - Re-enters… User Arms - Fails to Exit in time… User Arms - Building still Occupied… User Arms - Exits Through Wrong Door… User Arms - Fails to exit at all...
False Dispatch Elimination Most User Errors - During Entry/Exit: User enters - forgets code… User enters - fails to disarm within delay time… User enters - unfamiliar with system... User enters - through the wrong door… non-delayed no keypad - unable to hear prewarn
New Control Panel Standards Exit Delay: Default - 60 seconds (Min 45 sec) Progress Annunciation - different sound the last 10 seconds of delay AUTOMATIC RESTART of exit delay, ONCE! (upon re-entry) Recent Closing - signal sent if alarm within 2 minutes of Exit time expiration
New Control Panel Standards Exit Delay: Fail to exit - arms all zones STAY MODE Remote annunciation supported by panel Exit Time DOUBLED if user disables pre-warning. (dealer cannot disable globally) Exit Error - Immediate local alarm...
New Control Panel Standards Entry Delay: Default 30 seconds (Minimum 30 sec) Progress Annunciation - different sound last ten seconds of delay Pre-Warning Silenced - after 1st digit code entry Cancel Message window after abort window - 5 minutes
ALL BURG ZONES… ABORT WINDOW Burglary - default 30 sec* (15-45 range) Fire - default No delay Hold-up/Tamper - No delay LOCAL ALARM STILL SOUNDS - ONLY COMMUNICATION IS DELAYED *May disable by zone or zone type!
New Control Panel Standards Wireless/Remote accommodations Inadvertent activation's - Minimized (No Single Action buttons… Hold-up, Panic, Fire, Etc) System Acknowledgement - Exterior Option to eliminate: (default - on) Exit Time Delay Stay Mode upon failure to exit
New Control Panel Standards Other New Features: Upon Power Restoral 60 second settling out period.. NO ALARM SIGNALS TRANSMITTED! Swinger shut-down - default - 1 (MAX-2) Will reset after 48 hours - with no trips NEW (OPTIONAL)- Swinger Trouble signal sent after 1st trip Universal disarming sequence - code only
New Control Panel Standards Other New Features: Cross Zoning features available 1+ duress Eliminated! *70 Call Waiting - 2nd Call Option… Test in Progress Features Preset Automatic Arming - Audible ! New Simple Instruction Card!
New Standards & UL UL - Testing to the new standards... New UL sticker on panels... LISTED DESIGN EVALUATED BY UL IN ACCORDANCE WITH SIA CP-01 Control Panel Standard - Features for False Alarm Reduction
What YOU can do... Verification Call - always… Customer Training - continuously.. Simplified operating instructions Written monitoring procedure Videos - Tips on reductions Billing/Newsletter reminders
What you can do... In House Employee Training Pro-Active Approach (Set-up Team) Use new standards on existing panels Call customers within 24 hours of event Service promptly! Target 10 Worst Offenders Monthly Use Central Station Software to Track! Be an ACTIVE Member of the Local, State and National Associations