Presentation on theme: "Summary of NFPA 101 Interior Finish Requirements"— Presentation transcript:
1 Summary of NFPA 101 Interior Finish Requirements Because of the significant impact wall and ceiling finishes and furnishings, such as drapes, curtainsNFPA 101: Chapter 10 addresses interior finish requirements
2 Interior Finish Classes Interior finishes are broken down into three classifications:Class A Interior Wall and Ceiling Finish (flame spread 0-25, smoke development 0-450)Class B Interior Wall and Ceiling Finish (flame spread 26-75, smoke development 0-450)Class C Interior Wall and Ceiling Finish (flame spread , smoke development 0-450)Where the standards require C, A or B can also be usedWhere the standards require B, A can also be used
3 Interior FinishesInterior Wall and Ceiling FinishInterior wall and ceiling finish materialsLess than 1/28” not considered interior finish if they meet Class A testing requirementsFixed or moveable walls and partitions, paneling, wall pads, acoustical materials, insulation, etc. are considered interior finishes.Floor finishes
4 Floor Finish ClassesInterior floor finishes are characterized by their critical radiant flux ratingsCritical Radiant Flux is the level of radiant heat energy on the floor covering system at the most distant flame out pointIt provides a basis for estimating one aspect of flame-spread behavior for floor covering systemsClass I: critical radiant flux of not less than .45 W/cm2Class II: critical radiant flux of not less than .22 W/cm2 but less than .45 W/cm2
5 Standards for Specific Materials Textile Wall and textile ceiling materialExpanded vinyl wall and expanded vinyl ceiling materialsCellular or Foamed PlasticMetal ceiling panels
6 Contents and Furnishings Upholstered furnitureResistant to cigarette ignitionChar length standards (1 ½”)MattressesChar length standards (2”)Heat release
7 Industrial OccupancyInterior Finishes in industrial occupancies can be Class A, B, or CIn exit enclosures, interior finishes shall be Class A or Class BFloor finishes in exit enclosures including stair treads and risers shall be not less than Class II.
8 Protecting OpeningsDepending upon the purpose walls will have different fire rating requirementsLoad bearing, non-load bearing, interior, exterior, exit corridor, etc.Doors used in these openings must meet applicable fire ratings
9 Determining Fire Ratings of Doors To determine the appropriate fire rating for a door you need to know the following:The purpose the wall/partition is servingFire barrierExit access corridorHorizontal exitFire rating of the component
10 Smoke Management Smoke Management Smoke management systems are designed to modify, dilute, redirect, or otherwise influence the movement of smoke in a building experiencing a fire, but not necessarily to control it or limit its movement.
11 Smoke ControlSmoke control systems limit and control the movement of smoke during a fireThe most common approach involves pressurizing the areas on either side of the compartment where the fire is located and exhausting the fire area.This is referred to as dynamic smoke control.This method creates a pressure sandwich which tends to move air (and thus smoke) from the protected areas towards the fire and move smoke out of the fire area.While this does introduce fresh oxygen to the fire area, most systems are aimed at protecting the occupants and equipment in the adjacent compartments to allow evacuation and to allow firemen to gain clear access to the fire to extinguish it
12 Dynamic Smoke ControlInstead of shutting down the ventilation fans when smoke is detected, dynamic smoke management systems often require the fans to continue to run.Strategically located dampers open or close to channel HVAC air into selected areas, creating high and low pressures as required.Areas favored for pressurization are stair towers. lobbies, hallways, and, in some instances, elevator shafts.
13 Static Smoke ControlConventional shutdown systems seek to contain smoke by limiting air movement.Once smoke is detected, ventilating fans shut down, and low leakage dampers throughout the system close to inhibit smoke passage.
14 Smoke Curtains and Fire Curtains Smoke curtains prevent the movement of smoke and heat from one area to another in a fire by channeling or containing the smoke and heat.Fire curtains are vertical fire barriers that separate and protect escape routes.Automatic curtains are comprised of fire resistant fabric fixed to a steel roller which is driven by an internal electric motor.