Presentation on theme: "RADIANT HEATING SYSTEMS ECOFILM an electric heating foil."— Presentation transcript:
RADIANT HEATING SYSTEMS ECOFILM an electric heating foil
Convection: Radiators, fires, heaters etc.
ECOFILM F –Floor heating foil
ECOFILM F -Radiant heat
20 º 22 º 24 º 26 º 2.5 m ECOFILM C –ceiling radiant heating
The floor surface must be level and clean. Cut a channel in the concrete for the floor probe. It should lead to where the thermostat is to be placed. Put the floor probe into the channel and run the connection wire to the wall. Secure the probe with tape. Concrete sub floor
Lay hardboard on top of the floor boards to achieve a smooth, clean level surface. Put the floor probe into the channel and run the connection wire to the wall. Secure the probe with tape. Cut a groove in the board for the floor probe. Timber sub floor
Use Depron to insulate the floor. Secure the Depron using 2 tape. Cut a hole in the Depron where the floor probe is to be positioned.
The ECOFILM F can now be rolled out across the floor covering the area that is to be heated. Remember not to place the element under fixed objects in the room. The Flexel element is joined up in parallel leading to the point where the thermostat is to be placed. Install the thermostat making connections from the element and the floor probe.
A polythene sheet is laid over the top of the element. This can be replaced by the manufacturers recommended material if required for warranty. The laminate floor is laid on top of the polythene.
ECOFILM C –Ceiling heating foil
Install metal joists (5) to the ceiling structure (6), lay thermal insulation min. 50mm (4), spread the heating foil ECOFILM C (3), lay PE foil as moisture stop (2), carry out wiring, cover with plasterboard (max. 16 mm thick) (1) ECOFILM C – ceiling heating foil
Fenix Crimping Tool Check calibration on a regular basis Equipment required for ceiling installation
Top ViewSide ViewSnapped together Fenix) t type connector cover AMP Termifoil (Fenix) Clear, 150C rated, polyester tape (Fenix)
Non – Heating Leads (Fenix) PVC ETFE 1.5 mm² single core 1.5 mm² Single core, double insulated, ETFE/ flexible PVC, Blue or black colour.
Check the roll for any damage including folds and creases. Damaged areas must be discarded
Seal both ends of element with Fenix tape
Fold AMP and close with thumb and forefinger Insert leads Insert element into crimp
Make 2 diagonal applications with the flat edge of the crimping tool on the crimp. Make application with the W section of the crimping tool on the cylindrical ferrule.
Equipment required for floor installation ) Crimp connectors 2) Vulkanized tape MASTIC 3) Polyester insulation tape 4) Connection cables 1,5 mm2: black and blue colour 5) Crimping tool
1) Check the roll for any damage including folds and creases. Damaged areas must be discarded 3) Seal both ends of element with Fenix tape 4) Insert leads. Insert element into crimp. Fold AMP and close with thumb and forefinger.
5) Crimp connector must be insulated by MASTIC strip.
Introduce lower section of t connector cover. Equipment required for ceiling installation
When crimp is in place introduce top section of t cover
Snap connector covers together. Repeat for all copper conductor end pieces.
ECOFILM Set An electric heating foil - DIY product - an effective system for laminate and wooden floor warming and heating. - The set contens: Strip of heating foil Ecofilm of 600-mm total width (heating active width getting 550 mm), of the 60W/m 2 or 80W/m 2 surface input, supplied in rolls of different lengths as the customer requires and in accordance with the laying plan. Couple of additional insulating discs (using in case of heating foil length cutting and need copper electrode strips insulation) Instruction manual
ECOFILM Set INSTALLATION STEPS The ECOFILM Set is installed directly under the laminate (floating) or timber floors in the same way as the standard ECOFILM F606 or F608 foils offered since many years. The floor structure is recommended as follows: 1 - laminate floating floor 2 - PE film 3 - ECOFILM F heating film 4 – INSULATION (Depron, Saarpor- Polyplan) 5 - baase concrete
ECOFILM Set LAY-OUT SAMPLE
ECOFILM Set INSTALLATION STEPS 1.The connection of the ECOFILM Set with connecting leads prepared in advance is just the great advantage because the installer or even the user by himself may very easily. Just the final electrical measuring and connection (interconnection of all connecting leads in the installation box and thermostat connection) shall be entrusted to a professional possessing the necessary qualification
ECOFILM Set PRODUCT RANGES
ECOFILM MHF An electric heating foil under mirror - an effective system for keeping the mirror completely steam-free. - ECOFILM MHF is connected to the lighting circuit so that it is activated when the light is switched on. - Self-adhesive side of ECOFILM MHF is placed on back of mirror after peeling of protective release paper. Mirror WITH a heating foil ECOFILM MHF Mirror WITHOUT a heating foil ECOFILM MHF
ECOFILM Products ranges Note :Types F 606 and 608 for the wooden and lamiante floors – there cannot be use heating film with higher output !!!
Recommended regulation method ECOFILM C – analogue or digital room thermostat FLASH 25614EBERLE RTR-E 6202EBERLE Instat 2 EBERLE Instat 6-2 ECOFILM F – analogue or digital thermostat with floor sensor FENIX Therm 100 M&S ECO M/z(s)2 EBERLE Instat 6-3 EBERLE Instat 8 MICROLINE OCD 1999 H
ECOFILM advantages vs metal foil ECOFILMMETAL FOIL - suits to ceiling construction (width of 40, 50 and 60 cm) - simply cut to length according to requested dimensions - easy electric connection (in parallel for direct return to the room thermostat position) - if Ecofilm will be damaged it can be simply repaired - limited modular sizes (making stocking difficult and transport difficults) - individual termination into separate termination boxes - in case of damage metal foil rerequires complete replacement
YOUR A RIGHT PARTNER IN AN ELECTRIC HEATING SYSTEMS Contact us : FENIX Trading s.r.o. Slezska Jesenik, Czech Rep. Tel/Fax: /303 Web: