Presentation on theme: "Cathy Beahm Technical Assistance Specialist NH DES, Air Resources"— Presentation transcript:
1Cathy Beahm Technical Assistance Specialist NH DES, Air Resources New England Healthcare Engineers’ Society Recently Promulgated National Air Quality Regulations and How They Will Impact HospitalsCathy BeahmTechnical Assistance SpecialistNH DES, Air Resources
2Presentation Overview Air Emission BasicsBoiler RegulationsEmergency Generator RegulationsQuestions
3Air Emission Basics Criteria Pollutants Products of combustion: Nitrogen Oxides (NOx), Carbon Monoxide (CO), Sulfur Dioxide (SO2), Particulate Matter (PM) and Volatile Organic Compounds (VOC) or Non-methane hydrocarbons (NMHC)The Clean Air Act (CAA) requires EPA to identify sources of Hazardous Air Pollutants (HAPs) and develop regulations to limit these emissions.Boilers, Incinerators and Reciprocating Internal Combustion EnginesHazardous Air PollutantsList of 188 HAPs from the CAA can be found at
4Air Emission Basics (continued) EPA has developed both Major and Area Source National Emission Standards for Hazardous Air Pollutants (NESHAPs) promulgated under 40 CFR 63Major vs. Area SourcesMajor sources have the Potential to Emit (PTE) greater than tpy individual HAP and 25 tpy combined HAPsArea sources are facilities that are not major sources - who do not have PTE above these levels either due to permit limitations or design capacity.Majority of Sources in NH are Area Sources
5Hospital SpecificsHospitals in NH are area sources of HAPs based on the boilers and emergency generators currently permitted.To determine your facility’s classification, you must calculate your PTE of HAPs from all devices at your facility (boilers, emergency generators, ethylene oxide sterilizers, etc.)Hospitals typically burn traditional fuels in their boilers (coal, biomass, oil or gas) as opposed to solid waste.Presentation today is not covering HIMWI (none in NH – few, if any, in New England).Almost 97% of the hospitals in NH burn fuel oil alone or in combination with natural gas.One facility in NH operates 2 small (<10 MMBtu/hr) biomass boilers.Over 70% have at least one boiler >10 MMBtu/hr.
7Overview of recent EPA actions affecting boilers EPA issued three rules that reduce emissions of HAPs:NESHAP for Industrial, Commercial, and Institutional Boilers and Process Heaters (40 CFR 63, Subpart DDDDD) (“Boiler MACT”)NESHAP for Area Sources: Industrial, Commercial, and Institutional Boilers (40 CFR 63, Subpart JJJJJJ) (“Boiler Area Source Rule”)Section 129 NSPS and Emission Guidelines for Commercial and Industrial Solid Waste Incinerators (CISWI)EPA also issued a final rule that defines “solid waste”Necessary to determine whether a source must meet boiler standards or an incinerator standardExplain delegation issue and the lead agency on each rule.
8Overview of recent EPA actions affecting boilers (cont.) ScheduleProposals signed on April 29, 2010Published in the Federal Register on June 4, 2010Promulgations signed on February 21, 2011 (Court-ordered)Published in the Federal Register on March 21, 2011Effective Date: May 20, 2011EPA has initiated reconsideration of certain aspects of the boiler and CISWI rulesSome of the comments raise difficult technical issues that would benefit from additional public involvement.Stakeholders have petitioned for reconsideration of other issues.StayOn May 18, 2011, EPA delayed the effective date of the Boiler MACT and CISWIBoiler Area Source Rule and Solid Waste Definition are in effect even during the reconsideration process.Facilities need to comply with rules as they were promulgated.Key points:June 4, 2010 is the date that distinguishes “existing” devices from “new” devices.March 21, 2011 is the date that establishes future due dates for notifications, work practice standards.May 20, 2011 was the effective date of the Area Source Boiler Rule.Boiler MACT and CISWI are stayed and Boiler MACT, Area Source Boiler Rules and CISWI are under reconsideration.EPA’s Tentative Schedule for Reconsideration: Proposal due out October, 2011; Final April, 2012
9Focus of Today’s Presentation: Boiler Area Source Rule Area Sources burning Traditional Fuel (oil)
10Boiler Area Source Rule Rule is broken down based on:Boiler size:Small (<10 MMBtu/hr)Large (≥10 MMBtu/hr)Fuel type:Coal-fired unitsBiomass-fired unitsOil-fired unitsBoiler Construction:Existing prior to June 4, 2010New or reconstructed after June 4, 2010Note:NH has not taken delegation of the Boiler Area Source Rule. Therefore, the information presented here is based on the regulation and conversations that have taken place with EPA, Headquarters and Region 1, and are in some cases based on interpretations by EPA and DES as we have tried to work through various issues not clearly defined in the existing rule. In addition, any requirements in the existing rule may be changed in the future as a result of the reconsideration process. It is up to the source to review the regulation as it pertains to their specific situation, comply with the regulation as promulgated and keep informed of any changes.
11Are any boilers not subject to this subpart? Any boiler covered by another part of 40 CFR 63Any boiler covered by CISWIHazardous waste boilersA boiler that is used specifically for research and development.This exemption does not include boilers that solely or primarily provide steam (or heat) to a process or for heating at a research and development facility.Any boiler that is used as a control device to comply with another Subpart of 40 CFR 63, provided that at least 50 percent of the heat input to the boiler is provided by the gas stream that is regulated under another subpart.Key points:Gas-fired boilers (as defined) are not subject to the Area Source Boiler Rule.Dual fired boilers (e.g. NG/#2 FO) that don’t meet or are unwilling to meet the gas-fired boiler definition would be subject to the rule when burning liquid fuel. (Existing: work practice standards; New: emission limitations and work practice standards)If a gas-fired boiler switches to dual fuel or liquid fuel only in the future, this constitutes fuel switching and the device would be considered “new”. At that point, the device would have to meet the oil-fired emission limit as well as tune-up.
12Are any boilers not subject to this subpart? (continued) A hot water heater as defined in this subpart.Hot water heater means a closed vessel with a capacity of no more than 120 U.S. gallons in which water is heated by combustion of gaseous or liquid fuel and is withdrawn for use external to the vessel at pressures not exceeding 160 psig, … and … water temperatures exceeding 210°F.A gas-fired boiler as defined in this subpart.Gas-fired boiler includes any boiler that burns gaseous fuels not combined with any solid fuels, burns liquid fuel only during periods of gas curtailment, gas supply emergencies, or periodic testing on liquid fuel. Periodic testing of liquid fuel shall not exceed a combined total of 48 hours during any calendar year.Key points:Gas-fired boilers (as defined) are not subject to the Area Source Boiler Rule.Dual fired boilers (e.g. NG/#2 FO) that don’t meet or are unwilling to meet the gas-fired boiler definition would be subject to the rule when burning liquid fuel. (Existing: work practice standards; New: emission limitations and work practice standards)If a gas-fired boiler switches to dual fuel or liquid fuel only in the future, this constitutes fuel switching and the device would be considered “new”. At that point, the device would have to meet the oil-fired emission limit as well as tune-up.
13Fuel Switching Rule Provisions A boiler is a new affected source if you commenced fuel switching from natural gas to solid fossil fuel, biomass, or liquid fuel after June 4, 2010.If you intend to switch fuels, and this fuel switch may result in the applicability of a different subcategory or a switch out of Subpart JJJJJJ due to a switch to 100 percent natural gas, you must provide 30 days prior notice of the date upon which you will switch fuels.If you own or operate an industrial, commercial, or institutional boiler and would be subject to this subpart except for the exemption for units covered by the CISWI rules, and you cease combusting solid waste, you must be in compliance with this subpart on the effective date of the waste to fuel switch.If you intend to commence or recommence combustion of solid waste, you must provide 30 days prior notice of the date upon which you will commence or recommence combustion of solid waste.
15Emission Limits for Area Source Boilers Oil and Biomass Only SubcategoryEmission LimitsPM (lb/MMBtu)10 – 30 MMBtu/hr>30 MMBtu/hrNew Biomass0.070.03New OilExisting Biomass-Existing OilNote:The emission limit of 0.03 lb/MMBtu limit for PM from new devices is the same emission limit in the NSPS for new >30 MMBtu/hr boilers.
16Energy Assessment [40 CFR 63, Subpart JJJJJJ - Table 2] One-time energy assessment performed by a qualified energy assessor.An energy assessment completed on or after January 1, 2008, that meets or is amended to meet the energy assessment requirements satisfies the energy assessment requirements.The energy assessment must include:A visual inspection of the boiler system,An evaluation of operating characteristics of the facility, specifications of energy using systems, operating and maintenance procedures, and unusual operating constraints,Inventory of major systems consuming energy from affected boiler(s),A review of available architectural and engineering plans, facility operation and maintenance procedures and logs, and fuel usage,A list of major energy conservation measures,A list of the energy savings potential of the energy conservation measures identified,A comprehensive report detailing the ways to improve efficiency, the cost of specific improvements, benefits, and the time frame for recouping those investments.EPA is hoping to come out with more detailed guidance on the energy assessment portion of the rule soon.NH DES is also going to be conducting Workshops on the rules and expanding the website with information and links to documents to aid facilities in complying with the rules, including but not limited to lists of qualified energy assessors, notification forms, Fact Sheets and Frequently Asked Questions.
17Tune-up Requirement [63.11223(b)] As applicable, inspect the burner, and clean or replace any components of the burner as necessary (you may delay the burner inspection until the next scheduled unit shutdown, but you must inspect each burner at least once every 36 months).Inspect the flame pattern, as applicable, and adjust the burner as necessary to optimize the flame pattern. The adjustment should be consistent with the manufacturer’s specifications, if available.Inspect the system controlling the air-to-fuel ratio, as applicable, and ensure that it is correctly calibrated and functioning properly.Optimize total emissions of carbon monoxide. This optimization should be consistent with the manufacturer’s specifications, if available.
18Tune-up Requirement [63.11223(b)] (continued) Measure the concentrations in the effluent stream of carbon monoxide in parts per million, by volume, and oxygen in volume percent, before and after the adjustments are made (measurements may be either on a dry or wet basis, as long as it is the same basis before and after the adjustments are made).Maintain onsite and submit, if requested, biennial report containing the following information:The concentration of CO in the effluent stream in ppm, by volume, and oxygen in volume percent, measured before and after the tune-up of the boiler.A description of any corrective actions taken as a part of the tune-up of the boiler.The type and amount of fuel used over the 12 months prior to the biennial tune-up of the boiler.If the unit is not operating on the required date for a tune-up, the tune-up must be conducted within one week of startup.
19Existing Biomass and Oil-Fired Boilers Notifications and Reporting TimelineExisting Biomass and Oil-Fired Boilers<10 MMBtu/hr≥10 MMBtu/hrInitial Notification of Applicability ReportBy September 17, 2011Initial Compliance DateFirst biennial tune-up by March 21, 2012One Time Energy AssessmentNABy March 21, 2014Notification of Intent to Conduct a Performance TestInitial Compliance TestingInitial Notification of Compliance Status ReportBy July 19, 2012By July 19, 2012 for initial tune-up;By July 19, 2014 for one-time energy assessmentContinuing Compliance –Biennial Tune-upSubsequent tune-ups should be completed no later than 25 months after the previous tune-upContinuing Compliance –Triennial TestingBiennial Compliance Certification Report – Biennial Tune-upPrepare first report by March 1, 2015 with subsequent reports prepared biennially by March 1stAnnual Compliance Certification ReportSample Initial Notifications and Notification of Compliance Status forms are located on the EPA and DES websites.
20New Biomass and Oil-Fired Boilers Installed between 6/4/10 and 5/20/11 Notifications and Reporting TimelineNew Biomass and Oil-Fired Boilers Installed between 6/4/10 and 5/20/11<10 MMBtu/hr≥10 MMBtu/hrInitial Notification of Applicability ReportBy September 17, 2011Initial Compliance DateFirst biennial tune-up by May 20, 2011One Time Energy AssessmentNANotification of Intent to Conduct a Performance TestAt least 60 days before performance stack test is scheduled to beginInitial Compliance TestingBy May 20, 2011Initial Notification of Compliance Status ReportWithin 60 days of completing the performance testContinuing Compliance –Biennial Tune-upSubsequent tune-ups should be completed no later than 25 months after the previous tune-upContinuing Compliance –Triennial TestingNo more than 37 months after the previous testBiennial Compliance Certification Report – Biennial Tune-upPrepare first report by March 1, 2012 with subsequent reports prepared biennially by March 1stAnnual Compliance Certification ReportPrepare first report by March 1, 2012 with subsequent reports prepared annually by March 1stSample Initial Notifications and Notification of Compliance Status forms are located on the EPA and DES websites.
21New Biomass and Oil-Fired Boilers Installed after 5/20/11 Notifications and Reporting TimelineNew Biomass and Oil-Fired Boilers Installed after 5/20/11<10 MMBtu/hr≥10 MMBtu/hrInitial Notification of Applicability ReportWithin 120 days of startup of the boilerInitial Compliance DateFirst biennial tune-up upon startupOne Time Energy AssessmentNANotification of Intent to Conduct a Performance TestAt least 60 days before performance stack test is scheduled to beginInitial Compliance TestingWithin 180 calendar days of startupInitial Notification of Compliance Status ReportWithin 60 days of completing the performance testContinuing Compliance –Biennial Tune-upSubsequent tune-ups should be completed no later than 25 months after the previous tune-upContinuing Compliance –Triennial TestingNo more than 37 months after the previous testBiennial Compliance Certification Report – Biennial Tune-upPrepare first report by March 1st of the year immediately following startup of the boiler with subsequent reports prepared biennially by March 1stAnnual Compliance Certification ReportPrepare first report by March 1st of the year immediately following startup of the boiler with subsequent reports prepared annually by March 1stSample Initial Notifications and Notification of Compliance Status forms are located on the EPA and DES websites.
22Notification and Reporting Guidance Sample Initial Notifications, Notifications of Compliance Status, and Tune-up Guidance and Example Recordkeeping Forms for Area Sources can be found under “Implementation Tools” at:Send copies of paperwork toEPA Region 1 US Environmental Protection Agency5 Post Office Square, Suite 100, Mail code: OES04-2,Boston MAAttention: Air Clerkand in the case of NH sourcesNew Hampshire Department of Environmental ServicesAir Resources Division29 Hazen DriveP.O. Box 95Concord, NHAttention: Section Supervisor, Compliance Bureau
23Contacts Regulation Contact Office Telephone Number E-mail Boiler MACT Brian ShragerUSEPA Headquarters - OAQPS(919)Susan LanceyUSEPA – Region 1(617)Boiler Area Source RuleJim Eddinger(919)CISWIToni JonesUSEPA Headquarters - NRCG(919)Solid Waste DefinitionGeorge FaisonUSEPA Headquarters – RCRA(703)Jui-Yu HsiehUSEPA - Region 1(617)
24Design gross heat input (BTU/hr) Permitting GuidanceNH Permit ApplicabilityNH Permit ApproachesIndividual Permits (Temporary, State, Title V)DeviceDesign gross heat input (BTU/hr)FuelExternal Combustion Device (Boiler)≥10,000,000Gaseous fuel, LPG, distillate fuel (#2 fuel oil) or diesel fuel, any combination≥4,000,000#4 fuel oil≥2,000,000Solid fuel, residual fuel (#6 fuel oil), used oil, any combination
26Overview of recent EPA actions affecting emergency generators EPA issued three rules that regulate emissions from reciprocating internal combustion engines (RICE):NSPS for Stationary Compression Ignition (CI) Internal Combustion Engines (40 CFR 60, Subpart IIII) (“Quad I”)NSPS for Stationary Spark Ignition (SI) Internal Combustion Engines (40 CFR 60, Subpart JJJJ) (“Quad J”)NESHAP for Stationary Reciprocating Internal Combustion Engines (RICE) (40 CFR 63, Subpart ZZZZ) (“Quad Z”)
27How do these three rules compare How do these three rules compare? (Information is for comparison purposes only)RegulationFuel TypeManufacture Date of Engine1Pollutants RegulatedQuad IDieselBeginning in model year 2007 and laterNOx, PM, CO, NMHCQuad JGasolineQuad ZBoth fuelsAll enginesHAPs1 Manufacture date varies with size of engine. See rule for more accurate information on the dates.
28NSPS for Stationary CI Internal Combustion Engines (“Quad I”) Affects new, modified, and reconstructed stationary CI engines [diesel fired engines]Initially promulgated on July 11, 2006Amendments signed June 8, 2011Applies to diesel engines (compression ignition).
29Who is Subject to Quad I?Manufacturers of 2007 model year or later stationary CI engines <30 liters/cylinder displacementModel years differ for fire pump engines ( depending on size)Owners/operators of enginesConstructed (ordered) after 7/11/2005 and manufactured after 4/1/2006Constructed after 7/1/2006 for fire pump enginesModified/reconstructed after 7/11/2005
30Quad I - Emission Standards Phased in over several years and have Tiers with increasing levels of stringencyOutput-based, units of g/kW-hr (g/HP-hr)Pollutants: NOx, PM, CO, NMHCSOx reduced through use of low sulfur fuelModeled after EPA’s standards for non-road and marine engines
31Quad I - ComplianceManufacturers must certify 2007 model year and later engines with a displacement <30 liters/cylinderCertification = EPA Certificate of ConformityOwner/operator of emergency generators complies by:Purchasing certified engineInstall, configure, operate and maintain engine per manufacturer’s instructions or manufacturer-approved proceduresInstall a non-resettable hour meter prior to startupOwner/operator operates unit with ultra low sulfur fuel after October 1, 2010 (<15 ppm sulfur content)
33Quad I - Notification and Recordkeeping Emergency Generators not required to submit an initial notification.Maintain documentation from the manufacturer certifying that the engine complies with the applicable emission standards of Quad IRecord the time of operation of the engine and the reason the engine was in operation during that time.Keep records of the sulfur content of the fuel burned in the device.
34NSPS for Stationary SI Internal Combustion Engines (“Quad J”) Affects new, modified, and reconstructed stationary SI engines [gas fired engines]Initially promulgated on January 18, 2008Amendments signed June 8, 2011Applies to gas fired engines (spark ignition).
35Who is Subject to Quad J? Manufacturers of stationary SI engines: ≤25 HP and manufactured on/after 7/1/2008>25 HP, gasoline or rich burn LPG, manufactured on/after 7/1/2008 (on/after 1/1/2009 for emergency engines)>25 HP, not gasoline or not rich burn LPG, voluntary certified engines manufacture on/after7/1/2007 >500 HP (except lean burn 500≤HP<1,350)1/1/2008 lean burn 500≤HP<1,3507/1/2008 <500 HP1/1/2009 emergency engines
36Who is Subject to Quad J? (continued) Owners/operators of stationary SI engines:Constructed after 6/12/2006 and≥500 HP manufactured on/after 7/1/2007 (except lean burn 500≤HP<1,350)Lean burn 500≤HP<1,350 manufactured on/after 1/1/2008<500 HP manufactured on/after 7/1/2008Emergency >25 HP manufactured on/after 1/1/2009Modified/reconstructed after 6/12/2006
37Quad J - Emission Standards Phased in over several years and have Tiers with increasing levels of stringencyOutput-based, units of g/kW-hr (g/HP-hr)O2, standards for some enginesPollutants: NOx, CO, VOCSulfur limit on gasolineSome standards modeled after EPA’s standards for non-road SI engines
38Quad J - ComplianceManufacturers must certify engines ≤25 HP, gasoline engines, and rich burn LPG enginesManufacturers can elect to certify other enginesOwner/operator complies by either:For certified engines: Install, configure, operate and maintain engine per manufacturer’s instructions or manufacturer-approved proceduresFor uncertified engines: Conduct performance test (requirements vary depending on engine size)
39Quad J - Notification and Recordkeeping Owners/operators of uncertified SI RICE ≥500 HP must submit an initial notification.Owners/operators of all SI RICE must keep records of:All notificationsAll maintenance conducted on the engineFor certified engines: Documentation from the manufacturer certifying that the engine complies with the applicable emission standards of Quad JFor uncertified engines or certified engines operating in a non-certified manner: Documentation that the engine meets the emission standards.
40NESHAP for Stationary Reciprocating Internal Combustion Engines (RICE) (“Quad Z”) New or reconstructed stationary RICE located at an area source must meet the requirements of Quad I or Quad J. No further requirements apply under Quad Z.Existing (1/1/2009) institutional emergency stationary RICE located at an area source of HAP emissions do not have to meet the requirements of Quad Z or the General Provisions of 40 CFR 63.
41Permitting Guidance NH Permit Applicability NH Permit Approaches General State Permit (up for renewal April 2013)On-line permitting (http://des.nh.gov)Easy, fast, less paperworkInitial permit is freeEmission-based fees still applyIndividual Permits (Temporary, State, Title V)DeviceDesign gross heat input (BTU/hr)FuelIndividualCombinedOne or more Internal Combustion Devices (Engines)150,0001,500,000Liquid fuel oil10,000,000NG or LPG
42Questions? Contact: Cathy Beahm N.H. Department of Environmental ServicesAir Resources Division(603)