We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byDerick Franklin
Modified about 1 year ago
The eStorage project WP1 Presentation 28/10/2013 Henri Jacquet-Francillon - EDF
© 2013 eStorage2 eStorage project : WP1 Objectives and organisation Objectives : Demonstrate the feasibility and benefit of converting a large fixed speed pump- turbine into a variable speed machine: Le Cheylas PSP unit 2 (240 MW) Evaluate the likely benefits of such conversion, Monitor results from the demonstration plant and provide data for WP3 Develop solutions for conversion of a significant share of European fixed rotating speed pumped hydro storage units into variable speed units Organization : EDF : Hydro and research & development divisions. ALSTOM Grenoble (turbine), ALSTOM Birr (DFIM) 28/10/2013 eStorage ambition : « Deploy flexible PSPs across the EU and enhance grid management systems to support the integration of renewable energy »
© 2013 eStorage3 Upgrade of le Cheylas PSP Presentation of le Cheylas PSP, located in the Alps, close to Grenoble Commissioned in 1979 2 identical 240 MW reversible units A plant with two purposes : Electricity generation (Arc river inflows) Electricity storage, on a daily cycle Benefits from conversion of unit 2 to variable speed, Increased efficiency in both turbine and pump mode +/- 35 MW regulation in pumping mode 28/10/2013 3
© 2013 eStorage4 Upgrade of le Cheylas PSP Details of operation Main components to be replaced, modified or added : Runner and wicket gates (replaced) Motor / generator and its refrigeration system (replaced) Main transformer (replaced) Overhead travelling crane (modified) Additional electrical equipment (VSI) (added) Main challenges : Optimisation of hydraulic design to both gain efficiency and extend range of operation in pump mode Minimise impact on existing structures and handling equipment of increased weight of the new motor generator Minimise downtime of unit 2 for conversion 28/10/2013 4
© 2013 eStorage5 WP1 Actions (1) Results Task 1.1 : performance and service target A comparison between the operational performance of le Cheylas in 2010, 2011 & 2012 in its existing configuration and of its probable operational performance over the same years with a variable speed unit The increased turbine efficiency procures additional peak generation both from the Arc river inflows and from the volumes from the lower reservoir, and should therefore procure - under likely future values of peak energy – additional revenues that justify the expenditure incurred by improving the efficiency of the pump- turbine, Concerning the ancillary services in pump mode, under the current French grid code compensation for ancillary services, the additional revenues are unlikely to justify the corresponding expenditures. However, compensation to operators for providing ancillary services may need to be increased in the coming years to take into account the development of wind and solar projects 28/10/2013 5
© 2013 eStorage6 WP1 Actions (2) Results Task 1.2 : Unit Design and Model Test, AHF The Basic design of the motor generator has begun, including the first mechanical computations, and the main characteristics have been determined : weight, size etc.. Based upon the new runner design, the flow transient computer simulations have been performed : the overspeed and overpressure values during these transients are acceptable, The model tests of the modified pump-turbine are underway : the first results indicate that the performance targets (efficiencies and extended operating range in pump mode) should be reached, Simulations conducted by ABB (the VSI manufacturer) to verify compliance with the French grid code : harmonic studies, short circuit studies, response to a voltage drop, amperage variation during machine start-up &shutdown are well underway (ABB final report is due at the end of November). No difficulty has been identified so far. 28/10/2013 6
© 2013 eStorage7 WP1 Actions (3) Results Task 1.2 : Unit Design and Model Test, EDF, re engineering of the whole unit electrical equipment The basic design of the circuit breaker used for the DFIM, for the launching in motor mode and for the regenerative braking sequence (based upon ABB simulations) has been performed, The basic design of the GCB (Generator Circuit Breaker), using the results of the ABB simulation has also been performed, A verification that no change in design of the new main transformer for unit 2 is necessary due to the different harmonics of the new unit, DFIM rotor feeding : studies have started for the isolated phase bus ducts, The existing structures can take the load and torque applied by the stator ; the best way to apply the additional weight of the new rotor to the unit fixed parts and civil structures is being worked out, The cooling system modifications required for unit 2 are now defined, Handling of the heaviest component (the new rotor) : The existing metallic supports of the overhead travelling cranes and their foundations can take the additional weight. The extent of the modifications to the travelling cranes is still being studied. 28/10/2013 7
© 2013 eStorage8 WP1 : next year actions Get ready to start the demonstration phase Final results of Model tests are expected in early December 2013, The objective is to complete all design & tests necessary and to identify, quantify and to reduce to an acceptable level all major project risks by the end of 2013, Starting then procurement in early 2014 should be adequate for achieving unit 2 conversion to variable speed in the selected 2016 window to limit the loss of revenue induced by unit 2 shutdown. 28/10/2013 8
© 2013 eStorage9 WP1 : critical success factors PROGRESS Reach target Performances of modified pump-turbine 90% Re arrange equipment in the powerhouse 90% Compliance with grid code 80% Duration of Outage period : looks realistic but is still an important risk to control during demonstration phase Modify Overhead Travelling crane : two options appear satisfactory ; best one to be selected Take new rotor weight : one preferred option identified – feasibility being confirmed Adapt interfaces with cooling system, SCADA, Bus bar, GCB.. 80% 28/10/2013 9
© 2013 eStorage10 eStorage project Summary of deliverables 28/10/2013 10
A consortium of energy-industry leaders and academic researchers Algoé, a management consultancy. Alstom, a leading power generation and grid equipment and solutions company. DNV KEMA, the global expert in energy and sustainability consultancy. EDF, the world’s largest producer of electricity. Elia, one of Europe’s leading electricity transmission system operators. Imperial College, a provider of world- class education and research. © 2013 eStorage11 28/10/2013
EStorage First Annual Workshop Arnhem, NL 30, Oct Olivier Teller.
Review of eStorage’s ﬁrst year results WP3 Benefits of Storage and Regulatory Framework & Market Design 30 October 2013 Wim van der Veen - DNV KEMA.
ESTORAGE WP 2 Progress & Results 28/10/2013 Jean-Christophe Passelergue Olivier De l’Hermuzière.
Conclusions Innovative application of induction and synchronous generators in autonomous small hydropower plant Prof. M.T.E. Kahn NeuroMorphoGenics/NMG.
M.E.F. Mechanical Energy Factory Mechanical Power Converter & Re-Generator System.
Offshore Wind 2004 From Vindeby to Nysted A Manufacturer’s Experience Henrik Stiesdal Bonus Energy A/S.
Importance of advanced simulations of electrical system in wind turbines April 2010.
© ABB Group May 24, 2015 | Slide 1 Improving Power System Stability Through Integrated Power System Stabilizers Rudolf Wieser, Matthias Baechle, Valerijs.
Wind Turbine Session 4. Fixed-speed wind turbines In the early 1990s the standard installed wind turbines operated at fixed speed. That means that regardless.
Dynamic Transmission Response of a Hydrostatic Transmission Results measured on a Test Bench J. Schmitz, N. Diepeveen, N. Vatheuer
Three-Phase ac Voltage Generation Advantages: For single phase power is rms value of voltage multiplied by current. Whereas 3 phase provide 73% more power.
Review of progress and future work SQSS Sub Group 2 August 2006 DTI / OFGEM OFFSHORE TRANSMISSION EXPERTS GROUP.
1. Introduction 2. E-On Guidelines 3. Modelling 4. Controller Design 5. Simulation Results 6. Conclusion Voltage Regulator for Reactive Power Control on.
Daudi Mushamalirwa Luanda June, 2014 Technical issues of the stability of small size electric systems composed of wind generators and conventional generating.
Chapter 5. Synchronous Machines. Introduction Unlike induction machines, the rotating air gap field and the rotor in the synchronous machine rotate at.
RACING WITH HYBRIDS PROPOSAL TO THE ESMSC Jean Jacques His, Ferrari Head of Powertrain Department 16/11/2010.
UK Power Networks. All rights reserved Demonstrating the benefits of energy storage on an 11 kV Distribution Network Matthieu Michel – Technology.
GENERATOR PROTECTION. Generator Differential Protection (87 G) It is unit type protection, covering the stator winding for phase to phase faults due to.
International Atomic Energy Agency 1 Grid, Industrial involvement and procurement Akira OMOTO DIR, NENP.
1 | Program Name or Ancillary Texteere.energy.gov Percheron Power, LLC’s Proof of Power Project on Potholes East Canal (POP ‐ PEC) 2011 Water Power project.
EFFECTS OF VOLTAGE IMBALANCE ON 3-PHASE INDUCTION MOTORS DESIGN TEAM 3.
Recent TSO report on changes because of larger amounts of renewable enery IEA Task 25, January 14, 2016 Edf – Clamart – Paris – France Lennart Söder Professor.
Lesson 33 AC Generators. Learning Objectives Understand the operation of a single phase two pole AC generator. Describe the operation of a simple AC generator.
©2015 Energy Technologies Institute LLP - Subject to notes on page 1 ©2015 Energy Technologies Institute LLP The information in this document is the property.
Water turbines BILLY GERENA # ROBERT DE AZA # JORGE SEDA # JOSE GARCIA # PROF: EDUARDO CABRERA (ME )
Wind, wave and tidal energy DNV serving the energy industry.
Condition Monitoring Adam Adgar School of Computing and Technology.
Ludington Pumped Storage Plant and Wind Power Operational Considerations David Lapinski Consumers Energy Company June 16, 2009.
1 Institute of Mechatronics and Information Systems Control and Driving Systems.
DC Machines. A DC Machine Armature along with the commutator.
OBTAINING QUALITY MILL PERFORMANCE Dan Miller IOM 3 Meeting on Maximising Mill Performance London 4 December 2008.
Year 2006 Report “Better” Managed and Controlled Transmission Grids using Advanced Technological Concepts Aty Edris EPRI Power Delivery & Markets
1 permanent performance Design of the Z72 wind turbine with direct drive PM generator Introduction The turbine design The conversion system Testing.
1 Motors and Generators ©Dr. B. C. Paul More Fun with Flux Mechanically Rotated Shaft Slip Rings Wires with brush contacts to slip rings Electromagnetic.
1. Hydraulic accumulator 2. Hydraulic intensifier 3. Hydraulic press 4. Hydraulic crane 5. Hydraulic lift 6. Hydraulic ram 7. Hydraulic jack 8. Fluid.
VECTOR DRIVES EASA June 2005 “REACHING NEW HEIGHTS” Dave Ruehle and Bill Colton.
WISA Meeting Help Arrange a Speaker, Write Bio, Introduce February 24, 2015 March 24, 2015 May 26, 2015 Upcoming Meetings October 28, 2014 Del Tech Tour.
1 HYDRAULIC MOTORS. 2 DIFFERENT FORMS OF ENERGY HYDRAULIC SYSTEM TYPES OF ACTUATORS WHAT IS A HYDRAULIC MOTOR ? COMPARISON BETWEEN ELECTRIC & HYDRAULIC.
Overview OF MULTI Mega Watt WIND TURBINES and wind parks.
1 Electric Utility Power Systems Generation of Electricity.
EE535: Renewable Energy: Systems, Technology & Economics Energy Storage.
14-1 Copyright © 2003 by John Wiley & Sons, Inc. Chapter 14 Induction Motor Drives Chapter 14 Induction Motor Drives Extremely large potential as adjustable.
1 Study Committee Representatives Annual Report December, 2012 SC B4 “HVDC and Power Electronics” Activity Report Presented by: John McNichol (Manitoba.
DM Copyright © Tekes Digital Product Process.
1 Smart Grid Vision Electric Grid Modernization Steering Committee Grid Facing Technology Subcommittee January 14, 2013.
Clean Energy Project Analysis Training Hydro Project Analysis.
Motors and Generators. Electric Machine: Motor and Generator stator & rotor wiring types: field winding: only provide field armature: the coil carries.
Welcome to First Hydro 16 July First Hydro Slide 2 Approximately 200 employees across four sites Dinorwig –largest pumped storage plant in Western.
WORLDWIDE WIND ENERGY SOLUTIONS State-of-the-art midsize (50 to 500 kW) wind turbines reducing your energy cost. Designed for industries, farms schools,
© 2017 SlidePlayer.com Inc. All rights reserved.