Download presentation

Presentation is loading. Please wait.

Published byHaylee Garber Modified over 3 years ago

1
**Insulation Resistance Calculations of Airfield Lighting Circuits**

35th annual Hershey conference Insulation Resistance Calculations of Airfield Lighting Circuits Joseph Vigilante, PE

2
**Presentation Objective**

To develop a formula to calculate insulation resistance for an airfield lighting circuit and provide theoretical and real-life examples.

3
**Presentation Agenda Cable insulation resistance (IR) background**

FAA IR guideline recommendations Formula development Airfield lighting circuit calculations Summary Open Q&A

4
**Anatomy of insulation current flow**

Capacitance charging currents, C Absorption current, RA Conduction current, RL Circuit model DC VOLTAGE SOURCE RA C RL S

5
**Anatomy of insulation current flow**

CURRENT - MICROAMPERES 100 90 80 70 60 50 40 30 25 20 15 10 9 8 7 6 5 4 3 2.5 2 1.5 1 0.1 0.15 0.2 0.25 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1.0 SECONDS CAPACITANCE CHARGING CURRENT

6
**Anatomy of insulation current flow**

CURRENT - MICROAMPERES 100 90 80 70 60 50 40 30 25 20 15 10 9 8 7 6 5 4 3 2.5 2 1.5 1 0.1 0.15 0.2 0.25 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1.0 SECONDS CAPACITANCE CHARGING CURRENT ABSORPTION CURRENT

7
**Anatomy of insulation current flow**

CURRENT - MICROAMPERES 100 90 80 70 60 50 40 30 25 20 15 10 9 8 7 6 5 4 3 2.5 2 1.5 1 0.1 0.15 0.2 0.25 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1.0 SECONDS CAPACITANCE CHARGING CURRENT ABSORPTION CURRENT CONDUCTION CURRENT

8
**Anatomy of insulation current flow**

CURRENT - MICROAMPERES 100 90 80 70 60 50 40 30 25 20 15 10 9 8 7 6 5 4 3 2.5 2 1.5 1 0.1 0.15 0.2 0.25 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1.0 SECONDS CAPACITANCE CHARGING CURRENT TOTAL CURRENT ABSORPTION CURRENT CONDUCTION CURRENT

9
**Types of insulation resistance testing**

Short-time/spot reading TIME 60 sec MEGOHMS VALUE READ AND RECORDED TIME (MONTHS) MEGOHMS VALUES CHARTED

10
**Types of insulation resistance testing**

Time-resistance method TIME 10 Min MEGOHMS INSULATION SUSPECT INSULATION PROBABLY OK

11
**Testing airfield lighting circuits**

AC 150/ F, Design & Installation Details for Airport Visual Aids - Chapter 12, Equipment & Material, Section 13, Testing 50MΩ Non-grounded series circuits FAA-C-1391, Installation & Splicing of Underground Cable

12
**Resistance values for maintenance**

AC 150/ B, Maintenance of Airport Visual Aid Facilities Suggested minimum values 10,000 ft. or less - 50MΩ 10,000 ft. – 20,000 ft. - 40MΩ 20,000+ ft. - 30MΩ

13
**FAA-C-1391 Installation & Splicing of Underground Cables**

Spot Test Take readings no less than 1 minute after readings stabilized Cable IR values = 50MΩ, 40MΩ & 30MΩ Loop IR reduced due to parallel summation Cable IR never less than above values

14
**Insulation resistance formula**

Constant current series lighting circuit Provides for parallel summation of circuit components 3 components L-824 cable L-823 cable connectors L-830 isolation transformers RT RN RC I V

15
**FAA minimum IR values L-824 cable**

AC 150/5345-7E, Specification for L-824 Underground Electrical Cable for Airport Lighting Circuits Table 1, Test #9 > ICEA S , Section Corresponding to IR Constant 50,000 MΩ - k-ft. at 15.6°C

16
**FAA minimum IR values L-823 cable connectors**

AC 150/ D, FAA Specification for L Plug and Receptacle, Cable Connectors Section 5.1 – Type I Connectors 75,000 MΩ

17
**FAA minimum IR values L-830 isolation transformers**

AC 150/ C, Specification for Series to Series Isolation Transformers for Airport Lighting Systems Table 3 Insulation Resistance 7,500 MΩ

18
Base formula 1/IR = 1/RC + 1/RN + 1/RT RT RN RC I V IR

19
Cable equation The insulation resistance of cable for a certain length can be calculated by the following formula: Where: RC = Insulation resistance in Megohms of cable K = Specific IR in Megohms - k ft at 60˚ F of insulation D = Outer diameter of insulation d = Outer diameter of bare copper wire L = Length of airfield cable in feet Value of K for EPR insulation = 50,000 Megohms 𝑅𝐶=𝐾 ∗𝐿𝑜𝑔 𝐷 𝑑 ∗ 𝐿

20
**Cable equation D= 9.18 mm d= 4.58 mm D d CONDUCTOR JACKET INSULATION**

OD

21
**Cable equation 𝑅𝐶=𝐾 ∗𝐿𝑜𝑔 𝐷 𝑑 ∗ 1000 𝐿**

𝑅𝐶=𝐾 ∗𝐿𝑜𝑔 𝐷 𝑑 ∗ 𝐿 RC = 50,000 MΩ-k ft * Log ( 9.18/4.58) * (1,000/L) RC = 15,098,860 MΩ / L

22
Connector equation The insulation resistance of L-823 connector splices can be calculated by the following formula: RN = Rc/Nc Where: RN = Insulation resistance in Megohms of all connectors Rc = Insulation resistance of L-823 connector splice Nc = Quantity of L-823 connector splices RN = 75,000MΩ/Nc

23
**Isolation transformer equation**

The insulation resistance of L-830 isolation transformers can be calculated by the following formula: RT = Rt/Nt Where: RT = Insulation resistance in Megohms of all transformers Rt = Insulation resistance of L-830 isolation transformers Nt = Quantity of L-830 isolation transformers RT = 7,500MΩ/Nt

24
**IR Base formula 1 𝐼𝑅 = 𝐿 15,098,860 + 𝑁𝑐 75,000 + 𝑁𝑡 7,500 MΩ⁻¹**

1/IR = 1/RC + 1/RN + 1/RT 1 𝐼𝑅 = 𝐿 15,098, 𝑁𝑐 75,000 + 𝑁𝑡 7,500 MΩ⁻¹ RT RN RC I V IR

25
**Developing IR calculation formula**

L-823 Connector L-830 Isolation Transformer L-824 Series Lighting Cable Supply Return Section 1 Section 2 Section 3

26
**Developing IR calculation formula**

L-823 Connector L-830 Isolation Transformer L-824 Series Lighting Cable Section 1 Section 2 Insulation Resistance to Earth Earth Ground Section 3

27
**Developing IR calculation formula**

L-823 Connector Supply L-824 Series Lighting Cable Insulation Resistance to Earth Earth Ground 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 1 = 𝐿 15,098, 𝑁𝑐 75,000 MΩ⁻¹

28
**Developing IR calculation formula**

1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 2 = 𝐿 15,098, 𝑁𝑐 75,000 + 𝑁𝑡 7,500 MΩ⁻¹ L-823 Connector L-830 Isolation Transformer L-824 Series Lighting Cable Insulation Resistance to Earth Earth Ground

29
**Developing IR calculation formula**

1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 3 = 𝐿 15,098, 𝑁𝑐 75,000 MΩ⁻¹ Earth Ground Insulation Resistance to Earth L-823 Connector Return L-824 Series Lighting Cable

30
**Developing IR calculation formula**

1 𝐼𝑅𝑡𝑜𝑡𝑎𝑙 = 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛3 𝐼𝑅𝑡𝑜𝑡𝑎𝑙= 1 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 3 MΩ IR total IRsection 1 IRsection 2 IRsection 3

31
**Calculation example Vault SECTION 1 SECTION 2 SECTION 3 CCR Handhole**

32
**Calculation example Cable = 5,000 feet Section 1: Section 2:**

Connectors = 2 Isolation XFMRs = 0 Section 2: Cable = 20,500 feet Connectors = 224 Isolation XFMRs = 112 Section 3:

33
Calculation Example Section 1: Cable = 5,000 feet Connectors = 2 Isolation XFMRs = 0 Vault CCR Handhole Handhole 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 1 = ,098, ,000 = 𝑀Ω⁻¹

34
Calculation Example Section 2: Cable = 20,500 feet Connectors = 224 Isolation XFMRs = 112 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 2 = 20,500 15,098, , ,500 = 𝑀Ω⁻¹

35
Calculation Example Section 3: Cable = 5,000 feet Connectors = 2 Isolation XFMRs = 0 Vault CCR Handhole Handhole 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 3 = ,098, ,000 = 𝑀Ω⁻¹

36
Calculation Example 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 1 = ,098, ,000 = 𝑀Ω⁻¹ 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 2 = 20,500 15,098, , ,500 = 𝑀Ω⁻¹ 1 𝐼𝑅𝑠𝑒𝑐𝑡𝑖𝑜𝑛 3 = ,098, ,000 = 𝑀Ω⁻¹ IR total = 50 MΩ Circuit length is 30,500 ft, so the circuit IR is well over the recommended minimum value.

37
**Modifying a circuit Vault SECTION 1 SECTION 2 SECTION 3 CCR Handhole**

38
Modifying a circuit Each circuit modification warrants a reevaluation of the IR for that circuit Assume: Segment 1: Cable = 5,000 feet Connectors = 2 Isolation XFMRs = 0 Segment 2: Cable = 20,500 feet Connectors = 430 Isolation XFMRs = 215 Segment 3: Total circuit: IRsection1 = 2,795 MΩ IRsection3 = 2,795 MΩ IRsection2: RC = 50,000 * Log ( 9.18/4.58) * (1,000/L) = 15,098,860/20,500 = 755 MΩ RN = 75,000/Nc = 75,000/430 = 174 MΩ RT = 7,500/Nt = 7,500/215 = 35 MΩ IRsection2 = 1/(1/ /35 + 1/174) IRsection2 = 28 MΩ IR = 1/ ( 1/2, /28 + 1/2,795 ) IR = 27.4 MΩ

39
**Modifying a circuit Total circuit IR = 27.4 MΩ**

Circuit Length = 30,500 feet Recommended value for +20k feet circuit = 30 MΩ If you remove the transformer component, the circuit IR = 128 MΩ

40
**Case study example: Measuring IR of a TDZ Circuit**

Section 1: Cable = 1,615 feet Connectors = 5 Isolation XFMRs = 0 Section 2: Cable = 13,200 feet Connectors = 365 Isolation XFMRs = 180 Section 3: Total circuit IR = 33.2 MΩ Circuit Length = 16,430 feet 10k-ft – 20k-ft = 40 MΩ W/O Transformers; IR = 164.3 Measured value = MΩ

41
**Case study example: Measuring IR of a REL Circuit**

Section 1: Cable = 1,540 feet Connectors = 5 Isolation XFMRs = 0 Section 2: Cable = 27,777 feet Connectors = 180 Isolation XFMRs = 90 Section 3: Total circuit IR = 61.6 MΩ Circuit Length = 30,857 feet + 20k-ft = 30 MΩ Measured value = 998 MΩ

42
Summary Good engineering practice to perform circuit load and insulation resistance calculations Best practice – establish field test baseline and track results Standards provide recommended values - reductions are allowed Check & verify transformers, connectors and cable types and sizes Minimum allowable component values – higher factory test values High initial field value does not necessarily indicate a good circuit

43
Questions

Similar presentations

OK

Find the perimeter. Areas Grade 7 - CIC 15-Feb-14 Area of a Rectangle 31 2 43 3 3 6 12 X = X = X = BAh B B h h B h B = base h = height Must learn formula.

Find the perimeter. Areas Grade 7 - CIC 15-Feb-14 Area of a Rectangle 31 2 43 3 3 6 12 X = X = X = BAh B B h h B h B = base h = height Must learn formula.

© 2017 SlidePlayer.com Inc.

All rights reserved.

Ads by Google

Ppt on social media advertising Ppt on chinese food Ppt on panel discussion invitation Ppt on image compression using wavelet transform Ppt on self awareness test Ppt on birds and animals Ppt on plane table surveying Ppt on human chromosomes labels Ppt on solid dielectrics pdf Ppt on tsunami early warning system