We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byDawson Winnett
Modified about 1 year ago
© ABB Ltd - ATLV /26/2015 Insert image here Fuses vs Fuseless Technology
© ABB Ltd - ATLV The Great Debate ACB MCCB MCB Switch + Relay Fuse Fuse Switch Switch fuse
© ABB Ltd - ATLV The Great Debate Lets go back to basics……… Question: Why do we use protection devices???? Common Ans: To prevent Faults Wrong! Protection whether by fuse, circuit breaker or relay cannot prevent faults from happening. Only good design, high quality components, careful installation, preventative maintenance along with good working practices can prevent major faults However, protection devices can limit the damage and inconvenience caused if faults occur.
© ABB Ltd - ATLV The Great Debate What do we mean by a fault? Overload Operating condition in an electrically undamaged circuit which causes an current to flow in excess of the full load current Example: Starting condition during DOL start If this type of fault continues indefinitely because of an anomolous operating condition., damage begins to occur creating……….
© ABB Ltd - ATLV The Great Debate What do we mean by a fault? Short Circuit Operating condition in an electrically damaged circuit where there is an accidental or intentional connection by a relatively low resistance between two points of a circuit which are normally at different voltages This type of fault can generate high current flows, arcing and fire if not cleared quickly
© ABB Ltd - ATLV The Great Debate So back to the debate……. Which technology is best? The answer is not simply a matter of one being superior to the other Lets look at the technology more closely
© ABB Ltd - ATLV Typical fuse Current (A) Time (s) Ultra Reliable Standard Characteristic High current limitation effects High threshold on low overloads ( clears overloads at approx 1.45x rated FLC)
© ABB Ltd - ATLV Fuses & their associated switches Advantages Lower cost than comparative MCCB up to approx 400A Fuses readily interchangeable between switches of different manufacture hence low stocking costs for protective element Test Position for auxiliary contact testing Easier discrimination/selectivity due to non-adjustment of protective element Disadvantages Expensive to automate (motorise) Limited data extraction (ON/OFF, Fuse intact/Blown) Single shot protection before manual intervention Deterioration of protection with age and current stress System protection can be compromised by use of increased fuse size or by defeating fuse ( the old copper wire trick!!) Non-adjustment capability leads to potential oversizing of cables to achieve discrimination
© ABB Ltd - ATLV Fuseless technology Two main types:- Thermomagnetic protection- MCB and lower rated MCCB plus older type protection relays Electronic protection – Microprocessor based relays fed from CTs either external to switches or integral within a circuit breaker
© ABB Ltd - ATLV Thermomagnetic Thermal curve (adjustable) Time (s) Current (A) Magnetic curve (fixed) Offer thermal longtime overcurrent protection using Bi- metal technology ( operates at 1.3x FLC) Uses the magnetic effect of short circuit currents to offer shorttime short circuit protection
© ABB Ltd - ATLV Thermomagnetic MCB & MCCBs Advantages Small size at low current ratings ( MCB) Easily automated – shunt trip/ UVR/ Motor operator (MCCB) Difficult to compromise system protection Multishot protection before manual intervention ( at least 2 shots) Non-deterioration of protection element with age or current stress Better overload protection leads to optimisation of cable sizing Disadvantages Limited data extraction ON/OFF, Tripped (MCCB) Expensive replacement of protection element as switch contacts are used in arc clearance More complex discrimination Poorer current limitation than equivalent fuse
© ABB Ltd - ATLV Electronic Relays Time (s) Current (A) Overcurrent functions such as:- Long time overcurrent Short time instantaneous protection Short time time delayed protection Ground fault or Earth fault protection
© ABB Ltd - ATLV Electronic ACB & MCCBs Advantages Lower cost at 630A and above than fuse equivalent Easily automated – shunt trip/ UVR/ Motor operator Difficult to compromise system protection Multishot protection before manual intervention ( at least 2 shots) Non-deterioration of protection element with age or current stress Better overload protection leads to optimisation of cable sizing Complex functionality Wide ranging data extraction Disadvantages Expensive replacement of protection element as switch contacts are used in arc clearance More complex discrimination due to complexity of protective functions Poorer current limitation than equivalent fuse
© ABB Ltd - ATLV Relay functionality STANDARD RANGE OF PROTECTION FUNCTIONS : Overload Short Circuit ( with or without time delay) Earth fault High complexity protection functions: Minumum / Maximum / Residual voltage protection Phase imbalance Inverse power flow Directional Protection Restricted earth fault Standby earth fault Zone Discrimination
© ABB Ltd - ATLV Measurements Amps Volts Power Trip information ( Phase/ current/ date/time) Data logging Maintenance indication No. of operations Settings Harmonic content All capable of being transmitted either visually or by data stream
© ABB Ltd - ATLV Conclusions The choice of protective device needs to be considered taking the requirements of the installation and the end client into consideration Examples:- Within a remote installation, the automation capabilty to restore power remotely after a fault condition without human intervention may be critical to the needs of the end client requiring the use of circuit breakers capable of transmitting information on the level of fault current cleared When protecting particular equipment, such as inverter drives for example, the high current limiting effect of fuses may be critical to sucessful protection of the thyristor circuits.
© ABB Ltd - ATLV Conclusions These examples are extreme and generally both fuse or fuseless technology can be used sucessfully within the majority of installations. The choice is yours…. The secret is to be aware of the capability of the technology you are using and to design your installation within the limits of the protection you have chosen ABB has been manufacturing both circuit breakers and switchfuses for many years, research and development within both technologies continues to increase the capabilities of the products we supply to make sure that whatever technology you choose, there is a suitable product within the range to meet your protection requirements.
Power Systems Engineering Selective Coordination for Emergency and Legally-Required Standby Power Distribution Systems Presented for the IEEE Industry.
L.T Circuit Breakers. L.T Circuit Breaker A circuit breaker is an automatically- operated electrical switch designed to protect an electrical circuit.
Presentation : IMS – Tech Managers ConferenceAuthor : IMS StaffCreation date : 08 March 2012Classification : D3Conservation :Page : # 04 - Power and Control.
1 EC Fans. 2 Leonardo Evolution units offer the possibility to choose between two different types of Backward Curved Fans: Standard Asynchronous Fans.
Power Transfer Applications & Considerations John Stark – Russelectric Inc.
Introducing Electricity and Electrical Safety. What is electricity and what are the different kinds of electricity?
APPLIED ELECTRONICS Outcome 2 Gary Plimer 2004 MUSSELBURGH GRAMMAR SCHOOL.
Electrical Safety. OSHA – General Industry Electrical 29 CFR 1910 Subpart S.
John Stark – Russelectric Inc.. Overview Recent changes to the National Electrical Code (NEC) require the selective coordination of overcurrent protective.
OEM Control Components Control Circuit Protection Supplementary Protectors vs. Miniature Circuit Breakers UL 1077 vs. UL 489.
Presented by: H.J. Arnett Industries, LLC. D.C. Scout Purpose The D.C. Scout is used for locating resistive or non- resistive current paths from DC Battery.
Lesson Introducing Electricity and Electrical Safety.
Alternator Protection for Emergency Standby Engine Generators Kenneth L. Box P.E. Regional Sales Manager – Power Electronics Cummins Power Generation.
Dimming Methods Types of Solid State Dimming Types of Fluorescent Dimming HID Dimming By Jon Limbacher of Spectrum Lighting.
Seminar on Circuit Breaker Made By :- Dhruv Shah Made By :- Dhruv Shah (09 EE 111) (09 EE 111)
Pneumatics - Use Some examples of everyday pneumatic systems are shown below. How many do you recognise?
UNIT – V I: Telephone Instruments and Signals The Subscriber Loop, Standard Telephone Set, Basic Telephone Call Procedures, Call Progress Tones and Signals,
Copyright© Voltimum Experts – not to be reproduced without prior consent of Voltimum UK Voltimum Expert Topic – Power Harmonics.
1 OPERATIONS The term production and operations tend to be interchangeable today the main feature of operations is that there is an input, process, output.
Test Parameter Typ. Unit Typical Description Input Bias Current µA Each input of an operational amplifier has a certain amount of current that flows in.
Automatic Transfer Switch (ATS) The Key to High Reliability Source Switching.
Soft-Starters Drives A new product for OEMs, End Users, Panel Shops, Facilities Engineers, Maintenance Personnel, MRO Accounts … High Speed J (HSJ)
1 GE Consumer & Industrial Multilin Protection Basics Presented by John S. Levine, P.E. Levine Lectronics and Lectric, Inc
Basic Electronics. Basic Electronics Course Standard Parts List QuantityPart DescriptionPart NumberJamco NumberCost (2004) 1Mastech MulitmeterM830B220855CR$9.95.
REVIEW Green Professional Building Skills Training Electrical Systems.
Version 4.1 CCNA Discovery 2– Chapter 7. Contents 7.1: ISP Services : TCP / IP Protocols 7.2: 7.3: DNS 7.3: 7.4: Application Layer Protocols 7.4.
UEE31307 Certificate III in Refrigeration and Air Conditioning Stage 2A Units: UEENEEPOO2B Chris Hungerford Saturday, May 31, 2014 EKAS Fault find-
Fundamentals of Bus Bar Protection GE Multilin. 2 GE Consumer & Industrial Multilin 2-Jun-14 Outline Bus arrangements Bus components Bus protection techniques.
Gary Plimer 2005 Electrical Circuits / Electronics Electricity is one of the most important forms of energy available to man. It affects everyones lives.
Design for Overpressure and Underpressure Protection Slide ShowExitSlides with Text.
© 2016 SlidePlayer.com Inc. All rights reserved.