Download presentation

1
GAS BURNERS R 40 GS 20

2
**0’ sec 1 RMG 88.620A2 M Ph N 3 2 1 To be connected when phase-phase PA**

10 13 4 12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F Manual Switch

3
**0’ sec 1 RMG 88.620A2 M Ph N 3 2 1 PA Damper Motor Opens TB B4 S3 T2**

10 13 4 12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Damper Motor Opens Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 Once Open Contact Will Change TL PG TS F

4
**is the condition to begin the ignition**

0’ sec 2 Tension At both # 9 and # 4 is the condition to begin the ignition cycle... …waiting time (2 sec)... 6 10 13 4 12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

5
**2’ sec 3 Fan Motor is Supplied Through #7 RMG 88.620A2**

10 13 4 12 2 1 RMG A2 2 PA 9 P 17 7 Air Pressure Switch Changes to Normally Opened Position (by 10 sec) 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

6
**2…40’ sec 4 RMG 88.620A2 M This Circuit Remains Until**

10 13 4 12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black This Circuit Remains Until Prepurge is Completed (40 sec) Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

7
**40’ sec 5 …then ignition: both # 13 and # 12 are energised**

6 10 13 4 …then ignition: both # 13 and # 12 are energised 12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

8
**The Ignition Transformer**

40..43’ sec 6 6 10 13 The Ignition Transformer is energised for 5 sec Flame Signal Max 3 sec 4 12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

9
**7 RMG 88.620A2 M Ph N 3 2 1 PA TB B4 S3 T2 T1 N L1 TL PG TS F 6 10 13**

12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

10
**8 RMG 88.620A2 M Ph N 3 2 1 PA TB B4 S3 T2 T1 N L1 TL PG TS F 6 10 13**

12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

11
**9 RMG 88.620A2 M Ph N 3 2 1 PA TB B4 S3 T2 T1 N L1 TL PG TS F 6 10 13**

12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

12
**10 RMG 88.620A2 M Ph N 3 2 1 PA TB B4 S3 T2 T1 N L1 TL PG TS F 6 10 13**

12 2 1 RMG A2 2 PA 9 P 17 7 15 5 16 1 Blue M Black Capacitor TB Ph N 3 2 1 B4 S3 T2 T1 N L1 TL PG TS F

Similar presentations

OK

RL 22-32 BLU BUrners TRAining CEntre. RL 22-32 BLU BUrners TRAining CEntre CONTROL BOX LOA 24.171 B27 FEATURES: #Electrical protection IP 40 #Electrical.

RL 22-32 BLU BUrners TRAining CEntre. RL 22-32 BLU BUrners TRAining CEntre CONTROL BOX LOA 24.171 B27 FEATURES: #Electrical protection IP 40 #Electrical.

© 2018 SlidePlayer.com Inc.

All rights reserved.

To make this website work, we log user data and share it with processors. To use this website, you must agree to our Privacy Policy, including cookie policy.

Ads by Google

Ppt on telephone etiquette training Ppt on history of vedic maths Presentation ppt on leadership Ppt on 5g wireless system Ppt on agriculture and food security Ppt on ms word window with label Ppt on chapter management of natural resources Ppt on magic maths Download ppt on mutual fund Download ppt on pulse code modulation math