Download presentation

1
PID Control Loops Guy Zebrick

2
**Direct and Reverse Acting Proportional Control Integral Control **

Contents Open & Closed Loops Direct and Reverse Acting Proportional Control Integral Control Derivative Control Definitions Loop Tuning

3
**Open Loop Control / Direct Acting**

Mathematical Calculation Input Control Variable Setpoint Output Device 0-100% Input: Outside Air Temperature Setpoint: 50’F Output: Chiller on/off (0-100%) Action: Direct (input output )

4
**Open Loop Control / Reverse Acting**

Mathematical Calculation Input Control Variable Setpoint Output Device 0-100% Input: Outside Air Temperature Setpoint: 60’F Output: Boiler on/off (0-100%) Action: Reverse (input output )

5
**Closed Loop Control Reverse Acting**

Mathematical Calculation Input Control Variable Output Device 0-100% Setpoint Input: Room Temperature Setpoint: 70’F Output: Radiator Valve (0-100%)

6
**PID Control by Mathematical calculation**

Proportional Output varies in PROPORTION to input error Integral Output varies over TIME based on input error Derivative Output varies based RATE of CHANGE of input error P control P + I control P + I + D control (not used in our industry!)

7
**PID closed loop control – driving at speed**

0% P 30% PID 40% PI 60% PI 0% PID 40% PID 70% PI 25% PID 40% PI

8
**Definition: (SETPOINT)**

The desired value of the input variable T1 T2 T3 T4 T5 T6 Input Value Setpoint Time

9
**Definition: OFFSET (error)**

The DIFFERENCE between the input variable and the desired setpoint. T1 T2 T3 T4 T5 T6 Input Value Setpoint Time Offset

10
**Definition: Throttling Range (Proportional Band)**

Amount of Change in INPUT that equals a 0-100% change in OUTPUT 100% Controller Output 50% 0% 70° 65° 75° Setpoint T1 T2 T3 T4 T5 T6 Throttling Range (Proportional Band) (10’F)

11
**Proportional Control (with Offset Error)**

Control Point Setpoint T1 T2 T3 T4 T5 T6 Offset 0=100% Time

12
**Proportional + Integral Control (eliminates offset)**

Control Point Setpoint T1 T2 T3 T4 T5 T6 Offset 0=100% Time

13
**Derivative Calculation based on RATE of CHANGE**

Control Point Setpoint T1 T2 T3 T4 T5 T6 Offset D P + I + D Not used in our industry! Time

14
**Integral Windup Condition**

Setpoint T1 T2 T3 T4 T5 T6 100% Control Point Time Prevented by Disabling Loop when system is OFF

15
**PID Enhancements Setpoint Reset Setpoint Recovery Ramp**

Setpoint Demand Limit “BUMP” Setpoint Select(s) PID Output BIAS PID Output Start Point PID Output Start Ramp PID Output Adjust Delay PID Output Adjust Threshold PID AUXILLARY Output PID Output Sequencer

16
**Definition: PID Output Bias**

50% 0% 100% 100% 50% 50% 0% 0% T1 T2 T3 T4 T5 T6 T1 T2 T3 T4 T5 T6 Output = 50% at Setpoint Output = 0% at Setpoint

17
**PID Setpoint RESET Requires RESET sensor (typically outside air)**

Automatically adjusts setpoint

18
**PID Setpoint Recovery Ramp**

Degrees/Hr Requires multiple schedule information Current State (occupied/unoccupied) Next State (occupied/unoccupied) Time until next state (minutes) UNOCC Setpoint OCC OCC Time

19
**PID options (not available on ALL PID loops)**

Output Start Value (%) Provides starting value for initial control Output Start Ramp (seconds) limits action during initial startup to prevent overshoot Output Dead Band (%) Output Adjust Delay & Threshold Prevents repeated minor adjustment to output Prevents needless wear & tear on mechanical devices

20
**Definition: Hunting (over-reacting)**

100% Controller Output 50% 0% 70° Setpoint T1 T2 T3 T4 T5 T6 69° 71° Proportional Band Throttling Range (2’F) Time

21
Tuning Hints: PI control for closed-loop applications only. The narrower (smaller) the throttling range, the more precise the control operation. The wider (larger) the throttling range, the more stable the control action. Generally the throttling range required for PI control is greater than what is used for proportional control only. The integral time value is set in seconds. A slow process such as space temperature control requires a long integral time (600 seconds or more), while a fast process such as static pressure control requires a short integral time. An integral time of 0 eliminates the integral function for the control loop.

22
**Typical Values From Engineering Manual**

Default Space Temperature Control (CV AHU controller)

23
**Throttling Range = ½ Input Sensor Range **

Field Tuning Integral Time to Zero Throttling Range = ½ Input Sensor Range Adjust Throttling Range to point where about first begins to hunt. Increase Throttling Range 1.5 X Add Integral Time based on system response time (typically 60 – 2500 seconds) Check for Stable Operation

24
PID POP Quiz Define open loop Define closed loop A cooling loop is (direct/reverse) acting An AHU static pressure control loop is (direct/reverse) acting Define P, I, D Define throttling range Define integral time When do you use Differential control? What adjustment(s) reduce ‘hunting’?

25
Questions?

Similar presentations

OK

Effects on UK of Eustatic sea Level rise GIS is used to evaluate flood risk. Insurance companies use GIS models to assess likely impact and consequently.

Effects on UK of Eustatic sea Level rise GIS is used to evaluate flood risk. Insurance companies use GIS models to assess likely impact and consequently.

© 2018 SlidePlayer.com Inc.

All rights reserved.

By using this website, you agree with our use of **cookies** to functioning of the site. More info in our Privacy Policy and Google Privacy & Terms.

Ads by Google

Ppt on automobile industry in india Ppt on moral education by horace Ppt on means of transport for class 2 Ppt on field study example Ppt on hard gelatin capsule ingredients Ppt on art of war pdf Ppt on values attitudes and job satisfaction Ppt on natural resources of india Tough times never last but tough people do ppt online Ppt on waves tides and ocean currents for kids