4 WT4Most recent proposal  & . Not very different from  and only a few changes compared to current WECC model.Used Data graciously provided under NDA from Vestas and Siemens Wind Power, respectively.Acknowledgements:Babak Badrzadeh, VestasNikolaus Moeller Goldenbaum, Siemens
14 ABB CASES SHOWN PREVIOUSLY  STILL VALID WITH THIS MODEL Data provide by ABB under NDA to EPRI
15 CONCLUSIONWe believe that this model now caters to multiple vendor equipment, and has been shown to give good validation resultsSome minor conventions have to be discussed and finalizedThe “spike” issue need software resolution – several ideas are being pursued
16 REFERENCES P. Pourbeik, “Using Field Data for Model Validation of a Vestas Type 4 Wind Turbine Generator”, Memorandum to IEC TC88 WG27, WECC REMTF and EPRI P173, 11/3/11. P. Pourbeik, “Example Case of Using Field Data for Model Calibration of a Type 4 Wind Turbine Generator”, Memorandum to IEC TC88 WG27, WECC REMTF and EPRI P173, 10/24/11. S. Seman, “WT 4 (full converter RMS model) – IEC ; for Working Draft 4.6 – updated version”, 5/4/11. P. Pourbeik, “The WT4 Model”, presentation made at IEC meeting November 2010 and February 2011 (also presented at WECC REMTF in March 2011).
17 ASIDE – SOLAR PV MODELING (simulation ONLY – not validated) -