We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byDominic Fletcher
Modified over 3 years ago
Summary of Second Draft of the NERC Standard PRC-002-2 Disturbance Monitoring and Reporting JSIS Meeting August 10, 2010 Salt Lake City, UT
© Copyright 2009, Southern California Edison 2 Purpose: To ensure that Facility owners collect the data needed to facilitate analyses of Disturbances on the Bulk Electric System (BES) To establish requirements for recording and reporting sequence of events (SOE) data, fault recording (FR) data, and dynamic disturbance recording (DDR) data to facilitate analyses of disturbances. This standard will replace PRC- 002-1 and PRC-018-1 standards.
© Copyright 2009, Southern California Edison 3 Planning Coordinators Transmission Owners with BES substation buses. Generator Owners with equipment connected to BES substation buses and either of the following: 1.Generating units having single units of 20 MVA or higher. 2.Generating plants with an aggregate total capacity of 75 MVA or higher. Applicability
© Copyright 2009, Southern California Edison 4 Requirements Each Planning Coordinator shall establish a list of SOE and FR monitored locations by applying the following criteria to their Planning Coordinator area every five years: 25% of the bus locations with the highest calculated short circuit MVA levels for bus locations within their fault study greater or equal to 100 kV and have three-phase short circuit level of 1500 MVA or higher calculated under normal conditions.
© Copyright 2009, Southern California Edison 5 Each Transmission Owner shall record the SOE data for changes in circuit breaker position (open/close) for each of the circuit breakers it owns, at 200 kV and higher voltages in facilities designated to have SOE. Each Generator Owner shall record the SOE data for changes in circuit breaker position (open/close) for each of the circuit breakers it owns functioning as the primary generator output circuit breaker on the high or low side of a GSU for the individual generators of 20 MVA or higher or for an aggregate rating of 75 MVA or higher, in facilities designated to have SOE. Each Generator Owner shall record the SOE data for changes in circuit breaker position (open/close) for each of the circuit breakers it owns at 200 kV and higher voltages in facilities designated to have SOE. Requirements (Contd)
© Copyright 2009, Southern California Edison 6 Requirements (Contd) Each Transmission Owner shall record FR data [each bus, transmission line, and transformer] at locations it owns which are identified to have FR. Each Generator Owner shall record FR data for the individual generators with a rating of 100 MVA or higher or for an aggregate rating of 300 MVA or higher, with a common point of interconnection connected to facilities designated to have FR.
© Copyright 2009, Southern California Edison 7 Requirements (Contd) Each Transmission Owner and Generator Owner shall have FR that meets the following: –A minimum recording rate of 16 samples per cycle. –A pre trigger record length of at least 2 cycles and a post trigger record length of at least 50 cycles for the same trigger point; or at least two cycles of pre trigger data, the first 3 cycles of the fault, and the final cycle of the fault.
© Copyright 2009, Southern California Edison 8 Requirements (Contd) Each Planning Coordinator shall establish a list of DDR monitored locations by applying the following criteria to their Planning Coordinator area every five years: –10% of the bus locations with the highest calculated short circuit MVA levels for bus locations within their fault study greater or equal to 100 kV and have three- phase short circuit level of 1500 MVA or higher calculated under normal conditions. –Generators with an individual rating of 500 MVA or higher or for an aggregate rating of 1500 MVA and higher.
© Copyright 2009, Southern California Edison 9 Requirements (Contd) Each Planning Coordinator shall ensure that the list of DDR monitored locations will monitor the following: –Planned islands formed as a result of generation-load imbalances of 5000 MW and higher. –Any SPS actuation that result in loss of load of 500 MW and higher. –Elements associated with Interconnection Reliability Operating Limits (IROL). –Both ends of a HVDC terminal. –Dynamically controlled devices such as synch condensers, static VAR compensators and all FACTS devices greater than or equal to 100 MVA and voltages above 200 kV. –Each end of transmission lines 300 kV and above between Planning Coordinator areas.
© Copyright 2009, Southern California Edison 10 Requirements (Contd) Each Transmission Owner and Generator Owner, for those DDR devices installed to meet Planning Coordinator requirements, shall ensure its DDR data conforms to the following specifications: –Input sampling rate of at least 960 samples per second. –Store calculated electrical quantities at a rate of at least 30 times per second; or store sampled input quantities for calculations by other devices. Each Transmission Owner and Generator Owner that implements DDR functionality shall provide continuous recording and storage of DDR data.
© Copyright 2009, Southern California Edison 11 Requirements (Contd) Each Transmission Owner and Generator Owner that has DDR functionality and does not have continuous recording capability because the devices were installed prior to the effective date of the continuous recording requirement, shall set data record lengths at a minimum of 3 minutes. Each Transmission Owner and Generator Owner shall have all recorded SOE, FR, and DDR data available (locally or remotely) for 10 calendar days after a disturbance.
© Copyright 2009, Southern California Edison 12 Requirements (Contd) All SOE, FR, and DDR data shall be provided to the Regional Entity, Reliability Coordinator or NERC within 30 calendar days of a request. ALL FR and DDR data shall be in a format such that any software system capable of viewing and analyzing COMTRADE files may be used to process and evaluate the data. Each Transmission Owner and Generator Owner shall each retain all data provided to the Regional Entity, Reliability Coordinator or NERC for at least 3 years following the event.
© Copyright 2009, Southern California Edison 13 Thank You!
Questions about AVR & PSS
PMUs for NERC Reliability Standards Ryan D. Quint, Ph.D., P.E. Staff Coordinator, NERC SMS, SAMS WECC JSIS Meeting September 22, 2015.
1. 11/26/2012: NERC Board of Trustees adopted CIP v5 CIP thru CIP CIP and CIP Version 5 Filing FERC requested filing by 3/31/2013.
PRC Process Overview Presented by SPP Staff SPCWG/TWG/RCWG Meeting Month of June 2016 Doug Bowman – –
Jay Loock SR Compliance Auditor Operations & Planning Audit Approach MOD-026 & MOD-027 CUG Meeting June 3 – 5 Salt Lake City, UT.
Doug Tucker Associate Staff Engineer TRD/TADS update and Future reporting.
NERC Footnote b / 12 – Load Loss
FRCC Seasonal Transmission Assessment & Operational Seasonal Study Winter 2012.
1. 2 NERC Bulk Electric System (BES) Definition (NERC Glossary of Terms Used in Reliability Standards) FERC Order 693 FRCC Handbook Review Task Force.
Reliability Subcommittee Report Vishal C. Patel Chair – Reliability Subcommittee March 2014.
Reliability Standards – Disturbance Monitoring Webinar PRC Disturbance Monitoring and Reporting Requirements.
ERCOT SOL Methodology for the Planning and Operations Horizons Stephen Solis 2014 OTS 1.
December 7, 2012 ERCOT Planning Horizon SOL Methodology Update Jeff Billo RPG.
NERC Project S ystem Protection Coordination - PRC-027 Presentation to the NSRS Conference Call April 20, 2015 Sam Francis Oncor Electric Delivery.
Voltage Control Brad Calhoun Consultant, Sr. Trainer Spring 2016.
Marv Landauer Report to TSS on Annual Study Program Report Review Task Force April 2012 TSS Meeting Salt Lake City.
System Operator Conference NERC Standards Review for: Simulator Drill Orientation 2014 System Operator Conferences Charlotte NC & Franklin TN SERC/SOS.
2015 RTP – Study Scope of Short Circuit Analysis RPG Meeting May 19,
TransWest Express and Gateway South WECC Planning Coordination Committee David Smith, National Grid October 25-26, 2007 Vancouver, B.C.
System Strength Discussion Shun-Hsien (Fred) Huang Electric Reliability Council of Texas July 16, 2014 System Strength Workshop, Austin, Texas 1.
Bulk Electric System Definition Task Force Update Reliability Policy Issues Committee March 4, 2010 Brian Theaker BESDTF Chair.
April 7, 2015 Washington, D.C. Area Low-Voltage Event Operations Training Seminar 2016 Erik Johnson System Operations Training (ERCOT)
Project Definition of Bulk Electric System & Bulk Electric System Rules of Procedure Development Presenter: Peter Heidrich, FRCC – BES Drafting.
NERC Standards Update Colleen Frosch ROS Meeting January 7, 2016.
Standards Subject to Enforcement Currently Or Standards Subject to Future Enforcement TSS Meeting #169 May 6-8, 2015 By: Lesley Kayser-Sprouse.
NAESB Coordinate Interchange Version 1 Standard Revision 1, Draft 5 August, 2005.
2004 NERC, NPCC & New England Compliance Programs John Norden Manager, Operations Training, Documentation & Compliance August 31, 2003 RC Meeting.
WECC Board of Directors April 21-23, 2004 Seattle, Washington WECC Procedure for Reporting of System Events Disturbance Reports Rod Maslowski OC Vice Chairperson.
WECC TRD/NERC TADS Webinar
Applying the Distribution System in Grid Restoration/NERC CIP-014 Risk Assessment Srijib Mukherjee, Ph.D., P.E. UC Synergetic.
New Energy Horizons Opportunities and Challenges Fault Current Contributions from Wind Plants Dean Miller PacifiCorp July 25,
1 New Resource Qualification Testing Sandip Sharma Supervisor, Operations Analysis New Generation Information Forum ERCOT Public November 4, 2014.
Determine Facility Ratings, SOLs and Transfer Capabilities Paul Johnson Chair of the Determine Facility Ratings Standard Drafting Team An Overview of the.
1 MSRATF Update to TSS (Modeling SPS and RAS Ad Hoc Task Force) Scope of Work Approval January 25, 2013 Joe Seabrook Puget Sound Energy.
1 Wyoming Infrastructure Authority November 10, 2009 Superconductor Electricity Pipelines.
NERC Project S ystem Protection Coordination - PRC-027 Presentation to the NSRS Conference Call August 17, 2015 Sam Francis Oncor Electric Delivery.
Lecture 21 Symmetrical Components, Unbalanced Fault Analysis Professor Tom Overbye Department of Electrical and Computer Engineering ECE 476 POWER SYSTEM.
Reliability Standard TPL Transmission System Planned Performance for Geomagnetic Disturbance Events Presented to PGDTF February 11, 2015 TPL
WECC Response to BAL-002-WECC-1 Remand Order December 10, 2010 WECC Board of Directors Meeting Steve Rueckert Director of Standards.
Project System Protection Coordination Requirement revisions to PRC (ii) Texas Reliability Entity NERC Standards Reliability Subcommittee.
1 NPCC – A-2 Dr. Mayer Sasson Transmission Planning Consolidated Edison of New York June 1, 2006 Presented to the NYSRC-RRS.
Jerry Rust Chair - Underfrequency Load Shedding Criterion Team WECC Regional Criterion PRC-006-WECC-CRT-1 (Project WECC-0065) Underfrequency Load Shedding.
Material for 10/23/2015 PGDTF Meeting Michael Juricek.
CIP Version 4 The Basics. CIP Version 4- Background Centers around expanded criteria for Critical Assets – FERC thought Risk Based Methodologies used.
Demand Resource Operable Capacity Analysis – Assumptions for FCA 5.
RiversidePublicUtilities.com Arts & Innovation RiversidePublicUtilities.com MOD GENERATOR TESTING REQUIREMENTS RESOURCE PLANNERS LeeAnne Uhler, Regulatory.
2006 Reliability Study Scope Name Date. DRAFT 2 Purpose of Study Assess the PEC and Duke transmission systems’ reliability Develop a single reliability.
THE POWER OF POSSIBILITY AESO current limits for Alberta-BC transfers Jeff Palermo – KEMA/AESO.
Parallel Flow Visualization Data Requirements Parallel Flow Visualization Data Requirements NERC ORS Meeting Toronto, Ontario September 23-24, 2009 Jim.
NERC BAL-005, BAL-006, FAC-001 Gary Nolan WECC ISAS April 20, 2016.
© 2017 SlidePlayer.com Inc. All rights reserved.