We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byLauren McKnight
Modified over 3 years ago
25 Years Gas-Insulated Medium-Voltage Switchgear from Siemens Medium-Voltage Switchgear - Then and Now - Hans-Joachim Müller
Power Transmission and Distribution © Siemens AG 2006 Page 2 June 07 Medium Voltage Division Evolution of Medium-Voltage Switchgear non type tested Air-insulated type tested Gas-insulated Air/solid-insulated Cast-resin insulated Source: ABB Local installation Workshop manufacture Factory- assembled, type-tested Factory- assembled, compact Factory- assembled, SF 6 -insulated Yearuntil 1950 until 1970since 1970since 1980since 1982 Building83 m 3 47 m 3 29 m 3 24 m 3 8 m 3 Panel19 m m m m m 3
Power Transmission and Distribution © Siemens AG 2006 Page 3 June 07 Medium Voltage Division Situation in the Past Yesterday, switchgear were air, oil or cast-resin insulated with the following features: Huge dimensions Dependent on pollution and climate Maintenance at regular intervals Human failure during maintenance High fire risk Not arc-fault tested This means: High investment for buildings High costs for maintenance staff and system transfer in the network Breakdown of the network (longer downtimes)
Power Transmission and Distribution © Siemens AG 2006 Page 4 June 07 Medium Voltage Division Restricted Availability and Reliability of Supply After short circuit at the rear side of an epoxy-resin insulated switchgear Burned-out 10 kV substation: Fire after short circuit in an epoxy-resin insulated ring-main unit
Power Transmission and Distribution © Siemens AG 2006 Page 5 June 07 Medium Voltage Division Requirements for development: Personal safety Reliability of supply Maintenance-free design Suitability for all switching duties Sufficient power reserves Low fire risk Small, light design Concept options for new switchgear due to availability of the following equipment: Maintenance-free switching devices Shockproof cable plugs and bar connections Electronic measuring and protection devices Objectives for the Development of New Switchgear
Power Transmission and Distribution © Siemens AG 2006 Page 6 June 07 Medium Voltage Division Constructional implementation: Solid insulation is replaced by insulating gas with constant properties Sealed enclosure of primary part Installation of fixed-mounted, maintenance-free switching devices: - Vacuum circuit-breaker - Three-position switch - SF 6 -switch-disconnector Shockproof cable plugs Use of current and voltage transformers with low susceptibility to faults Verification of safe isolation from supply with capacitive voltage dividers Maintenance-free and reliable operating elements with few parts inside the enclosure Easiest operation Pressure-resistant enclosure with defined pressure relief Implementation of the Development Tasks
Power Transmission and Distribution © Siemens AG 2006 Page 7 June 07 Medium Voltage Division Situation with Gas-Insulated Switchgear Todays state of the art is gas-insulated switchgear with the following main benefits: Small, compact dimensions Independent of environmental effects and climate Widely maintenance-free Maximum safety for staff Low fire risk Arc-fault tested Advantages: Low invest for buildings due to compact dimensions and climate-independent design Maximized power supply reliability Maximum personal safety Lowest life cycle costs Reduced operational costs - no additional maintenance costs
Power Transmission and Distribution © Siemens AG 2006 Page 8 June 07 Medium Voltage Division First SIEMENS Gas-Insulated Medium-Voltage Switchgear (April 1982) Kulmbach / Germany 8DA10 16 panels 24 kV / 16 kA (3s) / 1250 A
Power Transmission and Distribution © Siemens AG 2006 Page 9 June 07 Medium Voltage Division Applications Today Tibet / China 8DA panels 40.5 kV / 31.5 kA (3s) / 1250 A Site altitude: 3000 – 5000 m
Power Transmission and Distribution © Siemens AG 2006 Page 10 June 07 Medium Voltage Division First SIEMENS Gas-Insulated Medium-Voltage Ring-Main Unit (April 1982) Stadtwerke Lambrecht / Pfalz, Germany Project:Municipal power supply Electrical data:24 kV, 16 kA, 630 A Typicals:8DJ10, scheme 10
Power Transmission and Distribution © Siemens AG 2006 Page 11 June 07 Medium Voltage Division Switchgear Type 8DJ Typical Application Examples
25 Years Gas-Insulated Medium-Voltage Switchgear from Siemens Thank you very much for your attention!
25 Years Gas-Insulated Medium-Voltage Switchgear from Siemens Resistance to Internal Faults Martin Schaak Olaf Bischur Thomas Stommel.
IEM Industrial Electrical Mfg. (Canada) Inc. IEM Canada is a subsidiary of IEM US who is North Americas largest independent full-line manufacturer of electrical.
Prepared by Kazi Md. Shahiduzzaman Lecturer,EEE Detail Discussion on Different type of Circuit Breaker.
Electric power transmission was originally developed with direct current. The availability of transformers and the development and improvement of induction.
Introduction to Switchgear Prepared by Kazi Md. Shahiduzzaman Lecturer, EEE.
1 PERFORM WHEN THE HEATS ON NOMEX ® is a Registered Trademark of E.I. DuPont de Nemours & Co. Frequent Questions & Answers for DuPont TM ReliatraN ® Global.
© Siemens AG Alle Rechte vorbehalten. Industrial Control and Distribution SIRIUS Portfolio 2009.
Power Transfer Applications & Considerations John Stark – Russelectric Inc.
John Stark – Russelectric Inc.. Overview Recent changes to the National Electrical Code (NEC) require the selective coordination of overcurrent protective.
Power Systems Engineering Selective Coordination for Emergency and Legally-Required Standby Power Distribution Systems Presented for the IEEE Industry.
1 Confidential and Proprietary to Littelfuse, Inc. © 2005 Littelfuse, Inc. All rights reserved. Telecom WIA Training Training Agenda 1.Fuse Definition.
1 GE Consumer & Industrial Multilin Protection Basics Presented by John S. Levine, P.E. Levine Lectronics and Lectric, Inc
Underground Cables Presented By: Er. H.S. Dhaliwal Assistant Professor, Deptt. Of Electrical Engg BHSBIET, Lehragaga. 1Punjab EDUSAT Socity.
1 GE Consumer & Industrial Multilin Protection Fundamentals By Craig Wester, John Levine.
CIRCUIT BREAKERS. CONTENTS Introduction History Basic Element Of circuit breaker Type Of Circuit Breakers Advantages Conclusion References.
Funded by FCH JU (Grant agreement No ) 1 © HyFacts Project 2012/13 CONFIDENTIAL – NOT FOR PUBLIC USE 1.
SCCR Codes and Standards Including: Basic Principles NEC ® 409 and UL 508A How to Determine the SCCR of an Industrial Enclosure.
An Introduction to On-line Partial Discharge Surveys.
AC Interference Columbia Gas of Ohio/Kentucky Tim Jenkins Corrosion Front Line Leader.
Automation and Drives Safety at Work AS-i SIGNUM Extension Plug Low Voltage Switchgear Burns Master Configuration K60 ATEX Analogue modules Analyser.
Global Developments in Electrical Safety Electrical Safety week, ICF, Perambur, 13th June 2003 P.G. Sreejith Cholamandalam AXA Risk Services Ltd.
Innovated Solutions by Cooper Crouse Hinds Technology & Innovation.
Nr. MTS May 2006 Innovations 2006 HMI innovations.
© Siemens AG All Rights Reserved. Industry SectorPage 1 How do you achieve sustainable business?
Fundamentals of Bus Bar Protection GE Multilin. 2 GE Consumer & Industrial Multilin 2-Jun-14 Outline Bus arrangements Bus components Bus protection techniques.
ATIB Drilling Presentation ATIB Drilling company was established for Uzbekistan Oil and Gas industry. KTB is one of ATIBs division which provides.
UEE31307 Certificate III in Refrigeration and Air Conditioning Stage 2A Units: UEENEEPOO2B Chris Hungerford Saturday, May 31, 2014 EKAS Fault find-
1 PRESENTATION INSTRUMENT HOOK-UP (PROCESS & ANALYZER) Prepared By : M. Asim Ashraf Date:
1 Current Date Standards Document Path..ppt SWITCHGEAR BIG GRAY BOXES SWITCHBOARD.
© 2017 SlidePlayer.com Inc. All rights reserved.