Presentation on theme: "ENERGY EFFICIENCY FOR END-USERS. CSU Chancellors office coordinates the efforts to accomplish the goals established by Assembly Bill 32 for green house."— Presentation transcript:
CSU Chancellors office coordinates the efforts to accomplish the goals established by Assembly Bill 32 for green house gas reduction. California's major initiatives for reducing greenhouse gas are outlined in AB 32, one of the goals is to reduce GHG emissions to 1990 levels by 2020. GREENHOUSE GAS EMISSIONS
Executive order 987 The CSU shall develop a strategic plan for energy procurement and production to reduce energy capacity requirements from the electricity grid, and to promote energy independence using available economically feasible technology. CSUSM COMPLIANCE WITH 987
Performance standards for new buildings of at least 20% better than Title 24 New buildings designed to meet LEED standards Participating in SDG&E Savings by Design program NEW BUILDINGS
1.4 million gallon Thermal Energy Storage tank (TES). Siemens Building Automation System Schedule for equipment start and stop times Schedule exterior and interior lighting High efficiency air filters Cog style belts for large air handlers Continuous commissioning and monitoring of the existing buildings. CENTRAL UTILITY PLANT
Interior and exterior lighting retrofit projects Exterior/High pressure sodium to T-5 florescent Interior/Motion sensors, 32 Watt 5000K lamps and new diffusers Central Utility Plant upgrades and energy efficiency projects Boiler and chiller replacement Variable primary pumping New cooling tower ENERGY SERVICE COMPANY PROJECT (ESCO)
Sub metering all buildings for electrical demand Flow meters for chilled and hot water in each building Comprehensive Building Management System SiteSMART to pull all the data together and make it presentable. DemandSMART provides incentive payment opportunity as well as meeting the load shed requirement. TOOLS
Monitoring-Based Commissioning (MBCx) Identifies a prioritized list of savings opportunities based on continuous analysis of the buildings operations. SITESMART
SiteSMART: Data Driven Energy Efficiency Thousands of data points from throughout the facility are collected and analyzed by EnerNOC and delivered in detailed energy dashboards and scorecards with savings recommendations Data is captured at the meter and behind the meter, then EnerNOC’s software continuously looks for equipment-level savings opportunities.
EnerNOC won the contract with the CSU through an RFQ process. CSU Chancellors office provided funding to do MBCx in three of the CSUSM campus buildings. CSUSM’S ENROLLMENT IN SITESMART
CRAVEN HALL BUILDING 154,967 square‐foot building, estimated savings of 10% electricity and 15% for Heating Hot Water (in therms) using MBCx
UNIVERSITY HALL BUILDING 71,300 square‐foot building, estimated savings of 10% electricity, and 15% for heating hot water(in therms) using MBCx program.
KELLOGG LIBRARY BUILDING 200,530 square‐foot building, estimated savings of 11% electricity, 11% for Chilled Water, and 23% for heating hot water (in therms) using MBCx program.
Campus used existing sub meters and installed a BACnet compatible server. EnerNOC installed the gateway to download the data. MONITORING EQUIPMENT INSTALLATION
EnerNOC conducted a comprehensive audit at each building. Baseline data starts being trended AUDITS & MONITORING
EnerNOC issued the initial ScoreCard, with specific recommended measures. The campus implemented the measures which were low cost – no cost maintenance items. The measures that were implemented were submitted to the utility company for incentives. – Some of the measures that were identified included: Loose belts, broken dampers, stuck hot water valves, and other maintenance items. Optimization of the VAV boxes and other controllers. MEASURE & INSTALLATION
M&V reports were generated for the implemented measures. The campus reviews the ScoreCard to see the impact of the implementations. – The scorecards showed us the savings we provide the University by scheduling HVAC and interior lighting to be off during unoccupied times. – The scorecards have identified several operational areas to help optimize plant operations. MEASUREMENT &VERIFICATION
ENERGY SAVINGS Building Electricity (kWh) Chilled Water (ton- hours) Heating Hot Water (million BTUs) Total Energy Savings ($) University Hall 25,000 (4%) 147,000 (53%) 1,126 (44%) $ 25,816 (22%) Craven Hall 217,000 (14%) 55,000 (12%) 1,146 (40%) $ 40,432 (17%) Kellogg Library 478,000 (21%) 383,000 (63%) -899 (-138%)* $ 80,776 (25%) *Kellogg Library lighting retrofit increased heating loads during program
The M & V reports created by SiteSMART were used to verify the savings we accomplished during our energy conservation project. MBCx process will help us obtain LEED points for our new construction projects. OTHER BENEFITS OF M & V FOR THE CAMPUS
The amount of data being transferred for a large campus requires a Building Management System that is BACnet compatible to operate efficiently. Calibrate and verify all flow and kWh meters before recording the baseline data. Communicate any other energy conservation projects to the MBCx team (this will effect incentive payment) LESSONS LEARNED
FLOYD DUDLEY ASSISTANT DIRECTOR OF ENERGY AND ENGINEERING SERVICES FLDUDLEY@CSUSM.EDU