We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byGordon Goodwin
Modified about 1 year ago
Effects of Daylight Harvesting on Electronic Lighting Control C opyright © 2004 Joshua Scot Lester - Calvin College Engineering 315 Control Systems
© 2004, Joshua S. Lester2 Triac Dimming Zero-crossing A dimmer controls the power to the load through a solid state switch or triac. The triac is synchronized to the AC line through signals obtained at zero crossings Triac-firing The zero crossing signals are then used to fire the triac to give the correct dimmed waveform
© 2004, Joshua S. Lester3 Daylight Harvesting System  Closed-Loop Lighting Control System Diagram
© 2004, Joshua S. Lester4 Photosensor vs. Photocell photocell the light sensitive component inside the photosensor. Photosensor an entire product including the housing, optics, electronics, and the photocell.
© 2004, Joshua S. Lester5 Spectral and Spatial Response  Closed-loop lighting control block diagram
© 2004, Joshua S. Lester6 Input characterization Spatial response The input to a photosensor is optical radiation infrared (IR) ultraviolet (UV) radiation For lighting control it is measuring the distribution of luminaire intensity  Photosensor Spatial Response Spectrum
© 2004, Joshua S. Lester7 Input characterization Spectral response sensitivity to optical radiation of different wavelengths  Spectral Response Chart  Optical Radiation Chart
© 2004, Joshua S. Lester8 Open-loop Proportional Control Open-loop control has one adjustable parameter the constant of proportion between the control voltage and the optical signal  Savings in the Spotlight  Open-loop control
© 2004, Joshua S. Lester9 Closed-loop Proportional Control 2 ADJUSTABLE PARAMETERS: 1. SLOPE ( open-loop response curve ) 2. OFFSET ( commissioning ) Closed-loop control algorithm a.k.a "sliding set point control"  Savings in the Spotlight Closed-loop control
© 2004, Joshua S. Lester10 Control Algorithm Closed-loop proportional control The ceiling illuminance is 100 lux with no daylight present (from the 5:1 work-plane: ceiling ratio) Desired work-plane illuminance 500 lux Daylight enters the room and adds 250 lux Rate of dimming was set to -0.25% per lux 0.25% per lux X 250 lux = 62.5% This sets the luminaire light output to: 100 lux - (62.5% X 100 lux) = 37.5 lux. The total ceiling illuminance is now 37.5 lux + 250 lux = 287.5 lux.  CL Example
© 2004, Joshua S. Lester11 Sample of Daylight Harvest Control  Simulation of lighting levels in modeled room.
© 2004, Joshua S. Lester12 Personal controls http://www.vantagecontrols.com/
© 2004, Joshua S. Lester13 Big Picture
© 2004, Joshua S. Lester14 References I.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/controlMostImportantGraphic.jpghttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/controlMostImportantGraphic.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USA II.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/polar.asphttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/polar.asp Rensselaer Polytechnic Institute, Troy, NY 12180 USA III.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/spectralgraph.jpghttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/spectralgraph.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USA IV.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/small5.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USAhttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/small5.jpg V.Savings in the Spotlight By John L. Fetters, published June ’02 VI.http://eetd.lbl.gov/btp/pub/designguide/section8.pdf VII.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/openLoopProp.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USAhttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/openLoopProp.jpg VIII.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/closedLoopProp.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USAhttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/closedLoopProp.jpg IX.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/closedLoopExample.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USAhttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/closedLoopExample.jpg X.http://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/photosensors%20fig.jpg Rensselaer Polytechnic Institute, Troy, NY 12180 USAhttp://www.lrc.rpi.edu/programs/nlpip/tutorials/photosensors/img/photosensors%20fig.jpg
Smart lighting control Done by : Haya Salah Esraa Nabulsi Eman Dwikat Under the supervision of: Dr. Kamil Subhi.
1. Model common control system components. Course Objectives INTRODUCTION TO CONTROL SYSTEMS 2. Select an appropriate control algorithm of PID type or.
Energy Saving Climate Control System (ESCCS) Team: Sean Jacobs, Brad Nissenbaum, Colin Tracy Advisor: Professor Anderson.
Control Systems Engineering, Fourth Edition by Norman S. Nise Copyright © 2004 by John Wiley & Sons. All rights reserved. Figure1.5 Elevator input and.
Why BoldPlay? Brilliant Design. Intuitive Engineering Innovation + Design = Performance Serious Energy Savings Ideal direct/indirect distribution maximum.
Lighting System A lighting system consists of : 1.Light sources 2.Luminaires (or fixtures) 3.Ballasts.
Chapter 10: Frequency Response Techniques 1 ©2000, John Wiley & Sons, Inc. Nise/Control Systems Engineering, 3/e Chapter 10 Frequency Response Techniques.
Week 8 AC-to-AC Converters 1. Single-phase AC Voltage Controller 2.
AC-AC Converter. AC-to-AC converters have a wide range use in the industry. Applications such as light dimmers, AC motor controllers, heat controllers,
Training manual Lighting concepts – Ballasts and Lighting Controls Ballasts and Lighting Controls Training manual Chapter 3.
Modeling of Power Converters using Matlab and Simulink Reference : Fundamentals of Power Electronics second edition By R. Erickson and D. Maksimovic 1.
Electronic Troubleshooting Chapter 13 Power Control Devices.
Student Name USN NO Guide Name H.O.D Name Name Of The College & Dept.
CHE 185 – PROCESS CONTROL AND DYNAMICS PID CONTROLLER FUNDAMENTALS.
Infrared IR Sensor Circuit Diagram and Working Principle.
Getting started with MATLAB/Simulink. Starting and running simulations in MATLAB/Simulink. Constructing Simulink models. Examples: Open-loop synchronous.
Sliding Mode Control for Half-Wave Zero Current Switching Quasi-Resonant Buck Converter M. Ahmed,Student member IEEE, M. Kuisma, P. Silventoinen Lappeenranta.
TI Information – Selective Disclosure Prescalar – Postscalar Open-loop and Closed-loop Settings.
Integrator Op Amp Amplifier M.S.P.V.L. Polytechnic College, Department of ECE & EEE, Pavoorchatram.
Cruise Control 3 RETURN OF THE SPEED CONTROL JEFF FERGUSON, TOM LEICK.
Artificial Lighting Design Task lighting for general purpose rooms involves the installation of light sources that will provide the optimum amount of.
SOLAR CELL TESTING Basic Structure of a Solar Cell.
Networks in Engineering A network consists of a set of interconnected components that deliver a predictable output to a given set of inputs. Function InputOutput.
Kathmandu Engineering College DIFFERENTIAL AMPLIFIER ELECTRONIC CIRCUITS-I Course Instructor (Elex. SECTION A) Ajay Kumar Kadel ASSISTANT LECTURER (KEC,
BASIC SOLAR CELL TESTING Basic Structure of a Solar Cell.
Examining how much light is absorbed by a compound’s sample at various wavelengths Spectrum peaks— Indicates the wavelengths associated with electrons’
Chapter 11 1 Closed-Loop Responses of Simple Control Systems In this section we consider the dynamic behavior of several elementary control problems for.
Electronic Instrumentation Experiment 8: Diodes * Introduction to Diodes * Part A: Diode i-v Characteristic Curves * Part B: Diode Circuits: Rectifiers.
Electrical and Computer Engineering iLights Nick Wittemen, EE Chris Merola, EE José Figueroa, EE Matt Ryder, EE Midway Design Review.
Block Diagram. Computer Simulation Color Mixing.
Expand the setup to 4x4 s-MIMO Incorporate FPGAs at the transmitter and receiver to demonstrate high speed wireless VLC link Install the setup in VLC +
Electromagnetic Spectrum. -is the range of all possible frequencies of electromagnetic radiation. The "electromagnetic spectrum" of an object is the characteristic.
LIGHTING MANAGEMENT | PRODUCTS & SYSTEMS PUTTING A STOP TO ENERGY WASTE LIGHTING MANAGEMENT SYSTEM PUTTING A STOP TO ENERGY WASTE.
OPTOELECTRONICS. Photoresistors up close and personal CdS.
Chapter 5 AC-to-AC Converters 1 “Introduction to Modern Power Electronics”, 2 nd Ed., John Wiley 2010 by Andrzej M. Trzynadlowski.
Planck’s constant in the light of an incandescent lamp.
Solar Patio Umbrella Final Presentation May 3 rd, 2016 Team #37 ECE 445 – Spring 2016.
1 An introduction to Ultraviolet/Visible Absorption Spectroscopy Lecture 24.
System A collection of parts that perform a function.
Hybrid Wind & Solar Generation Project FINAL PRESENTATION.
VSF as a proxy for Particle Size Distribution Pauline Stephen.
Unit 3 REACTIVE POWER AND VOLTAGE CONTROL. BASIC REQUIREMENTS OF EXCITATION CNTRL Excitation Current up to 10’000 amps Input frequency range from.
CLS 332 CLINICAL INSTRUMENTAL ANALYSIS. A VISIBLE ABSORPTION SPECTROMETER.
Chapter 33 Thyristors and Optical Devices. 2 Introduction to Thyristors Thyristors –Switch –On-state, off-state –Unilateral or bilateral –Latching –High.
What disperses radiation into component wavelengths? Prisms Uses refractive index of material to bend different wavelengths of light different amounts.
Closed-loop Control of DC Drives with Controlled Rectifier By Mr.M.Kaliamoorthy Department of Electrical & Electronics Engineering PSNA College of Engineering.
HossamTalaat - MATLAB Course - KSU - 19/09/ IEEE Student Branch - College of Engineering - KSU Getting started with Power System Blockset By Prof.
Lighting calculations. The Illuminance: (E) شدة الإضاءة =Luminous Flux / area of the sphere surface E= Φ /A E= I/ r 2 = lumen/ m 2 = lux.
2009 vf Measuring Kinetics of Luminescence with TDS 744 oscilloscope Nex E0E0 Eex Luminescence Photon.
© 2017 SlidePlayer.com Inc. All rights reserved.