Download presentation

Presentation is loading. Please wait.

Published byMiranda Stafford Modified about 1 year ago

1
Assumption University Thailand EE4503 Electrical Systems Design Load Calculation 1

2
Assumption University Thailand Topics Load Calculation (E.I.T.) Load Calculation by Adding Branch Circuit Load Calculation for condominium Load Estimation 2

3
Assumption University Thailand Load Calculation (E.I.T.) lighting 3 BuildingLighting (VA)Demand Factor (%) Residential Area 2,000 > 2, Hospital 50,000 > 50, Hotel, Condominium 20,000 20,001 – 100,000 > 100, Warehouse 12,500 > 12, Other100

4
Assumption University Thailand Load Calculation (E.I.T.) receptacles 4 Total Load from Receptacle Demand Factor (%) Non residential area 10kVA 100 > 10kVA50 Residential area

5
Assumption University Thailand Load Calculation (E.I.T.) Demand Factor of Appliances 5 BuildingLighting (VA)Demand Factor (%) Residential Area Kitchen Hot Water Air Condition 10A+30% of extra first two + 25% of other 100 Office, StoreKitchen Hot Water First maximum device + 80% of the second max. + 60% of the rest 100% of the largest + 25% of the rest Hotel, OtherKitchen Hot Water Air Condition Same as Office 75

6
Assumption University Thailand Load Calculation by Adding Branch Circuit Add of all branch circuit Then multiply by the demand factor 6 Number of PanelsDemand Factor (%) >

7
Assumption University Thailand Load Calculation for Condominium Load: common area + individual room 7 TypeNumber of RoomsCoincident Factor (%) Residential > Non residential1-10 >

8
Assumption University Thailand Load Estimation Quick estimate of the load Many common tables, just refer to one 8

9
Assumption University Thailand Load Estimation 9

10
Assumption University Thailand Load Estimation 10

11
Assumption University Thailand Load Estimation (E.I.T.) lighting 11 TypeVA/m 2 School25 Computer Center, Meeting Room, Kitchen20 Walk way, Balcony8 Cafeteria18 Hospital – Operation Room100 Hospital – Patient Room14 Office, Shopping Store30 Drawing Room60 Laboratory50

12
Assumption University Thailand Load Estimation (E.I.T.) receptacles 12 TypeVA/m 2 Auditorium, Cafeteria, Church, Sport Complex 2 Drawing Room7 Hospital10 Machine Room15 Office10 School7

13
Assumption University Thailand Load Estimation (E.I.T.) air condition 13 TypeVA/m 2 Bank80 Department Store50 Hospital70 Office70 Grocery Store90 Cafeteria90

14
Assumption University Thailand Electrical Systems Design: ประสิทธิ์ พิทยพัฒน์ Reference 14

Similar presentations

© 2016 SlidePlayer.com Inc.

All rights reserved.

Ads by Google