4 Load Calculation (E.I.T.) receptacles Total Load from ReceptacleDemand Factor (%)Non residential area 10kVA100> 10kVA50Residential area𝐿 𝑚𝑎𝑥 +0.4 𝐿 𝑟
5 Load Calculation (E.I.T.) Demand Factor of Appliances BuildingLighting (VA)Demand Factor (%)Residential AreaKitchenHot WaterAir Condition10A+30% of extrafirst two + 25% of other100Office, StoreFirst maximum device + 80% of the second max. + 60% of the rest100% of the largest + 25% of the restHotel, OtherSame as Office75
6 Load Calculation by Adding Branch Circuit Add of all branch circuitThen multiply by the demand factorNumber of PanelsDemand Factor (%)12-34-67-10> 1010090807060
7 Load Calculation for Condominium Load: common area + individual roomTypeNumber of RoomsCoincident Factor (%)Residential1-1011-2021-3031-40> 419080706050Non residential> 1110085
8 Load Estimation Quick estimate of the load Many common tables, just refer to one
Your consent to our cookies if you continue to use this website.