Download presentation

Presentation is loading. Please wait.

Published byReginald Hamilton Modified over 2 years ago

1
TEAM II Cooling Tower Analysis By: Cortez Rankin & D. Caruthers

2
Objectives Components of Cooling Tower Air Outlet Velocities and Flow Rates Air Inlet Velocities and Flow Rates Water Inlet and Outlet Data Comparison of Data @ Different Water Inlet Flow Rates

3
Water Cooling Tower

4
Balances Assuming Steady State Operation [IN = OUT] Overall Mass Balance M AO + M WO = M AI + M WI Overall Energy Balance h AO M AO + h WO M WO = h AI M AI + h WI M WI AO=Air Outlet AI=Air Inlet WO=Water OutletWI=Water Inlet

5
Portable Cooling Tower

6
Air Inlet

7
Air Outlet and Water Inlet

8
Psychrometric Chart

9
Air Inlet Data for Water Inlet Flow Rate = 5.1 (l/min) Velocity = 12.2 m/s Wet Bulb Temp. = 18 °C Dry Bulb Temp. = 25.5 °C Area = 0.038 m 2 Relative Humidity = 48% Volumetric Flow Rate= 0.464 m 3 /s

10
Air Inlet Data for Water Inlet Flow Rate = 10.1 (l/min) Velocity = 12.0 m/s Wet Bulb Temp. = 17 °C Dry Bulb Temp. = 25 °C Area = 0.038 m 2 Relative Humidity = 45% Volumetric Flow Rate= 0.456 m 3 /s

11
Air Inlet Data for Water Inlet Flow Rate = 40.3 (l/min) Velocity = 8.0 m/s Wet Bulb Temp. = 19 °C Dry Bulb Temp. = 27.5 °C Area = 0.038 m 2 Relative Humidity = 45% Volumetric Flow Rate= 0.304 m 3 /s

12
Outlet Velocity as a Function of Radius for Water Inlet Flow Rate = 5.1 (l/min)

13
Outlet Velocity as a Function of Radius for Water Inlet Flow Rate = 10.1 (l/min)

14
Outlet Velocity as a Function of Radius for Water Inlet Flow Rate = 40.3 (l/min)

15
Calculate Outlet Air Velocity

16
Formulas Volumetric Flow Rate = (Area)(Velocity) Mass Flow Rate = (Density)(Volumetric Flow Rate)

17
Outlet Air for Water Inlet Flow Rate = 5.1 (l/min ) Area = 0.312 m 2 Volumetric Flow Rate= 1.7 m 3 /s Temp. Dry Bulb= 21 °C= Wet Bulb Temp. Enthalpy = 79 kJ/kg Dry Air

18
Outlet Air for Water Inlet Flow Rate = 10.1 (l/min ) Area = 0.312 m 2 Volumetric Flow Rate= 1.6 m 3 /s Temp. Dry Bulb= 23 °C= Wet Bulb Temp. Enthalpy = 86 kJ/kg Dry Air

19
Outlet Air for Water Inlet Flow Rate = 40.3 (l/min ) Area = 0.312 m 2 Volumetric Flow Rate= 1.0 m 3 /s Temp. Dry Bulb= 31°C= Wet Bulb Temp. Enthalpy = 123 kJ/kg Dry Air

20
Water Data for Water Inlet Flow Rate = 5.1 (l/min ) Inlet Temp.= 52.5 o C Outlet Temp.= 27.7 o C Temp. Change= 24.8 o C Mass Flow Rate= 0.085 kg/s Tons of Cooling= 2.5

21
Water Data for Water Inlet Flow Rate = 10.1 (l/min ) Inlet Temp.= 56.3 o C Outlet Temp.= 31 o C Temp. Change= 25.3 o C Mass Flow Rate= 0.168 kg/s Tons of Cooling= 5.1

22
Water Data for Water Inlet Flow Rate = 40.3 (l/min ) Inlet Temp.= 52 o C Outlet Temp.= 30.4 o C Temp. Change= 21.6 o C Mass Flow Rate= 0.671 kg/s Tons of Cooling= 17

23
Admin Tower Schematic

24
Admin Cooling Tower Front (West) Inlet Dry Bulb Temp = 18 o C Wet Bulb Temp = 12 o C Area = 4.6 m 2 Air Speed = 1.4 m/s Volumetric Flow rate = 6.1 m 3 /s Density of Area = 1.2 kg/m 3 Mass flow rate = 7.3 kg/s

25
Admin Cooling Tower Front (West) Inlet Team 3 Dry Bulb Temp = 33 o C Wet Bulb Temp = 24.5 o C Area = 4.6 m 2 Air Speed = 1.6 m/s Volumetric flow rate = 7.6 m 3 /s Density of Area = 1.1 kg/m 3 Mass flow rate = 8.3 kg/s

Similar presentations

OK

Heat Transfer Equations For “thin walled” tubes, A i = A o.

Heat Transfer Equations For “thin walled” tubes, A i = A o.

© 2017 SlidePlayer.com Inc.

All rights reserved.

Ads by Google

Ppt on social networking free download Ppt on history of space exploration Ppt on charge coupled device for side Ppt on political parties and electoral process united Ppt on our changing earth for class 7 Ppt on cartesian product database Ppt on conservation of momentum formula Ppt on power generation by speed breaker sign Ppt on area of parallelogram and triangles in geometry Ppt on credit policy in an organisation