We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byLeah Greive
Modified about 1 year ago
©2011, The McGraw-Hill Companies, Inc. Chapter 4
©2011, The McGraw-Hill Companies, Inc. PRIMARY AND PILOT CONTROL DEVICES
©2011, The McGraw-Hill Companies, Inc. All components used in motor control circuits may be classed as either primary control devices or pilot control devices. A primary control device, such as a motor contactor, starter, or controller, connects the load to the line.
©2011, The McGraw-Hill Companies, Inc. A pilot control device, such as a relay or sensor contact which activates a power circuit, directs the operation of another device.
©2011, The McGraw-Hill Companies, Inc. TOGGLE SWITCHES
©2011, The McGraw-Hill Companies, Inc. A manually operated switch is one that is controlled by hand. The toggle switch is an example of a manually operated switch.
©2011, The McGraw-Hill Companies, Inc. Electrical ratings for all switches are expressed in terms of the maximum interrupting voltage and current they can safely handle. The AC current rating will be higher than its DC rating for an equivalent amount of voltage. One reason for this is that AC has current zeros twice a cycle reduces the likelihood of an electric arc forming across the contacts. AC DC
©2011, The McGraw-Hill Companies, Inc. PUSHBUTTON SWITCHES
©2011, The McGraw-Hill Companies, Inc. Pushbutton switches are commonly used in motor control applications to start and stop motors, as well as to control and override process functions.
©2011, The McGraw-Hill Companies, Inc. A pushbutton operates by pressing a button that opens or closes contacts. The N.O. pushbutton makes a circuit when it is pressed and returns to its open position when the button is released. The N.C. pushbutton opens the circuit when it is pressed and returns to the closed position when the button is released.
©2011, The McGraw-Hill Companies, Inc. With a break-make pushbutton the top section contacts are N.C. the bottom section contacts are N.O. When the button is pressed, the bottom contacts are closed after the top contacts open.
©2011, The McGraw-Hill Companies, Inc. Simulated Break-Make Pushbutton Operation
©2011, The McGraw-Hill Companies, Inc. Most motor control devices are mounted in enclosures designed to protect their contents from operating environmental conditions. The types of enclosures are standardized by the National Electrical Manufacturers Association (NEMA). When you have one or more pushbuttons in a common enclosure, it is referred to as a pushbutton station. NEMA Type 1 Enclosure
©2011, The McGraw-Hill Companies, Inc. NEMA Type 7 NEMA Type 9
©2011, The McGraw-Hill Companies, Inc. Pushbuttons assemblies basically consist of an operator legend plate and contact block.
©2011, The McGraw-Hill Companies, Inc. The operator is the part of the pushbutton assembly that is pressed, pulled, or rotated to activate the pushbutton's contacts. Operators are come in many different colors, shapes, and sizes designed for specific control applications.
©2011, The McGraw-Hill Companies, Inc. Legend plates are the labels that are installed around a push button and identify its purpose. They come in many sizes, colors, and languages. Examples of label text include START, STOP, FWD, REV, JOG, UP, DOWN, ON, OFF, RESET, and RUN.
©2011, The McGraw-Hill Companies, Inc. The contact block is the part of the pushbutton assembly that is activated when the button is pressed. The contact block may house many sets of contacts that open and close when you operate the pushbutton.
©2011, The McGraw-Hill Companies, Inc. The standard contact configuration allows for one normally open and one normally closed set of contacts within a contact block. N.C. Contact N.O. Contact Operator A pushbutton may contain stacked contacts that change state with a single push of a single button.
©2011, The McGraw-Hill Companies, Inc. The contacts of the contact block itself are spring loaded and return to their normal "ON" or "OFF" state when the operator is released. However, when contact blocks are attached to a pushbutton operator their switching action is determined in part by that of the operator. Momentary type pushbutton operators return to their normal "ON" or "OFF" state as soon as the operator is released.
©2011, The McGraw-Hill Companies, Inc. Maintained type pushbutton operators require you to press and release the operator to switch the contacts to their "ON" state and to press and release the operator a second time to return the contacts to their "OFF" state. Maintained Contact Double Circuit Pushbutton Symbol Maintained type Emergency Stop switch
©2011, The McGraw-Hill Companies, Inc. Typical Emergency Stop Circuit In order to restart the motor after the emergency stop pushbutton has been activated you must first reset the emergency stop pushbutton and then press the start button.
©2011, The McGraw-Hill Companies, Inc. Simulated Emergency Stop Operation
©2011, The McGraw-Hill Companies, Inc. PILOT LIGHTS
©2011, The McGraw-Hill Companies, Inc. Pilot lights provide visual indication of the status for many motor controlled processes permitting personal at remote locations to observe the current state of the operation.
©2011, The McGraw-Hill Companies, Inc. Circuit for a start/stop pushbutton station with a pilot light connected to indicate when the starter is energized.
©2011, The McGraw-Hill Companies, Inc. Simulated RUN Pilot Light Operation
©2011, The McGraw-Hill Companies, Inc. If it is necessary for a pilot light to show when the starter is de-energized, a normally closed auxiliary contact may be attached to the starter. N.C. Auxiliary Contact Operated By Coil "M" Magnetic Starter
©2011, The McGraw-Hill Companies, Inc. Simulated OFF and RUN Pilot Lights Operation
©2011, The McGraw-Hill Companies, Inc. Pilot lights are available in both full voltage and low voltage types. Connecting a step-down transformer to a standard pilot light reduces the operating voltage supplied to the lamp. LED Also available are illuminated units utilizing integrated LED's (Light Emitting Diodes), which operate at 6 to 24-volt, AC or DC. 48 V to 600 v 24 V
©2011, The McGraw-Hill Companies, Inc. Dual input push-to-test pilot lights are designed to reduce the time required to troubleshoot a suspected faulty lamp. Press To Test Lamp Push-to-test pilot light pilot light circuit.
©2011, The McGraw-Hill Companies, Inc. Simulated Push-to-Test Pilot Light Circuit
©2011, The McGraw-Hill Companies, Inc. SELECTOR SWITCH
©2011, The McGraw-Hill Companies, Inc. Selector switches are manually operated switches in which the operator handle is rotated (instead of pushed) to actuate the attached contact block. Three-position selector switch pump circuit
©2011, The McGraw-Hill Companies, Inc. Simulated Selector Switch Operation
©2011, The McGraw-Hill Companies, Inc. Keyed selector switches require a special key for their operation. This allows only authorized personal actuate the switch and can serve as additional safety lockout for motors. Although keyed switches may be used in addition to standard lock out tag out procedures, under no circumstance should they be used in place of them.
©2011, The McGraw-Hill Companies, Inc. DRUM SWITCH
©2011, The McGraw-Hill Companies, Inc. Movable Contacts Stationary Contacts Insulated Shaft A drum switch consists of a set of moving contacts mounted on and insulated from a rotating shaft.
©2011, The McGraw-Hill Companies, Inc. Drum switches are used for starting and reversing 3ф squirrel-cage motors, 1ф motors that are designed for reversing service, and DC shunt and compound wound motors. 3ф MTR T1 T3 T2 Reversing the direction of rotation of 3ф squirrel-cage motors is accomplished by interchanging any two of the three main power lines to the motor (T1-T2-T3).
©2011, The McGraw-Hill Companies, Inc. Three-phase motor reversing drum switch connections
1 Industrial Machine Control EKT 451 CHAPTER 7. 2 Basics of Industrial Motor Control When applied to machinery, it involves the starting, acceleration,
Chapter 2 Symbols and Schematic Diagrams. Objectives Discuss symbols used in the drawing of schematic diagrams Determine the difference among switches.
Chapter 6 Control_relays. Relays and their Types Electromagnetic Contactors Motor Starters.
L 1 C N Stop Start Coil Auxiliary Contact Ladder Diagram for 120 V Motor Control Circuit Motor Control Circuit Push Button Station and Relay.
Electro-Pneumatics Module 1 Introduction to Electro-pneumatics.
HYDRAULICS & PNEUMATICS Presented by: Dr. Abootorabi Introduction to Electro-pneumatics 1.
Section 4: Electric Motors Unit 19: Motor Controls.
Industrial Controls. Industrial control devices range from simple knife switches to more complex solid state sensors. The type of control device selected.
Chapter 4 Electrical Symbols and Diagrams Language of Control Pictorial Drawings Electrical Symbols and Abbreviations Wiring Diagrams Schematic Diagrams.
Chapter 5 Control Logic Basic Rules of Line Diagrams Simplifying Printreading Line Diagrams — Signals, Decisions, and Action Logic Functions Common Control.
Components, Symbols, and Circuitry of Air-Conditioning Wiring Diagrams Electricity for Refrigeration, Heating and Air Conditioning 7th Edition Chapter.
Lesson 15: Dc Motor Control Components and Diagrams ET 332a Dc Motors, Generators and Energy Conversion Devices 1Lesson a.pptx.
SBO/ PMM/ EJ501/ Jun20111 EJ501 PROGRAMMABLE LOGIC CONTROLLER (PLC) AND AUTOMATION.
Chapter 3 Manual Starters. Objectives Discuss the operation of manual motor starters Discuss low voltage release Connect a manual motor starter Check.
Logic Control. What is Logic control Logic control is a control based on a logic concept, that is the on-off state of variable and/or equipment Logic.
ACTIVE LEARNING ASSIGNMENT TOPIC NAME :- DC MOTOR STARTERS ELEMENTS OF ELECTRICAL DESIGN ( ) AY Course co-ordinator:- SAMIR B PATEL PREPARED.
EGD ELECTRICAL ELECTRICAL SYMBOLS. Distribution board.
Contactor, Relays and Overloads Electricity for Refrigeration, Heating and Air Conditioning 7th Edition Chapter 11 Contactors, Relays and Overloads.
SECTION 4 ELECTRIC MOTORS UNIT 19 MOTOR CONTROLS.
Introduction To Programmable Logic Controllers. The concept: a machine that can be started from two remote places.
A process in which one event follows another until a job is completed Event 1Event 2Event N For a process with N steps …….. Characteristics 1.) Discrete.
PowerPoint ® Presentation Chapter 7 PLC and System Interfacing Systems Primary Systems System Interfacing Electrical Circuits Basic Electrical Circuits.
Siemens Building Technologies Building Technologies Variable Frequency Drives Bypass Options.
OR Operation A coil is not energized until either normally open switch A or B is closed. Boolean Logic Diagram Logic Functions.
GO ORDNANCE !!! ORDNANCECORPS 1 Troubleshoot the DC Electrical Control System on the EPP III.
Fluid Power Control. FLUID POWER INTRODUCTION TO PNEUMATICS ELECTRO – PNEUMATIC SYSTEM a) Use of electrical devices for controlling fluid circuits; b)
Chapter 11 Control Technology and Automation. Objectives Open loop and closed loop feedback in control circuitry. Applications of control logic.
Controls, Switches and Energy Transformation. CONTROL The function performed by a component that can open or close a circuit switches and pushbuttons.
Seminar on Circuit Breaker Made By :- Dhruv Shah Made By :- Dhruv Shah (09 EE 111) (09 EE 111)
Programming Logic Controllers Input/Output Devices & Motor Controls - Chapter 4.
Electrical Electricity Fuses Relays Solenoids Electrical Testing Wiring Harnesses Testing Voltage Drop Testing Test Procedures Cables/Connections Glow.
Components & Symbols Used in Electrical Circuits.
Three-Phase AC machines Three-phase Cage Rotor Starters and Control Gear Resource 3.
GO ORDNANCE !!! ORDNANCECORPS 1 Antenna Mast Group We will now trace the electrical circuits of the antenna mast mast group. Be fore we get started you.
E2 Motors and Motor Starting #3 Contactors and Motor Starters.
PROGRAMMABLE LOGIC CONTROLLER DNT 353/3 BY: Salsabila Ahmad.
Electronic component identification In order to identify electronic components from diagrams and data sheets and then select the appropriate electronic.
SECTION 3 BASIC ELECTRICITY AND MAGNETISM UNIT 15: TROUBLESHOOTING BASIC CONTROLS.
Salient characteristics / Approvals Non-illuminated Switches Illuminated Switches Pilot Lights Contact Elements Control & Signalling Devices.
1 Chapter 10 Advanced Programming, PLC Interfacing, and Troubleshooting.
Motors & Motor Starters Prepared By: Erik Redd & Jeremy Roberts.
ACADs (08-006) Covered Keywords Switchgear, motor control, ground, circuit breaker. Description Supporting Material
MECH 1500 Chapter 4. MECH 1500 The Binary Concept 4.1.
Troubleshooting Electric Control Devices Electricity for Refrigeration, Heating and Air Conditioning 7th Edition Chapter 14 Troubleshooting Electric Control.
MENG 447 Electrical Control Components. Switches Mechanical Electrical Optical Electromagnet DC Motor Integrated Device.
© 2017 SlidePlayer.com Inc. All rights reserved.