We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byCali Dorey
Modified about 1 year ago
© P. Kundur Wind Turbine Generators
© P. Kundur WTG - 1 Wind Turbine Generators Outline Wind Turbine Characteristics Types of Wind Turbine Generator Technologies Protection Systems Reactive Power Compensation and Voltage Control Requirements Impact on Power System Dynamic Performance Mitigation of Stability Problems
© P. Kundur WTG - 2 Wind Turbine Generators (WTGs) Wind turbine components: wind turbine runs at low speed (0.5 Hz) mechanical drive train includes a gear box converts low speed of turbine to high speed of generator Mechanical speed regulation: blade pitch angle control each blade rotated about longitudinal axis variable speed stall control no pitch actuators required fixed speed Types of generators induction generator synchronous generator doubly fed induction generator WTG ratings range from 25 kW to 3 MW
© P. Kundur WTG - 3 Typical WTG “Power Curve” Fig below shows typical output versus wind speed characteristics of wind turbines: The cut-in, rated and cut-out speeds shown are typical for utility-scale WTGs Generally, WTGs are designed to work at maximum aerodynamic efficiency between cut- in and rated wind speed For wind speeds higher than rated and lower than cut-out: blade pitching or blade stalling is used to maintain loading within the equipment’s rating WTGs shut down for wind speeds higher than cut-out speed to avoid excessive mechanical stress wind speed (m/s) Percentage Rated Output cut-in rated cut-out
© P. Kundur WTG - 4 Types of Wind Turbine Generator Technologies Presently four major types of WTG Technologies used: 1. Squirrel Cage Induction Generators driven by fixed-speed, stall-regulated wind turbines 2. Induction Generators with variable external rotor resistance driven by a variable-speed, pitch regulated wind turbines 3. Doubly-Fed Induction Generators driven by variable-speed, pitch regulated wind turbines 4. Synchronous or Induction Generators with full converter interface (back-to-back frequency converter), driven by variable-speed, pitch regulated wind turbines
© P. Kundur WTG - 5 Doubly Fed Induction Generator (DFIG) Wound rotor induction generator with slip rings Rotor is fed from a three-phase variable frequency source, thus allowing variable speed operation reduction of mechanical stress; higher overall efficiency, reduced acoustical noise The variable frequency supply to rotor is attained through the use of two voltage- source converters linked via a capacitor Note: A more appropriate designation for this type of generator is: Doubly Fed Asynchronous Generator
© P. Kundur WTG - 6 Doubly Fed Induction Generator Used in Large Wind Farms C bc Reactor Grid DC Link Chopper Grid side converter Rotor side converter DFIG
© P. Kundur WTG - 7 Control of Rotor-Side Converter The converters handle ac quantities: rotor-side converter carries slip frequency current stator-side converter carries grid frequency current Hence, they are controlled using vector- control techniques: based on the concept of a rotating reference frame and projecting currents on such a reference such projections referred to as d- and q-axis components With a suitable choice of reference frame, AC quantities appear as DC quantities in the steady state cont’d
© P. Kundur WTG - 8 Control of Rotor-Side Converter cont'd In flux-based rotating frames: changes in the d-axis component of current will lead to reactive power changes changes in the q-axis component will vary active power This allows independent control of active and reactive power of the stator Implemented through rotor-side converter control An important aspect of the DFIG concept ! Since rotor flux tracks the stator flux, air gap torque provides no damping of shaft oscillations additional modulating signal has to be added
© P. Kundur WTG - 9 Protection System Rotor current protection: Limits current in the rotor side converter If current rises above set value, a crowbar is activated short-circuits the rotor winding at the slip rings with a static switch the generator operates as a squirrel cage induction motor Typically, the case when the voltage at the terminals of the generator decreases rapidly, for example during a fault in the grid In order to avoid overspeeding of turbine, the speed reference for the pitch control is reduced simultaneously increases pitch angle and reduces mechanical power
© P. Kundur WTG - 10 Protection System cont'd Rotor speed protection: disconnects WTG from the grid if speed of rotor is higher or lower than set levels for a predefined time Over/under voltage protection: disconnects WTG from the grid if voltage is above or below set values for a predefined time
© P. Kundur WTG - 11 Performance of DFIG DFIGs have the ability to hold electrical torque constant rapid fluctuations in mechanical power can be temporarily stored as kinetic energy improves power quality! Performance for large disturbances requires thorough analysis may lead to separation of the unit process may not be readily apparent from simplified dynamic simulations
© P. Kundur WTG - 12 Performance of DFIG cont'd Large disturbances lead to large initial fault currents, both at the stator and rotor will flow through rotor-side converter; voltage source converters are less tolerant of high currents further, additional energy goes into charging the dc bus capacitor and dc bus voltage rises rapidly crowbar may be activated may lead to tripping of the unit Need for a careful assessment and proper design of controls to improve capability to ride through faults
© P. Kundur WTG - 13 Examples of Fault Ride-Through Capability Temporary reduction of active power: Active Power is ramped down for a predefined time and then ramped up again to prefault value This stabilizes wind turbine during the fault and reduces the current in the rotor converter Disadvantage: rotor can speed up causing overspeed protection to trip turbine handled by the pitch controller Temporary reduction of active power with reactive power boosting: Increases terminal voltage Improves system stability
© P. Kundur WTG - 14 Wind Power Plants Utility-scale wind power plants consist of several tens to hundreds of WTGs Each unit with a pad-mounted transformer Connected to transmission network through a medium-voltage collector network A power transformer used to interface with the transmission grid Depending on the application and type of WTG, shunt reactive power compensation may be added at one or more of the following locations: WTG terminals Collector system Substation interfacing with the Transmission grid
© P. Kundur WTG - 15 Impact of the Variability of Wind Power Plant Output Wind power plant output varies with wind resource Cannot be dispatched like conventional power plants System operators cannot control the rate of power decreases, i.e., ramp down due to falling wind speeds For ramping up, some manufacturers provide the option of controlling rate of power increase As wind power capacity within a control area increases, the variability of wind power can have a significant impact on: the efficiency of unit commitment process, and the reserve requirements to meet reliability performance standards As an example, a study of a system with 35,000 MW peak demand estimated that the regulation reserves would increase by 36 MW when adding 3,300 MW of wind power
© P. Kundur WTG - 16 Reactive Power Compensation and Voltage Control Requirements In areas with large amounts of wind generation, wind variability can have a significant impact on voltage profiles may require switched capacitor banks and shunt reactors, and transformer tap changer control Some wind power plants have the ability to control/regulate voltage at or near the point of interconnection to transmission grid accomplished by installing separate devices such as SVCs and STATCOMS, alternatively, external controller may be added for adjusting the power factor of each individual WTG until target voltage is achieved
© P. Kundur WTG - 17 Impact of Wind Power Plants on Power System Dynamic Performance The dynamics of individual WTGs and the entire wind farms could have a significant impact on the stability of the bulk power system “Rotor angle stability” is not an issue with wind power plants because most WTGs are asynchronous units No equivalent concept of “rotor angle” or synchronizing and damping torques for such generators Some studies have revealed that bulk power system “transient rotor-angle stability” is improved if wind power plants, as compared to conventional power plants with synchronous generators, are added at the same location with WTGs, a smooth and non-oscillatory power delivery is re-established following a disturbance cont’d
© P. Kundur WTG - 18 Impact on System Dynamic Performance cont’d Wind power plants could have a significant impact on “voltage stability” following a network fault Induction generators absorb higher reactive power when voltage is low Even DFIGs may “crow-bar” during a fault, and act as an induction generator Increased reactive power consumption can lead to voltage instability if the transmission grid is weak Voltage stability related to characteristics of WTGs, as opposed to load characteristics A short-term phenomenon Adequate and fast control of reactive power and voltage required Overall solution requires coordinated control of wind farms, including use of external compensators such as SVCs and STATCOMS cont’d
© P. Kundur WTG - 19 Impact on System Dynamic Performance cont’d DFIGs and generators with full converter interface do not contribute to system inertia May contribute to “frequency instability”, particularly in smaller power systems with high penetration of wind generation Special controls needed to solve this problem Present WTG designs do not contribute to primary frequency regulation Some demonstration projects in Europe have illustrated the possibility of frequency regulation using WTGs Requires more work and study before practical implementation Detailed simulation studies using appropriate wind plant models essential for satisfactory integration of large wind farms into power grids
© P. Kundur WTG - 20 Impact on System Dynamic Performance cont’d A good source of reference addressing some of these issues is the CIGRE Technical Brochure on: “ Modeling and Dynamic Behavior of Wind Generation As It Relates to Power System Control and Dynamic Performance” - Prepared by WG C of CIGRE Study Committee C4, January 2007
© P. Kundur WTG - 21 Modelling of Wind Farms Wind field model describing wind speed Wind turbine model Model for internal grid of wind farm For system studies aggregated representation is sufficient a single WTG model to represent the farm or a sub- group of WTGs Induction generator represented by a third order model d and q axis rotor circuits and acceleration of rotor Models for controls and protections Some of the modeling details/data considered: - proprietary information by manufacturers Need to move towards the development of: - “standard models” for planning and operating studies
© P. Kundur WTG - 22 Grid Codes In the past, wind power plants were allowed to trip off for nearby transmission faults and system disturbances Due to the increase in wind power capacity, this is no longer appropriate Transmission operators and reliability coordinators have begun to capture performance requirements for wind power plants in Grid Codes The Grid Codes address, among other issues, Fault tolerance and reactive power/voltage control requirements In some cases, they also address Ramp rate control and frequency response capability
© P. Kundur WTG - 23 Use of Multi-Terminal VSC-Based HVDC for Collector Network An effective way to integrate large percentage of wind generation Permits interconnection with main transmission network at relatively weak parts of the network Provides good dynamic response and ability to comply with grid code requirements in the event of AC system faults Results in smaller “footprint” Growing interest in the application for interconnection of off-shore wind farms with the transmission network
WECC Model Validation Working Group Denver, Colorado May 18-19, 2009 Wind Power Plant Dynamic Modeling and Validation Eduard Muljadi
1 EC Fans. 2 Leonardo Evolution units offer the possibility to choose between two different types of Backward Curved Fans: Standard Asynchronous Fans.
TRAINING FOR OLADE`S MEMBER COUNTRIES COURSE CAPEV By César Angeles-Camacho Instituto de Ingenieria, UNAM DESIGN AND IMPLEMENTATION.
1. Induction Machines 1.1 Introduction Induction machines are rotating electromechanical energy converting devices. Their operating principle is similar.
PowerPoint slides t/a Electrical Principles for the Electrical Trades (Machines) Vol 2 6e by Jim Jenneson and Bob Harper Copyright © 2012 McGraw-Hill Australia.
Energy Management Cell, WBSEB Presentation on Energy Efficiency and Conservation.
RAMPS © Reliability, Availability, Maintainability, Predictability, Scalability Presented by Joe Soroka Presented by Joe Soroka For additional information.
Presentation : IMS – Tech Managers ConferenceAuthor : IMS StaffCreation date : 08 March 2012Classification : D3Conservation :Page : # 04 - Power and Control.
Winding Resistance Testing ndb Technologies WRT-10.
1 by L Goel Professor & Head of Division of Power Engineering School of Electrical & Electronic Engineering Nanyang Technological University,
Engine management systems Scuola di Dottorato di Ricerca Road vehicle and engine engineering science 1 THE ENGINE MANAGEMENT SYSTEM FOR GASOLINE.
MFG Assessment Application: Assessment Criteria and Metrics 1 Performance assessment criteria and metrics may be used as the basis for determining the.
contents Introduction What is power factor Importance of power factor Disadvantages of low power factor Calculation of power factor.
1 Summary of Papers 1. P. Sauer and M. Pai, Power System Steady-State Stability and the Load Flow Jacobian, IEEE Transactions on Power Systems, Vol. 5,
PCI Bus CENG Spring Dr. Yuriy ALYEKSYEYENKOV 2 The PCI (Peripheral Component Interconnect) bus was developed as a low-cost, processor-independent.
Workshop on Future AS in ERCOT ERCOT Public 1 Future Ancillary Services (AS) Workshop Joel Mickey, Dan Woodfin, Julia Matevosyan, Sandip Sharma, Fred Huang,
1 WECC Modeling and Validation Work Group Report to TSS August 2007 Dmitry Kosterev Bonneville Power Administration Transmission Planning.
REVIEW Green Professional Building Skills Training Electrical Systems.
AGC of UAE Power System Done by: Awad Saleh Abdulla Al.Harthi Muhammed Usame Suzen Aadel Ahmed Al.Mehrezi Graduation Project.
UNIT – V I: Telephone Instruments and Signals The Subscriber Loop, Standard Telephone Set, Basic Telephone Call Procedures, Call Progress Tones and Signals,
MVWG Report to TSS August 2011 Stephanie Lu Puget Sound Energy.
ENERGY CONVERSION ONE (Course 25741) CHAPTER FIVE SYNCHRONOUS GENERATORS.
SENSORS FOR BIOMEDICAL APPLICATION Engr. Hinesh Kumar (Lecturer)O.
Schunk Kohlenstofftechnik SKT / GB4 Page: 1 Frequently asked questions Frequently asked questions - FAQ.
Distributed Computing Dr. Eng. Ahmed Moustafa Elmahalawy Computer Science and Engineering Department.
Transit Capacity & Quality of Service Manual, 3rd Edition Rail Transit Capacity.
Page 1 © , R.Levine Digital Telecommunications Technology - EETS8320 Fall 2006 Lecture 2 Analog and Digital Telephone and Wireless Sets (Slides.
1 Electrical Machines Chapter Outline Introduction Induced voltage Electromagnetic force, f Simple loop generator
ISO New England Demand Resource Measurement & Verification Standards Manual Overview April 11, 2007 NAESB Development of DSM/EE Business Practices Washington,
© 2016 SlidePlayer.com Inc. All rights reserved.