Presentation on theme: "TrueSTEAM™ Humidification Systems Module 4: Advanced Installation."— Presentation transcript:
TrueSTEAM™ Humidification Systems Module 4: Advanced Installation
Supplemental to Module 3 ‘Basic Installation’ Additional criteria for - Step-by-step instruction - Remote installation - Installation in finished space - Auxiliary plumbing requirements Key Learning Installing TrueSTEAM™ in unique applications
What’s in the Remote Kit (#50024917)? A. Insulated hose (10 or 20 ft) B. Remote duct nozzle C. Remote humidifier nozzle D. Foam gasket for remote nozzle E. Support hooks (7 or 14) F. Hose clamps (2) G. Drywall anchors (4) H. TrueSTEAM screws, 1-1/4 in. (4) I. Support hook screws, 3/4 in. (7 or 14)
Additional Materials May Be Required If… Remote hose has a downward slope. You must use a 212°F rated Tee and P-trap. Do not use a plastic Tee. TrueSTEAM is using an auxiliary drain. You must install a wetted drain trap or condensate pump rated at 212°F. Pump must have total minimum capacity of 1 gallon per minute water flow for the vertical rise of the installation. TrueSTEAM is installed in a living space. You must install a drip pan with overflow wet switch under the TrueSTEAM.
Installation Precautions Refer to the remote mount kit installation guide (form # 69-2317) for a complete listing of these precautions. Failure to comply with the installation manual may result in voided warranty.
Tools and Parts Needed Basic tools needed to install TrueSTEAM™ - Wire cutter/stripper - Torx driver T-20 and T-30 - Standard screwdriver - 1-3/4-in. diameter hole saw - 1/8-in. drill bit - 18-gauge wire (up to 5 conductor) Other optional parts for advanced installations: - Condensate pump rating of 212°F (100°C) if used. - Drip pan with water sensor shut-off required underneath TrueSTEAM if installed in or above finished space.
Step 1: Choosing a Location Endless Installation Options
Step 2: Install Remote Humidifier Nozzle Remote adapter nozzle should be pitched upward when installed correctly.
Step 6: Plumbing Use only cold water. Do not use hot water supply. a. Water Filter. Insert 1/4-inch copper or plastic water line. Apply modest pull to ensure a tight fit. b. Back-flow preventer valve. Insert 1/4-in. copper or plastic water line. Apply modest pull to ensure a tight fit. c. Connect 1/2-in. drain tube. Secure drain tube to barbed fitting with hose clamp. d. Shut off the water supply. Secure 1/4-in. copper or plastic water feed tube.
Step 6: Plumbing - Auxiliary Plumbing Options Choose the plumbing option that suits your installation. Use A, B, C, or D based on type of pipe or condensate pump. Consult and follow local plumbing codes in addition to these instructions.
Common Remote Mounting Mistakes to Avoid a. Sharp hose bends. Horizontal run does not have minimum pitch of 2 in. per ft. b. Sharp hose bends. Hose not continuously supported at least every 12 in., resulting in hose sag. c. Sharp hose bends. Does not have at least 6 in. vertical rise immediately out of humidifier, and nozzle is not pitched up. d. Horizontal run does not have minimum pitch of 2 in. per ft. Sharp hose bends. Downward pitch does not have trap at its lowest point. a. b. c. d.
Support Materials Detailed Training Materials on Installation Available! Visit www.forwardthinking.honeywell.com Enter literature form: #69-2285: TrueSTEAM Installation Manual #69-2317: Auxiliary Plumbing and Installation Optionswww.forwardthinking.honeywell.com
Module 4: Advanced Installation Supplemental to Module 3 ‘Basic Installation’ Additional criteria for - Step-by-step instruction - Remote installation - Installation in finished space - Auxiliary plumbing requirements Key Learning Installing TrueSTEAM™ in unique applications