We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byMarisa Brumitt
Modified about 1 year ago
© Siemens Industry, Inc. 2011 Confidential / Drive Your Business Forward Ignite the Power of New Products and Partnerships Siemens Fire Partner Summit
© Siemens Industry, Inc. 2011 Confidential / Sinorix updates Cerberus Pro and Releasing New Detection – Highlights for Releasing Sinorix 1230 Sinorix 227 Supply NFPA 2001 – 2012 Edition
© Siemens Industry, Inc. 2011 Confidential / Cerberus Pro Cerberus Pro and Releasing New Detection – Highlights for Releasing Sinorix 1230 Sinorix 227 Supply NFPA 2001 – 2012 Edition
© Siemens Industry, Inc. 2011 Confidential / Cerberus Pro Capable of 2 Independent Releasing Zones Can be used for the following types of suppression Clean Agents All devices must be on the local panel Pre-Action Single and Double Interlock Deluge Foam Open Architecture Programming
© Siemens Industry, Inc. 2011 Confidential / Cerberus Pro Releasing Module Maintenance Bypass switches that meet the NFPA 2001 requirement without extra hardware
© Siemens Industry, Inc. 2011 Confidential / Detection technologies Cerberus Pro and Releasing New Detection – Highlights for Releasing Sinorix 1230 Sinorix 227 Supply NFPA 2001 – 2012 Edition
© Siemens Industry, Inc. 2011 Confidential / Detection technologies OOH941 Smoke Detector Combined Dual Optical and Heat Technology Replaces the need for Ionization Smoke Detectors Sensitivity ranges that qualify for "High Sensitivity Smoke Detector" status in NFPA 76 Telecommunication Profile (Required for NFPA 76) Incipient Profile which is a High Sensitivity Profile
© Siemens Industry, Inc. 2011 Confidential / UL portfolio today HFP-11 HFPT-1 HFPO-11 (FS-250) Small to Mid Markets OOHC941 Advanced features Standard features OOH941 OH921 HI921 OP921 Detection technologies
© Siemens Industry, Inc. 2011 Confidential / Sinorix 1230 Cerberus Pro and Releasing New Detection – Highlights for Releasing Sinorix 1230 Sinorix 227 Supply NFPA 2001 – 2012 Edition
© Siemens Industry, Inc. 2011 Confidential / Sinorix 1230 All UL listings and FM approvals have been completed Manufacturing capabilities are at 100% Agent availability is good Most orders shipping in 10 business days
© Siemens Industry, Inc. 2011 Confidential / Sinorix 227 Cerberus Pro and Releasing New Detection – Highlights for Releasing Sinorix 1230 Sinorix 227 Supply NFPA 2001 – 2012 Edition
© Siemens Industry, Inc. 2011 Confidential / Sinorix 227 availability We are in a VERY GOOD position with HFC-227ea availability. Siemens' Global purchasing power has help us to secure additional agent At this time we believe we will have enough agent supply to meet your needs for all of 2012 There could be some slight delays depending on usage and delivery schedules but we do not expect this to be a significant problem
© Siemens Industry, Inc. 2011 Confidential / NFPA 2001 updates Cerberus Pro and Releasing New Detection – Highlights for Releasing Sinorix 1230 Sinorix 227 Supply NFPA 2001 – 2012 Edition
© Siemens Industry, Inc. 2011 Confidential / NFPA-2001 changes Design Concentrations have changed on all agents Class A HFC-227ea is now 6.7% NOVEC 1230 is now 4.5% Class C HFC-227ea is now 7% NOVEC 1230 is now 4.7% The Class C value above has a limitation All applications with a voltage 480VAC and below can utilize the values above Additional concentration testing will be required to protect facilities with voltages over 480VAC We are recommending using the Class C Value for all projects with 480VAC or less
© Siemens Industry, Inc. 2011 Confidential / NFPA-2001 changes Chapter 4 Section 4.3.4 Control Equipment 18.104.22.168 Removal of an electric actuator from the agent storage container discharge valve that it controls shall result in an audible and visual indication of system impairment at the system releasing control panel 22.214.171.124.1 Paragraph 126.96.36.199 shall become effective January 1, 2016 Chapter 5 Section 5.3.5 Where a clean agent total flooding system is being provided for the protection of a room with a raised or sunken floor, the room and raised or sunken floor shall be simultaneously protected 188.8.131.52* If only the space under the raised floor is to be protected by a total flooding system, an inert gas shall be used to protect that space 184.108.40.206 Each volume, room, and raised or sunken floor to be protected shall be provided with detectors, piping network, and nozzle
© Siemens Industry, Inc. 2011 Confidential / NFPA-2001 changes Chapter 5 Section 5.6 5.6 Duration of Protection. A minimum concentration of 85 percent of the adjusted minimum design concentration shall be held at the highest level of combustibles for a minimum period of 10 minutes or for a time period to allow for response by trained personnel 5.6.1 It is important that the adjusted minimum design concentration of agent not only shall be achieved but also shall be maintained for the specified period of time to allow effective emergency action by trained personnel Section 5.7 220.127.116.11.2 For inert gas agents, the discharge time required to achieve 95 percent of the minimum design concentration for flame extinguishment shall not exceed 60 seconds for Class B fuel hazards, 120 seconds for Class A surface fire hazards or Class C hazards, or as otherwise required by the authority having jurisdiction
© Siemens Industry, Inc. 2011 Confidential / NFPA-2001 changes Chapter 7 Section 7.4 7.4 Enclosure Inspection. Other than as identified in 7.4.1, the enclosure protected by the clean agent shall be thoroughly inspected at least every 12 months to determine if penetrations have occurred that could lead to agent leakage, if other changes have occurred that could change volume of hazard, or both. Where the inspection indicates conditions that could result in the inability of the enclosure to maintain the clean agent concentration, the conditions shall be corrected. If uncertainty still exists, the enclosure shall be retested for integrity in accordance with 18.104.22.168
Presented by John Lewandowski and Mike Larabel Inspection, Testing, and Maintenance of Kitchen Hood Systems Michigan Fire Inspectors Society Winter Educational.
Kidde Engineered Fire Suppression System 25 bar Equipment Hardware Engineered for use with 3M™ Novec™ 1230 Fire Protection Fluid.
NFPA-12 Edition 2005 What “IMPACT” will the changes to NFPA-12 have on the design and installation of a CO 2 system?
Kidde Fire Suppression Systems Engineered with 3M™ Novec 1230™ Fire Protection Fluid.
FIRE SERVICES AT DATA CENTRE. FM200 TRAINING COURSE.
Viking TotalPac2 FireFlex Dual / 1230 Systems Inc. Technical Presentation ASPE Cleveland, OH March 10th, 2010 Technical Presentation ASPE.
Hot /Cold Aisle Containment Traditional Data Center/Telco designs are changing significantly!
Marioff HI-FOG GPU Systems for the protection of Industrial Applications Marioff HI-FOG Training 5 August 2008 Amit Lior.
Fire Detection and Suppression Chapter 7 Special Extinguishing Systems.
NEXT GENERATION Kidde Engineered Fire Suppression System Designed for use with 3M™ Novec™ 1230 Fire Protection Fluid.
Maine State Fire Marshals Office1 Laws and Codes Relating to Existing Apartment occupancies in the State of Maine Mark Stevens CFI-II, CFPS, CFPE Inspections.
KURSUS PENGENALAN KEPADA PERKHIDMATAN MEKANIKAL DALAM BANGUNAN.
Subpart F - Fire Protection & Prevention ( ) Flammables/combustibles - Approved containers Fire protection program/equipment 2A fire extinguishers.
1 Carbon Dioxide System Design Chapter 9 Page 257.
1 Medium- and High-expansion Foam System Design Chapter 5 Page 166.
AUTOMATIC SPRINKLERS Sprinkler System OPERATION Automatic sprinkler system as a network of charged hose line (pipes) suspended throughout a facility.
1 © 2015 Eaton. All Rights Reserved.. Suggestion on How to Use Industry Trainers are encouraged to use this material in their sessions Download the presentation.
CNG STATION & GARAGE MODIFICATION CODES & STANDARDS Graham Barker Business Development Manager.
KB SYSTEMS KB SYSTEMS KB SYSTEMS KB Systems, Inc. Introduction KB SYSTEMS KB SYSTEMS Designer, manufacturer and installer of bakery.
FE Training School 2001 Kidde FM-200® Product Review Clean Agent Systems Clean Agent Systems.
2 IMPACT - THE FIRE PERMIT = Hot Work Permit 3 Welcome ! This course is linked to the use of IMPACT, so it is assumed that: You know how to use IMPACT.
By: Andrew Turchet. What is Aspirated Smoke Detection? In its simplest form a smoke detector Known as: ASD (Aspirated Smoke Detection) ASSD (Air Sampling.
1 Ultra High-speed Explosion Suppression Systems and Ultra High-speed Water Spray Systems Chapter 7 Page 209.
Spallation Neutron SourceOak Ridge December 5-9, 2005 Fire Protection Patrick Thornton, SNS/FPE June 9, 2008.
Control Rooms Serve as operations centers for the control and monitoring of a service or process Flight control rooms Power generation control rooms.
1 CXS490 - Pre-Engineered Fire Protection Systems Off-Road Vehicle Systems.
Water Mist Systems Chapter 6. Objectives Evaluate water mist as a potential halon replacement Discuss the applications for water mist systems Compare.
1 CXS490 - Characteristic of Fire. 2 Other Resources NFPA Standards (available through Seneca Libraries Link NFPA Handbook Manufacturer’s Technical Information.
3-1 NFIRS 3 Structure Fire Module. 3-2 ObjectivesObjectives The participants will be able to: –describe when the Structure Fire Module is to be used.
Marioff HI-FOG MAU Systems Marioff HI-FOG Training 4 August 2008 Amit Lior.
Student Book © 2004 Propane Education & Research CouncilPage Performing Pressure Tests on Gas Distribution Lines Gas personnel must understand.
Chapter 12 Systems and Equipment for Fire Protection.
Codes and Standards to be followed in the design and construction of the Green Energy facility National Fire Protection Assoc (NFPA); American Gas Association.
Student Book © 2004 Propane Education & Research CouncilPage Performing Gas Distribution System Leak Checks Requirements for vapor distribution.
CXS490 CO 2 Total Flooding Systems 1. Creation of an inert atmosphere in rooms or other enclosure (oven, ducts, etc.). Examples of application: Drying.
RP-2000 Series Deluge & Agent Releasing Panels Alex Luk 23 rd April 2008.
Denver Fire Alarm Test FUNDAMENTAL, POWER SUPPLIES, CIRCUITS, INSPECTIONS, TESTING and MAINTENANCE.
HVACR311 – Electrical for Refrigeration International Mechanical Code Relating to Refrigeration.
Page 1 April 2010 Building Technologies Product Presentation SINORIX TM CDT.
In today’s global business environment, the need for clean agent fire suppression has never been greater. Pem All.
The purpose of installing fire fighting equipments is to protect the public, property, and assets in fire emergency. Manufacturers of fire protection.
N.F.P.A. 13R Justin Bohlmann FIR-204. Table of Contents What is NFPA 13R? Grandfather Clause Identification Types of Sprinkler Systems –Wet-Pipe –Dry.
Business Owners and Managers and the Fire Code.
1 Air Conditioning International Mechanical Code Relating to Refrigeration.
Basic Fire & Life Safety for Radiation Safety Professionals Robert Emery, DrPH, CHP, CIH, CSP, RBP, CHMM, CPP, ARM Vice President for Safety, Health, Environment,
1926 Subpart J Establishes the requirements for welding and cutting in the construction industry Establishes requirements for equipment, fire protection,
Prevent False Alarms Eugene A. Cable, P.E., M.S.F.P.E. Life Safety Consultants NEHES Honorary Member 412 Horse Heaven Road Averill Park, New York
1 Exit Routes and Fire Protection. 2 Introduction Fires and explosions kill more than 200 and injure more than 5,000 workers each year There is a long.
1 HVACR318 – Refrigeration II International Mechanical Code Relating to Refrigeration.
© 2017 SlidePlayer.com Inc. All rights reserved.