We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byGenesis Ping
Modified about 1 year ago
Halon Systems Ch. 5, pages 88-99 HALogenated hydrocarbON not the same as halogen F, Cl, Br, I 1940’s - 1980’s extremely effective
Halon Systems gaseous agent worked at low concentrations (6-12%) stored as liquified gas relatively non-toxic blocked branching chain reaction class A, B, C
Halon Systems Chemicals that harm ozone layer CFCs ozone depleters phased out for environmental concern
Montreal Protocol 1987 agreement between 24 countries phase-out production by 1994
Exisiting Halon Systems Still legal Halon bank for decommissioned agent refill possible many have duplicate protection remove upon discharge
Halon Replacements next chapter clean agents drop-in replacement didn’t happen greater concentration required greater storage volume less effective
Halon Types and Composition Major use in WW II aircraft engines, fuel tanks
Numbering System 1st, carbon atoms 2nd fluorine atoms 3rd chlorine atoms 4th bromine 5th iodine
Numbering System Halon 130l CBrF 3 1 carbon 3 fluorine 0 chlorine 1 bromine
Streaming agents Halon 1211 gas at room temperature stored as liquified gas BP 25 F projected as stream portable extinguishers
Flooding agents Halon 1301 gas at room temperature stored as liquified gas BP -70 F rapid vapourization flooding systems computer rooms
Properties of Halon 1301 Flooding agent low design concentration (5-7%) harmless to equipment –non-corrosive –no residue relatively harmless to occupants
Properties of Halon 1301 continued Personnel Considerations no flame no products of combustion exposure 5-7 % OK if over 10% problems
Properties of Halon 1301 continued Products of Decomposition halons decompose with heat produce halogen acids HF, HBr, HCl very harmful
Properties of Halon 1301 continued Recommended Safety Features continuous alarm SCBA many exits signs training time delay
Design of Halon 1301 systems Storage liquified gas nitrogen gas as propellant 2 phase flow in piping vapour discharge
Design of Halon 1301 systems Types of systems 1301 for total flood [5-7% ] class A, B. C
Design of Halon 1301 systems Selection of Design Concentration for inerting –minimum 5% for flame extinguishment (surface) –5-8% deep seated fire –higher conc. –longer holding time
Design of Halon 1301 systems Calculate room volume L x W x H may deduct volume of solid objects
Design of Halon 1301 systems Calculation of Specific Volume (s) volume of Halon/mass ft 3 /lb s = 2.2062 + 0.005046 x T T = room temperature (F)
Design of Halon 1301 systems Correction for altitude if over 3,000 ft see table 5-4
Design of Halon 1301 systems Calculation of quantity (W) W = V x C x A (s) x (100-C)
Design of Halon 1301 systems W = weight of halon (lb) V = room volume (ft 3 ) s = specific volume of halon (ft 3 / lb) C = design concentration (%) A = altitude correction factor
Design of Halon 1301 systems Other factors extended discharge for leaky room normal discharge within 10 seconds minimize openings
1 CXS490 New Technology Inert Gas Fire Extinguishants.
NEXT GENERATION Kidde Engineered Fire Suppression System Designed for use with 3M™ Novec™ 1230 Fire Protection Fluid.
1 Carbon Dioxide System Design Chapter 9 Page 257.
Water Mist Systems Chapter 6. Objectives Evaluate water mist as a potential halon replacement Discuss the applications for water mist systems Compare.
1 CXS490 Chemical Extinguishing System Halocarbon Extinguishing System.
1 CXS490 - Characteristic of Fire. 2 Other Resources NFPA Standards (available through Seneca Libraries Link NFPA Handbook Manufacturer’s Technical Information.
Earth’s Changing Environment Lecture 5 Depletion of the Ozone Layer.
Dry and Wet Chem Systems Ch. 8, pages Dry Chemical Systems Dry Chem. System Components Dry Chem. Sequence of Operation Applications for Dry Chem.
Atmosphere Review Composition of air –Nitrogen (78%) –Oxygen (21%) –Water vapor (0.01-4%) –Argon (< 1%) –Carbon dioxide (0.037%)
The periodic table L.O.: Use the periodic table to find: the symbol of an element, metals and non-metals, halogens and noble gases. Explain the reactivity.
METO 737 Lesson 9. Fluorinated Hydrocarbons Developed in 1930 by the General Motors Research laboratories in seqrch for a non-toxic, non-inflammable,
Fire Extinguishers Essentials Chapter 6 Gwinnett County Fire Academy.
STOICHIOMETRY PRACTICE. 1. When solid aluminum chloride is heated at high temperatures, solid aluminum and chlorine gas are produced. a. Write and balance.
In today’s global business environment, the need for clean agent fire suppression has never been greater. Pem All.
1 CXS490 Carbon Dioxide Systems. 2 CO 2 recognized as a fire extinguishing agent for many years Used in fixed systems since before World War I. History.
To be effective an extinguisher: Must be readily accessible In working order Suitable for the hazard Large enough to control the size fire Must be readily.
Carbon Dioxide Systems 1.Carbon dioxide properties 2.Storage 3.Uses 4.Limitations 5.Types of systems 6.Local Application 7.Total Flood.
FE Training School 2001 Kidde FM-200® Product Review Clean Agent Systems Clean Agent Systems.
POLLUTION MANAGEMENT 5.6 Depletion of stratospheric ozone.
Federal Aviation Administration Status of Research & Testing to Replace Halon Extinguishing Agents in Civil Aviation Fire Safety Team FAA Wm. J. Hughes.
Ozone Depletion Sean Farrell. What is it? The ozone layer is a concentration of ozone molecules in the stratosphere. The stratosphere, the next higher.
1 Intro to Organic Chemistry Part 08: Alkanes and the Environment Chapter 10.
Our Natural Protection Against UV light. The Ozone layer that blocks out the sun’s harmful rays is being depleted. Todd Olsen Professor Kimball Chem 1A.
1 Medium- and High-expansion Foam System Design Chapter 5 Page 166.
Year 12 HSC Chemistry. * Is fixed – i.e. closed system for matter, but not energy! * Has many functions * Protection from cosmic rays * Keeping us warm.
Fire Hazards (this is not an introduction to urban warfare)
International Environmental Policy: Controlling Ozone Depletion.
Ozone Depletion and CFCs Madeline Midgett and Anna Lovelace.
Kidde Engineered Fire Suppression System 25 bar Equipment Hardware Engineered for use with 3M™ Novec™ 1230 Fire Protection Fluid.
CHAPTER 8 Copyright © 2007 Thomson Delmar Learning 8.1 Portable Fire Extinguishers.
The Ozone Hole. The Ozone Layer Stratospheric ozone Block 95% harmful UV radiation
CHAPTER 8 PORTABLE FIRE EXTINGUISHERS Copyright© Delmar is a division of Thomson Learning.
Federal Aviation Administration Status of Research & Testing to Replace Halon Extinguishing Agents in Civil Aviation Douglas Ingerson Louise Speitel Constantine.
Atmosphere and Climate ChangeSection 2 Objectives Explain how the ozone layer shields Earth from much of the sun’s harmful radiation. Explain how chlorofluorocarbons.
Outline of Presentation What is the Ozone layer? What is the Ozone layer? How is ozone created and destroyed? How is ozone created and destroyed? What.
Samuel Nii Tettey (Ergonomist). At the end of Session, participants should be able to: - Identify fire problems at the enterprise level and Conduct Fire.
CXS490 CO 2 Total Flooding Systems 1. Creation of an inert atmosphere in rooms or other enclosure (oven, ducts, etc.). Examples of application: Drying.
Question 16: Has the Montreal Protocol been successful in reducing ozone- depleting substances in the atmosphere? Deniz Ural.
OZONE and the ENVIRONMENT. Just what is Ozone? Ozone is a form of oxygen with a different chemical property Ozone differs from oxygen: Has a distinctive.
DAY ONE Chapter 13 Atmosphere and Climate Change Section 2: The Ozone Shield.
Depletion of Ozone Composition of Atmosphere Troposphere 0-12km thick; 75% of all gases in atmosphere; All weather happens here; Temperature falls with.
1 Global Change: Ozone Depletion Environmental Sustainability Educational Resources prepared by Gregory A. Keoleian Associate Research Scientist, School.
Group 17 Halogens By: Eli, Emma, Liz, Monica, and MJ.
Fire Extinguishers Team 6 Garrett Ellanson Jeffrey Ethier Sean Tacey.
5.6 Depletion of Stratospheric Ozone. Depletion of Ozone.
Atmosphere and Climate ChangeSection 2 DAY ONE Chapter 13 Atmosphere and Climate Change Section 2: The Ozone Shield.
ENVIRONMENTAL SCIENCE Chapter 13 Atmosphere and Climate Change 13.2 The Ozone Shield.
Chapter 2.3 Elements and Compounds -Pure Substances: Elements- simplest form of matter; unique properties; are on the Periodic Table; Au, Ag, Hg, K, N,
Haloalkanes Chapter 12 Alkanes. 2 In a haloalkane, one or more H atoms in an alkane is replaced by a halogen atom. Simple haloalkanes are named.
Discuss the problems associated with the use of CFCs and assess the effectiveness of steps taken to alleviate these problems By Narmada Harish & Daniel.
© 2017 SlidePlayer.com Inc. All rights reserved.