SHORE STATION… Power supply Selection Off-the-shelf Buck regulator. General ratings: Output Voltage = 10 kV DC Output Range = 9 – 15 kV Voltage tolerance within 2%. Output Power = 200 kW Current Limiting Capability = twice the rated current = 20 A. Local and remote control functions Self diagnostics capabilities
SHORE STATION… Power supply Selection Potential vendor for shore stations Manufacturer: Diversified Tech Model: Custom made. Specifications: Input: 3 phase 13.8 kW service. Output: 10kV / 200kW using the HV buck regulator technology. Over current protection: Above 40A. Solid state system will act as current limiter. Dimensions: 40” by 36” by 42” estimated.
SHORE STATION… Surge Protection Spark gap arresters Metal oxide varistor (MOV) ceramic, polymer or silicon rubber insulator Surge arresters are selected based on several ratings Energy absorption capability (or energy withstand capability) Maximum continuous operating voltage (MCOV) Temperature rise.
SHORE STATION… Vacuum Switches (Breaker) Types: Air Air-blast Magnetic quencher Oil Sulfur hexafluoride gas (SF6) Vacuum Solid-state
SHORE STATION… Vacuum Switches Vacuum breaker is used for systems under 36 kV. Pollution-free Fast Reliable Compact Light weight Requires small energy to operate.
S2S3 R1R2 S1S4 C DC CIRCUIT BREAKER … Stage 1- Normal closure
S2 R1R2 S1 S4 C S3 DC CIRCUIT BREAKER … Stage 2 - Interruption Current is routed through C Size of C is selected to prevent restrikes
R1R2 S1 S2S3 S4 C DC CIRCUIT BREAKER … Stage 3 – Discharging of Capacitor Cap is discharged through R2 to set the circuit for next switching
R1R2 S1 S2 S3 C S4 DC CIRCUIT BREAKER … Stage 4 – Soft Starting Soft starting resistance R1 reduces the inrush current during energization
S2S3 R1R2 S1S4 C DC CIRCUIT BREAKER … Stage 5 – Normal closure
Components Selection Vacuum Switches Voltage Rating Withstanding Voltage > 25kV Continuous Current Rating 20A or higher Release time Faster release time means smaller capacitor is required. Release time < 20 ms Lifespan, measured in cycles of operation Millions of operations
Components Selection Capacitor Voltage Rating 15-20kV rating Capacitance 1-10μF, depending on node location Size up to 600 cubic inches Lifespan Measured in hours of operation
Components Selection Resistors 2 Resistors: soft close and capacitor discharge Resistance value: Both are currently specified at 1kΩ Peak Voltage Rating: 10-20kV Peak Energy Rating Power dissipation more important in this application than average power, as resistors will be used for brief (less than one second) intervals
V RRM (maximum repeat reverse voltage): 20-25kV Continuous forward current Based on normal operation > 50 A Maximum Transient Current > 300A di/dt ratings > 100A/s Reverse leakage current ~ A Type: Stacked Hockey Puck
flux linkages theory a) the core b) the sheath. c) the insulation.
Cable Model …inductance Cable Inductance Where: = Total flux associated with the cable. = Total cable current.
Cable Model …Resistance The resistance per unit length of a tubular conductor is given by: The total cable resistance is thus given by:
Cable Model …Capacitance The cable capacitance per unit length can be calculated by the formula: Where, is the permittivity of the insulator. d is the outer radius of insulator c is the inner radius of insulator.
Cable Model …Seawater The current return is through the seawater. In near DC conditions the sea-water resistance and inductance are calculated as: R = 0.098 m/km. L = 2.221 mH/km. These values are frequency dependent.
Cable Model …Composite model For transient simulation, the steel core and copper sheath can be modeled as a composite conductor comp = 5.1753*10 -8 m. comp = 9.0788
TRANSIENT ANALYSIS… What is ATP? ATP is a universal program system for digital simulation of transient analysis of transmission systems. ATP has extensive modeling capabilities including power electronics, control, protection, etc.
Your consent to our cookies if you continue to use this website.