Presentation on theme: "The Smartest Line- Interactive UPS with Pure Sine Wave Output in High Frequency Technology."— Presentation transcript:
The Smartest Line- Interactive UPS with Pure Sine Wave Output in High Frequency Technology
Features Microprocessor controlling High Frequency Design with High Power Density Boost and Buck voltage regulation Pure Sine Wave Output Selectable output voltage via front panel Selectable operating mode via front panel Provide Overload, Short-Circuit, Overheat and Fan fail Protection. Available to connect external battery cabinet to extend the backup time Hot-Swappable / User replaceable battery design
Features Available for various installation environment with individual UPS & EBM case Output THD<5% with PFC load under Battery Mode Intelligent Slot for SNMP monitoring Available for 19” rack installation above 1.5Kva Green Power function to save battery energy with no load Smart RS232 and USB communication port Available to switch on UPS without battery EPO switch for operation safety
Models R750/500: Slim Type with 1U High 1000: Mini-Tower Type
Models 1500/2000VA: 19” Tower-Rack 2-in-1. UPS and EBM is in different chassis. 2U High.
Models 3000VA: 19” Tower-Rack 2-in-1. 2U High.
Rear Panel - 750/1Kva Input Power Cord Outlets RS232 USB RJ11/RJ45 connector R750 T1000
LED Panel ON/OFF Switch Self-Test/Silence Configuration Key Enter Key Load Level Battery Level Fault LED Bad Battery LED OPV Indicator Operating mode indicator Line Mode LED Battery Mode LED
Selectable Output Voltage The JPX provides the configuration key to let the user select the suitable output voltage by himself for 220Vac or 230Vac or 240Vac.
Selectable Operating Mode The JPX also provides the function to let the user to setup the acceptable operating mode for its application. Normal: Acceptable AC input voltage for +/-20%. Generator: No change to voltage window. However, the low frequency transfer point is changed to 40Hz and there is no limitation for high frequency transfer point. Wide Range: The acceptable AC input voltage will be changed to -30% ~ +20%. But the AVR transfer point would be not changed.
Comparison Table ItemJPXSGP APC Smart Intelligent Charging SystemVVV Auto-Restart when Power Return VVV Automatic self-testVVV AVR FunctionVVV Cold-StartVVV Flexible management CardVVV Audible AlarmVVV LED indicatorsVVV Remote ManagementVVV