Presentation on theme: "AP1000 Chilled Water System"— Presentation transcript:
1 AP1000 Chilled Water System HVAC SystemsAP1000 Chilled Water System
2 Central Chilled Water System VWS Design BasisContainment Isolation: Safety-related, seismic, ASME III, 1EProvides 40°F chilled waterVWS air-cooled chillers shall be designed for operation using outdoor air with a maximum summer design temperature of 115°F dry bulb / 85.5°F wet bulb and a minimum winter design temperature of -40°F based on 0% exceedanceVWS water-cooled chillers are designed for stable operation using Component Cooling Water System (CCS) water with a temperature range of 60 to 95°F.
3 Central Chilled Water System Sketch – High Capacity Subsystem
4 Central Chilled Water System Sketch – Low Capacity Subsystem