We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byPedro Coffer
Modified about 1 year ago
DNV GL © 2014 SAFER, SMARTER, GREENER DNV GL © 2014 Richard Schimmel ENERGY First Experiences with IEC 6185 Ed2 testing 1 DNV KEMA is now DNV GL
DNV GL © 2014 From KEMA to DNV GL 2
DNV GL © 2014 First Experiences with IEC 61850 Ed2 Contents What has changed in Edition 2? Testing experiences Next steps 3
DNV GL © 2014 What has changed in Edition 2? Larger scope from substation to power utility Many more Logical Nodes (LN): power quality, distributed energy resources, hydro power Hierarchy of logical devices -> improved grouping of LNs Extensions reduced to private data objects and private LN Added protection settings 4 Data Model
DNV GL © 2014 What has changed in Edition 2? 5 Communication Extended name length to 64/64 Simulated GOOSE <> Real GOOSE GOOSE fixed length encoding Tracking of services LTRK Supervision logical nodes GOOSE subscription = LGOS Sampled values subscription = LSVS Time = LTMS, LTIM Well defined error codes More precise specifications Mod = test, Operate with Test Local / Remote Reporting Control
DNV GL © 2014 What has changed in Edition 2? Many new “IED services” settings to improve the exchange between SCL tools Indexing of report control blocks SCL schema = 2007B.Jan 2014 New.IID = Instantiated IED Description New.SED = system engineering rights Setting group editing: FC=SE (in Edition 1 FC=SG) 6 SCL
DNV GL © 2014 Testing Experiences with Edition 2 7
DNV GL © 2014 Testing Experiences with Edition 2 What are the references for conformance testing? IEC 61850 Edition 2 parts 6, 7-x, 8-1 IEC 61850-10, Dec 2012 “IntOp2” TISSUES UCAIUG Server Ed2 Conformance Testing Procedures, version 1.0, April 2013 UCAIUG approved test procedure changes (TPCL), version 1.0 SCL schema, version 2007B.jan2014 8 www.tissues.iec61850.com iectc57.ucaiug.org/wg10
DNV GL © 2014 Testing Experiences with Edition 2 More precise testing possible due to improved specification in the standard Also the negative testing (errors) are well defined in the standard and well testable PIXIT is reduced because more information is available in the SCL More test cases, more testing! – Edition 1 = 239 test procedures – Edition 2 = 330 test procedures The TISSUE process was again a great help to quickly resolve ambiguities 9
DNV GL © 2014 Find the differences 10
DNV GL © 2014 Testing Experiences with Edition 2 11 Optional Edition 2 feature Device XDevice YDevice Z Time management: LTMS/LTIM Y YY GOOSE supervision: LGOS - Y - Service tracking Y - Y Simulated <> real GOOSE Y Y - Grouping of logical devices Y YY Protection settings - -Y
DNV GL © 2014 Edition 2 Certification next steps GOOSE performance test procedures for Ed1/Ed2 available, wait for Ed2 device Finalize the conformance test procedures for CLIENT, Q3/Q4 2014 Sampled value publishing testing is waiting for IEC 61869- 9 IS, 2015 Under discussion: conformance and/or interoperability testing of SCL engineering tools More manufacturers will implement Ed2 in more devices We look forward to test more Ed2 devices 12
DNV GL © 2014 Conclusions IEC 61850 Edition 2 standard is available and implemented in the first server products We are ready to perform Edition 2 conformance tests Utilities need to – Specify Edition 1 or 2 in the requirements – Check the Edition on the certificate(s) 13
DNV GL © 2014 SAFER, SMARTER, GREENER www.dnvgl.com First Experiences with IEC 6185 Ed2 testing Thank you 14 For more information Richard.email@example.com
Checking SCL Files for Improved Interoperability Joe Stevens Triangle MicroWorks
Join Us Now at: Enabling Interoperability for the Utility Enterprise And TESTING.
«Computer-Aided Design System for Digital Substation based on open standards IEC 61850, 61131, 61499» T. Gorelik, O. Kiriyenko LLC EPSA RUSSIA «Computer-Aided.
AMA ServerSim-G Use Cases (UC). AMA-SYSTEMS GmbH D Pforzheim August 2014 AMA ServerSim-G Use Cases Page 2 Content AMA-Systems GmbH.
IEC Substation Configuration Language and Its Impact on the Engineering of Distribution Substation Systems Dr. Alexander Apostolov.
Herbert Falk UCA IOP Group Meeting April 1, 2011 UCA Paris 2011 IOP Results Report ©2011 UCAIug Paris 2011 IOP Results - IEC UCAIug Pv1 1.
OpenSG and Conformity Bruce Muschlitz EnerNex Corporation Knoxville October 2009.
INTEROPERABILITY Tests IOP11/ IEC Interoperability with IEC IEC INTEROPERABILITY BETWEEN ABB, ALSTOM and SIEMENS STATUS REVIEW.
Power Quality Enhancements for IEC Winston CHUA Ywee Ming South-East Asia Business Development Manager Energy Management Solution September 19, 2011.
November 9-10, 2009 UCA IUG Testing Subcommittee Report Testing Subcommittee Report UCAI Users Group Meeting Charlotte, Nc, USA November 9-10, 2009 Bruce.
Megger - Substation overview product groups, 2600 products.
Enforcing Interoperability with the Open Archives Initiative Repository Explorer Hussein Suleman, Digital Library Research.
Engineering, Architecture, Construction, Environmental and Consulting Solutions © 2011 Burns & McDonnell Missouri Public Service Commission.
® Sponsored by SOS 2.0 Profile For Hydrology 90th OGC Technical Committee Washington, DC Michael Utech 26 March 2014 Copyright © 2014 Open Geospatial Consortium.
Enabling Interoperability for the Utility Enterprise And TESTING.
Sales Training Presentation IEC Client for Proficy.
Frankfurt (Germany), 6-9 June 2011 José Gonzalo – Spain – Session 3 – Paper 0422 ‘MINIMUM COMMON SPECIFICATION FOR SUBSTATION PROTECTION AND CONTROL EQUIPMENT.
לירן קציר Connectivity in Computers IEC TC 57 - Power system management and associated information exchange Established in 1964 – with focus.
ProcessIt Document Library 8.0 Controlled Documents Suite.
Wind, wave and tidal energy DNV serving the energy industry.
1 A step-wise path to e61850 with UML IEC TC 57 WG10 Laurent Guise (France) - leading Thierry Coste (France), Henry Dawidczak (Germany), Thierry Dufaure.
DNV GL © 2013 SAFER, SMARTER, GREENER DNV GL © 2013 Lighting & Advanced Controls Pilot Programs for AEP Ohio and Consumers Energy (Ohio and Michigan) 1.
UCA International Users Group The Quality Assurance Program prepared by the UCA ® International Users Group Testing Subcommittee UPDATED: 28 July 2008.
Nokia Internal Use Only Outline Status of the PAWS protocol document Open Issues – Review extensibility and IANA registries.
Rohan Joackhim Pinnacle Sports Policy Based Management In SQL Server 2008.
Mr. Harethe El Ouadhane IEC member for IEC MT14. |Infrastructure Business | Germany | Test Engineer & Expert (Internal Arc, Making, Breaking &
Adaptive Security for Wireless Sensor Networks Master Thesis – June 2006.
Sofia, Bulgaria | 9-10 October SQL Server 2005 High Availability for developers Vladimir Tchalkov Crossroad Ltd. Vladimir Tchalkov Crossroad Ltd.
CS Workshop 2007 PCS 3.0 Upgrade by Stefan Götte.
Understanding the IEC Standard 李嘉凱 指導教授：柯開維.
Team Gong CDR SDP10 1 /14 Comprehensive Design Review Team Gong: Jason Dodge Eric Every Andrew Hills Alan R Levin F.R.I.D.G.E.
Philips Research France Delivery Context in MPEG-21 Sylvain Devillers Philips Research France Anthony Vetro Mitsubishi Electric Research Laboratories.
DNV GL © 2013 Confidential April 10, 2014 SAFER, SMARTER, GREENER DNV GL © 2013 Confidential September 8, 2014 Jarred Metoyer ENERGY HVAC Permit Study.
DHCP Vrushali sonar. Outline DHCP DHCPv6 Comparison Security issues Summary.
DNV GL © SAFER, SMARTER, GREENER DNV GL © Tore Hartvigsen OIL & GAS Optique Project Dissemination 1 Summary.
© ABB - Page 1 Long lifetime guaranteed for IEC Designed for the future... SCL ACSI APP COM.
ATLAS Detector Description Database Vakho Tsulaia University of Pittsburgh 3D workshop, CERN 14-Dec-2004.
Scale Up Access to your 4GL Application using Web Services David Lund Sr. Training Program Manager, Progress.
Substation Automation (S.A) System Project Supervisor: Stuart Wildy.
UCAIug Annual Meeting 2009 November 9 th – 10 th, 2009 EPRI Office Charlotte, NC.
Joomla! Day France SEBLOD Version 2.0 for Joomla! 1.6.
1 CIM and UML Overview Terry Saxton Xtensible Solutions
© ABB - Page 1 IEC proven technology and innovation IEC UCA 2.0 IEC Communication concepts Data Models Ethernet Technology Process.
Image Distribution and VMIC (brainstorm) Belmiro Moreira CERN IT-PES-PS.
SCORM By: Akshay Kumar. SCORM 2 What we want? What is SCORM? What is SCORM? Connection with e-learning Connection with e-learning Application of XML Technology.
Facility Smart Grid Information Model Steven T. Bushby Engineering Laboratory WG1-N1605.
Product Tracking Database Sponsored by Aviation learning, Inc. The goal is to create an n-tier, client-server system that will track the product and order.
GE Multilin Copyright IEC Primer - Communication Networks and Systems In Substations February 16, 2005.
Conformance Mark Skall Lynne S. Rosenthal National Institute of Standards and Technology
© 2017 SlidePlayer.com Inc. All rights reserved.