Download presentation

Presentation is loading. Please wait.

Published byGuadalupe Sansom Modified over 2 years ago

1
www.crtech.com C&R Technologies, Inc. 9 Red Fox Lane Littleton CO 80127-5710 USA Phone 303.971.0292 Fax 303.971.0035 Refrigeration System Design and Analysis Brent Cullimore C&R Technologies

2
Background l Background å Vapor compression (V/C) systems are well established in the Automotive industry and HVAC, but are still emerging in thermal management of electronics å Modeling of V/C systems is only a few years old å In Automotive, driven by the need to meet EPA mileage/emissions standards: must use transient drive cycles as design criteria å Modeling helps address perpetual concerns such as start-up slugs, oscillations, oil and charge migration upon shut down, etc. l Purpose of this paper: å Share modeling “lessons learned” from Ford, Visteon, GM, Delphi, Danfoss, etc.

3
Fundamental “Lesson Learned” l Self-determination of pressure requires tracking refrigerant mass: full thermohydraulic solution required! Solve for pressures, qualities, temperatures, flow rates, heat transfer coefficients simultaneously Compressor, throttle performance Compressor, throttle performance Conserve loop charge Conserve loop charge Pressure prediction Pressure prediction Two-phase heat transfer Two-phase heat transfer Track liquid and vapor in evaporator and condenser Track liquid and vapor in evaporator and condenser Overall loop energy balance Overall loop energy balance

4
Example: Parametric Sweep l System Description å R134a working fluid å Air-cooled condenser (100ºF environment) å Rotary compressor (defined by performance maps) å Capillary tube throttle (0.030” x 10 ft) å with regenerative suction tube heat exchanger l Vary compressor RPM from 1000 to 3000 å Requires 800W to 1500W input power

5
Results: Compressor Exit Pressure Constant Inlet Pressure (Different systems!) Constant Charge Mass (Apples to apples!)

6
Cause of Difference Constant Inlet Pressure 7% increase in charge causes increased liquid “blockage” in condenser and evaporator

7
Solution: Generalized Thermal/fluid Analyzer SINDA/FLUINT Network Example

8
Example: Heat Exchanger Modeling Evaporator (R134a) Aluminum Heat Exch. Air Side to compressor or dryer from expansion device moist air in air and condensate out

9
Top level: The Whole Loop

10
Example: CAD-based Condenser Model Mix and Match Methods Condenser: 1D finite difference/volume thermohydraulics Pipe walls: 2D finite difference thermal Fins: 2D finite element thermal Air flow: 1D finite difference network Full parametric modeling

11
Layers of the “Computational Onion” Pseudo-steady thermal and thermohydraulics ( ~ 10 min.) Steady hydraulics, unsteady thermal( ~ 1 min.) Mass/energy storage without flow inertia( ~ 10 sec.) Flow inertia w/o mass/energy storage( ~ 1 sec.) Mass/energy and inertia, homogeneous equilibrium two-phase ( ~ 1 sec.) Nonhomogeneous equilibrium two-phase( ~ 1 sec.) Nonhomogeneous nonquilibrium two-phase ( ~ 0.1 sec.)

12
Two-phase Flow: What phenomena are important? l Homogeneous Equilibrium Flow å Phases at same temperature, same velocity å Flow regime mapping optional å Often adequate for VC cycles l Equilibrium Slip Flow å Phases at same temperature, different velocities å Flow regime information required å Enhances accuracy in VC cycles (better void fraction estimation) l Nonequilibrium Slip Flow (“two fluid”) å Phases at different temperatures and velocities å Usually not needed except for severe transients and high frequency instabilities or control systems V liq = V vap, T liq = T vap V liq < V vap, T liq = T vap V liq < V vap, T liq < T vap

13
Comparisons with Test: Using Equilibrium Slip Flow l From: “Improvements in the Modeling and Simulation of Refrigeration Systems: Aerospace Tools Applied to a Domestic Refrigerator,” Ploug-Sorensen et al. Danfoss, 1996. Cabinet TemperatureHi/Lo Pressures

14
Conclusions l Charge mass must be conserved in transients, parametric sweeps, sensitivity studies, etc. å Component-level approaches (effectiveness, average coefficients, etc.) are not suitable: limited to concept-level trade studies å Finite difference/volume subdivision of condenser and evaporator is suitable: tracks mass and “blockage” effects l Two-phase flow is not amenable to CFD approaches å but flow network modeling (FNM) is well suited for the task l Slip flow has been shown to improve accuracy, but full nonequilibrium nonhomogeneous (“two fluid”) modeling is usually not necessary

Similar presentations

Presentation is loading. Please wait....

OK

Review for Exam 2.

Review for Exam 2.

© 2017 SlidePlayer.com Inc.

All rights reserved.

Ads by Google

Download best ppt on cloud computing Ppt on javascript events w3school Ppt on ganga river system Ppt on 108 ambulance service Ppt on carl friedrich gauss Ppt on acid-base indicators Ppt on satellite orbit calculator Ppt on earthquake in china Ppt on inertial frame of reference Ppt on principles of object-oriented programming python