Presentation on theme: "ECDA Process for Cased Gas Transmission Pipelines"— Presentation transcript:
1ECDA Process for Cased Gas Transmission Pipelines Charlie HallManager, Special ProjectsMears, CPG
2ObjectivesReview the ECDA Process From a Technical and Regulatory PerspectiveReview On-Going Validation Efforts and our Casing Test Facility
3Technical Basis of the ECDA Process for Cased Pipelines Fundamentally the ECDA process seeks to determine if a corrosive situation potentially exists in the casing.AnodeCathodeMetallic PathElectrolytic PathIf the coating is free of holidays, an external corrosion cell cannot occur (absent disbonded coating issues).If a holiday is present, the highest risk of external corrosion occurs when the holiday is in contact with electrolyte.
4Technical Basis of the ECDA Process for Cased Pipelines If electrolyte is in contact with the holiday and the casing, indirect inspection tools can detect the holiday. Additionally, the holiday would be in the CP circuit and may be receiving adequate CP.If the casing is metallically shorted, the holiday will likely not receive any available CP. Available CP will seek the path of lowest resistance, which most likely is the metallic contact.These same principles apply to buried un-cased piping.
5Technical Basis of the ECDA Process for Cased Pipelines Situations that cause external corrosion in cased pipelinesMetallic contact between casing and pipelineElectrolytic contact between casing and pipelineAtmospheric Corrosion on pipeline in casingReference GRI-05/0200“External Corrosion Probability Assessment for Carrier Pipes Inside Casings”Casing Corrosion Direct Assessment – ECDALarry G. Rankin and Hussain M. Al MahrousJanuary 2005
6Principles of ECDA Process Development ECDA is a structured process that is intended to improve safety by assessing and reducing the impact of external corrosion on pipeline integrity.ECDA is a continuous improvement process targeted to identify and address locations where corrosion activity has occurred, is occurring, or may occur.
7DOT Code Requirements for the ECDA Process Per DOT Part , DA can be used to assess the integrity of gas transmission pipelines for the external, internal, and SCC.Per DOT Part , DA must be performed in accordance with , , , and , and specifically ECDA in accordance with NACE RP0502.
8Application of NACE RP 0502 to Cased Gas Transmission Pipelines Per NACE RP0502, Table 1, Cased crossings requires a separate ECDA region.Per NACE RP0502, Table 2, indirect testing methods are “applicable” for shorted casings.Per NACE RP0502, Table 2, indirect testing methods for cased piping are “Not Applicable: Not applicable to this tool or not applicable without additional considerations.The ECDA Process we have developed for Cased Piping addresses the NACE RP0502 requirement for “additional consideration” and fully complies with DOT part 192 and NACE RP0502 protocols.
9Mears solicited a clarification to footnote #3 Table 2 from PHMSA Quote from that clarification – one bullet second clarification include in regards to footnote #3Answer B – is intended to assess the integrity of the pipe including cased pipelines
10The ECDA Process for Cased Pipelines The Cased Pipeline ECDA Process looks to find areas where corrosion may have or may be occurring, just like the ECDA process for buried uncased pipelines.The Cased Pipeline ECDA Process uses the same 4 steps as used for buried uncased pipelines.
11The ECDA Process for Cased Pipelines The Cased Pipeline ECDA Process meets the same protocol requirements as for buried uncased pipelines (ie. immediate, schedule, monitored conditions, minimum excavation requirements, etc.).The Cased Pipeline ECDA Process utilizes Guided Wave Ultrasonic Inspection as an additional Indirect Inspection Tool concurrent with ALL Direct Examinations.The Cased Pipeline ECDA Process is being designed using the knowledge gained from the smart pig results of 1201 cased pipelinesThe process is being validated both in the field and using a newly constructed Casing Test Bed
12Pre-AssessmentCollect all required data elements (additional elements have been identified for cased pipelines)Must be Feasible to perform ECDA on cased pipelineMust be able to indirectly examineMust be able to directly examine both ends (if necessary) and comply with all of the PHMSA guided wave target itemsMust establish meaningful segments and regions for cased pipelines that pass the “red face test”
13Has the ability to detect corrosion wall loss Indirect InspectionIndirect inspection tools can detect metallic or electrolytic shorted conditionsPCM (NACE RP 0502)PCM with A-FRAME (NACE RP 0502)P/S & C/S Potentials (including CIS both sides)Internal Resistance (NACE RP 0200)Cycling the Rectifier (NACE RP 0200)Pipe/Cable Locator (NACE RP 0200)Panhandle Eastern Method (AGA)Has the ability to detect corrosion wall lossGuided Wave (Guided Wave UT Target Items)
14Are Tools Complimentary? The word complementary can mean different things to different people.Typically “complimentary” suggests something that adds value, reinforces, or supplements something else.When someone says you and your spouse compliment one another, it suggests that the two of you are better as a whole, and you make up for each others’ strengths and weaknesses.
15Are Tools Complimentary? The IITs for Casings are complimentary.The tools look for the same potential corrosive conditions, but they do so in slightly different manners.This can help to account for the strengths and limitations of each tool.This is also true for the IITs that are used to assess buried pipelines.
16Indirect Inspection Severity Guide CASED PIPELINE INDIRECT INSPECTION METHOD INDICATIONS & SEVERITY GUIDECOMMON NAME OF TOOLTYPE OF TOOLMINOR(NO PATH INDICATED)MODERATE (ELECTROLYTIC PATH)SEVERE (METALLIC CONTACT)P/S & C/S POTENTIALSELECTRICAL POTENTIALP/S & C/S "ON" DIFFER BY MORE THAN 100 mVP/S & C/S "ON" DIFFER BY 10 mV TO 100 mVP/S & C/S "ON" DIFFER BY LESS THAN 10 mVPIPE CURRENT MAPPERAC CURRENT ATTENUATIONCURRENT LOSS ACROSS CASING < 5%CURRENT LOSS ACROSS CASING 5%-25%CURRENT LOSS ACROSS CASING > 25%PCM WITH A-FRAMEAC VOLTAGE GRADIENTNO INDICATION AT EITHER ENDINDICATION < 80 dBmAINDICATION > 80 dBmAINTERNAL RESISTANCEELECTRICAL RESISTANCEPIPE-TO-CASING RESISTANCE > 0.5 OHMP-C RESISTANCE TO 0.5 OHMP-C RESISTANCE < 0.01 OHMCYCLING THE RECTIFIERCOMPARE P/S & C/S POTENTIAL SHIFTS>100 mV DIFFERENCE C/S SHIFT < 25% P/S SHIFT10 mV-100 mV DIFF. & C/S 25%-75% OF P/S SHIFT< 10 mV DIFF. & C/S > 75% OF P/S SHIFTPIPE/CABLE LOCATORRADIO SIGNALNO SIGNIFICANT SIGNAL LOSSMODERATE SIGNAL LOSSNEAR TOTAL SIGNAL LOSSPANHANDLE EASTERN METHODREVERSE CURRENT APPLIED TO CASINGADDITIONAL TESTING REQUIRED TO DEFINEPIPE-TO-CASING RES < 0.01 OHMCASING/PIPE CAPACITANCETINKER & RASOR MODEL CE-IT"CLEAR" DISPLAYNONE"SHORTED" DISPLAY
17Indirect Inspection Classification of Indirect Inspection Testing Indirect Inspection ResultsDE PrioritizationAny indication of a Metallic Short or Electrolytic PathImmediateNO indication of either a Metallic Short or Electrolytic PathMonitored11For casings that were identified with some history of either a Metallic Short or Electrolytic Path but are not presently indicating the same , the DE Priority will be moved to the Immediate category and require direct examination during the first application of the ECDA process..
18Direct Examination Must be performed per NACE RP0502. Minimum direct examinations per NACE RP0502 protocols (ie. All immediates, 2 worst case monitored for 1st time through)Guided Wave ultrasonic indirect inspections must be performed during all Direct Examinations. Any metallic shorts or indications of electrolytic paths must be cleared prior to inspection.
19Direct ExaminationGuided Wave must comply with all of the PHMSA Guided Wave Target Items, or exceptions documented with technical basis.
21Summary of Smart Pig Results 1201 cased pipelines smart pigged from 2004 to 2006.144 of the 1201 cased pipelines (12%) had anomalies with metal loss detected > 20%.20 of the 144 cased pipelines with metal loss >20% (1.6 % of all cased pipelines) were found with anomalies > 80 feet from the nearest end of the casing.
22Summary of Smart Pig Results The lowest Pf/MAOP for any anomaly was 1.67, and the anomaly was within .1 feet of the end of the casing.The lowest Pf/MAOP for all anomalies > 80 feet from the end of the casing was 1.79 (anomaly 27% deep, 5.3” long).The results strongly suggest that external corrosion is not a significant threat to cased pipelines.
26Example of IIT Results on Casing Test Facility - PCM Distance70Clear ConditionSimulated Elect ShortSimulated Metallic ShortActual Elect Short100 ft231760170048250 ft21768015504710 ft19459313403951912181521491461048980NorthSouthAll readings in milli-amps, out of a total of 2 ampsPCM A-Frame detected location of 20%, 50%, and 80% anomalies in shorted conditions
27SummaryThe ECDA process and the NACE RP 0502 is applicable to cased pipelines.The process will improve the safety of cased pipelines by identifying when potential corrosive conditions occur, requiring direct examinations and remediation, in the same manner as required when applying ECDA on buried pipelines.The process will continue to improve, as the tools and the process are continually improved.