11 IGC Error Codes: From NSMM 2003 (SPP PPT) in HVACPartners Fault 2 – Limit Switch OpenIf limit opens:Gas valve and ignitor will be disableIndoor blower will immediately energized.Inducer shall remain energizedThe indoor blower will turn off after the fan off delay if “W” goes away.If limit closes again the fault will clear. If you still have “W”, the gas valve still open and re-igniton will occur.
12 IGC Service Reference Material NSMM 2003 SPP PPT IGC AlarmsTechnical Base / Hall EffectService Training GT54-01
13 Heat Pump Defrost Board New PN: HK32EA005Thermostat demands for1 or 2 stage Cooling2 stage HeatingEmergency HeatingDefrost Control in Heating ModeBased on RES HK32EA003
14 Controls: Heat Pump HPS High Pressure Switch Opens 660PSI. Close 505PSILPS Low Pressure Switch (A/C’s)Opens 54PSI. Close 117PSILiquid Line Loss-of-Charge (HP’s)Opens 27PSI. Close 44PSIFreeze Protection Thermostat (FPS)Opens 30F. Close 45FConnects to new defrost board
15 Reversing Valve Operation No O or B signal requiredEnergized in CoolingReversing Valve does not shift mode in Off cycle (No Dump)
17 Heat Pump Electric Heat Heating Stage 2Concurrent with compressor(s)Emergency HeatElectric Heat WITHOUT compressorsDefrost Tempering
18 Heat Pump Defrost Time-Temperature Sequence 1. Heat Run Time (30,60,90 or 120 mins) Factory 60 mins2. Initiate if tube temperature (DFT) low3. Terminate when tube temperature (DFT) rises or defrost run period reaches 10 minHH18SA261DFT Settings:Open: 30FClose: 80F
20 Controls: Electric Heat Accessory installation1 or 2 stagesFan housing limit switch (pilot, manual)Element line-break(or secondary contactor)Heater control contactor(s)
21 Electric Heat: Single-Point Box Required with all electric heater installationsSplice box with coverPower terminal blockTap conductorsIf FLA > 48-A:Fuse blocks and 60-A fuses
22 CONTROLS TERMINAL BOARD SERVICE MANUALCONTROLS TERMINAL BOARDCONVENIENCE OUTLETSSMOKE DETECTORS
23 Installation Instructions and Service Manuals (SM) The complete unit installation procedure (rig and position through start-up) will require reference to two (or more) technical manuals.Mechanical Installation: SI (II)Configure/Start-up/Troubleshoot: SM
29 Specific Topic Tech Support Smoke Detectors: Application Tip Cat# HKRNKA-1XA(integration with building alarm systems)PremierLink: Form 33CS-58SI (configuration, t-s)RTU-MP: Form 48-50H-T-2T (configuration, t-s)RTU-MP 3rd Party Integration Guide
30 Controls Terminal Board akaLight Commercial Terminal Board (LCTB)Command Center Terminal BoardCarrier PN HK50AA049UTEC PN CEPLArray of terminal strips, housings and QCsContains NO LOGIC, no software
39 Non-Powered COProvide a separate 115-v 15-A power supply and circuit disconnect from the buildingConnect to the duplex outlet in the unit’s splice boxInstall the weatherproof hinged cover
40 Powered COCheck local codes to determine if connecting the convenience outlet transformer to the LINE side of the unit disconnect is acceptable.If acceptable: Connect primary leads at the power transformer together as required for unit line voltage and connect to unit disconnect’s line side terminals.If not acceptable: Connect primary leads at the power transformer together as required for unit line voltage and connect to unit disconnect’s load side terminals.Install the weatherproof hinged cover.
51 Smoke Detector: Alarm Integration Application Tip Cat# HKRNKA-1XA
52 NEW FIOP: Unit-Mounted CO2 Sensor Same control logic as on accessory CO2No LCD display on sensorRequires PC access to configureSoftware and cable available thru RCDDetails to follow in full training program
54 2010 SRT Accessories Economizers & Roofcurbs CO2 & Enthalpy sensors Power ExhaustMotormasters (low ambient) and winter startLP ConversionsHigh Altitude Kits2-pos damper / Man damperThru-The-BaseLouvered Hail GuardsElectric Heat / Single PointPhase Monitor, Status switch, time guardPremierLink
55 Economizer Plugs Command Center aka Low Voltage Terminal Board (LVTB) ECON 10pin PlugUsed for all EconomizersSAT/OAT 4pin PlugUsed for Econ 2 onlyOCCUPANCY TerminalsUsed for Econ IV and 2-pos Damper12-Pin Plug (male) – Unit Side plug in Econ SectionSame plug and arrangement as old units12-Pin Plug (female) – Econ SideComes with specific FIOP or AccessorySmall change on the Econ IV plug
56 Economizer PlugsTable to help Troubleshoot Economizer wiring at the LVTB and the 12-pin plug
57 Economizer IV Electro-mechanical Unit Economizer Stand alone operation with Honeywell W7212 controller.Compressor control runs through the W7212If no econ then jumpers must be in 12-pin plug for cooling to operateActuator is 2-10 vdc pre-programmed ready for W7212 outputSAT in 12-pin plug (PL6)Same economizer as the R-22 machines.
58 Economizer IV Added occupancy control Low Ambient Lockout The “N” terminal tells the controller when occupiedR-22 units had W7212 main power fed from the IFC and jumper to the N terminal410a units have main power fed from transformer, and IFC feeds the N terminal trough the Occupancy terminalsSo W7212 is powered up when the unit is, instead of only when the fan is onLow Ambient LockoutThe “LA” switch is installed on the Y2 input to the controllerPart number HH18HA286, Contacts Open: 42°F ±5°F, and Contacts Close: 57°F. ±5°F.Below 42°F the second compressor will not run, econ will be stage one and 1st comp is stage 2Power exhaust wireTan wire that is connected to 24Vac HOT, move to EF1Add jumper from 24Vac HOT to EFConnect other end of the tan wire to the tan wire in the PE Kit harnessConnect the Grey wire in the PE kit harness to the 24Vac COM terminal
59 Economizer IV CO2 Sensor Enthalpy Power Exhaust (PE) IAQ install, uses 24Vac (TR & TR1), and 0-10Vdc signal (AQ & AQ1), TR1 & AQ1 are commonDemand Control Ventilation (DCV) is the only CO2 control available for Econ IV.DCV SET (POT) tells the controller at what input vdc from the IAQ sensor do we want to start opening the damperDCV MAX (POT) tells the controller at what damper position do you want us to stop opening for DCVThe damper will modulate between the MIN POS (POT) and DCV MAX (POT) settings proportional to the IAQ vdc input from DCV SET (POT) to 10VdcEnthalpyThe Single Enthalpy sensor uses the same terminals as dry bulb (SO+ & SO).For Differential Enthalpy, 2 enthalpy sensors required. One installed per above and the other on terminals SR+ & SR (after removing the resistor). Set the cross over POT to “D”Whichever is lower is the air used for coolingRemember O for outdoor and R for ReturnEnthalpy sensors are HH57AC078 and Dry bulb are HH57AC074Power Exhaust (PE)Terminals EF and EF1 are dry contacts and switch when the damper pos (in Vdc) gets above the EXH SET (POT) setting (in vdc)DCV – have to work with air balancer to determine the position of the damper and convert to input volts to the actuator. That Vdc is what MIN POS and DCV MAX need to be based on. For IAQ convert the Vdc output to PPM 0-10vdc to PPM, each vdc is 200 ppm.
61 Economizer 2 Econ2 No controller, requires Plink or RTU-MP/open Jumper wires in 12-pin plug for cooling operationActuator is 2-10vdc pre-programmed500 ohm resistor (pre-installed) required for 4-20 controller outputOAT in 12-pin plug (PL6)
62 Economizer 2 CO2 Sensor Enthalpy (only field installed) PE IAQ is installed on the specific controller via PL18 for FIOP and direct to controller when field installedDCV is set in the specific controller with a user interface.Enthalpy (only field installed)Single or Differential control from the DDC controllerUses the 2 loose Grey wires near unit’s 12 pin plugSensor wires run to the LVTB and then to DDCPEWires provided with the PE accessory have to be run to the control box specifically to which ever DDC is installedSwitch one stage on and off based on damper position
63 Economizer 2 Cooling jumpers must be in harness for cooling to work Resistor must be between the White signal wire and Black actuator commonActuator is 2-10v and controllers output 4-20mAEnthalpy sensor power from Actuator powerSwitch signal using 2 grey wiresWhen troubleshootingRead vdc across resistorDetermine if it’s the actuator or the controllerShorting the actuator signal to 24VAC will drive it 100%, but disconnect the actual signal firstSpring return ClosedDirection switch set to same direction as the spring return
64 2-Position Damper Opens to set position whenever the fan is running To set position, set the screw on the actuator face near the shaft opening
65 Low Ambient Winter start Kit (CRWINSTR001A00) Motormaster I (32LT) 3 minute timer relay to bypass low pressure switchField supply wires to tie into the LVTB, contact across LPS and coil between HPS and compressor contactorCurrent Literature – IIK-CRWNTRAN01-01Motormaster I (32LT)Wave Chopper, varies voltage to vary fan speed, single phase approved motors, clip on sensorMay need to replace motor and capacitor. Usage chart in literature.Copper Coil Controller with sensor – 32LT (230v), and 32LT (460v)MCHX coil controller with sensor – 32LT (230v), and 32LT (460v)Tries to maintain 100 deg SCT, unit operation down to -20 degCurrent Literature – IIK-32LT903-01
66 Low Ambient Motormaster II (CPLOWAMB001A00) Motormaster V Fan cycle switch, on/off only, single phase motors, clip on sensorTries to maintain high and low SCT, unit operation down to -20 degMotormaster VKits CRLOWAMB030A00, 031A00, and 032A00 for specific voltageFor use on three phase motors (48/50TC 14 and 50TCQ 12)VFD, varies frequency (HZ) to vary fan speed, 3 phase approved motorsPressure sensor on liquid line, unit operation down to -20 deg
67 Gas Conversion Kits High Altitude Conversion Four kits for use with LP and/or high altitude applications. Each contain 25 spuds, 5 of 5 different sizes.Manifold PressureNatural Gas still 3.5-in.wc.LP now 10.5-in.wc.High Altitude ConversionPick kit based on orifices neededUse only spuds and High-Alt label in kitSome spuds may have to be purchased separatelyLiterature contains conversion tables
68 Gas Conversion Kits LP Conversion New, low pressure switch on supply sideCloses at 10.2-in.wc. and opens at 7.2-in.wc.Gas piping included in kitsKits include springs for gas valve to operate at higher pressureLabels for LP and high alt (if needed)Chose Kit based on orifices needed, some orifices may have to be purchased separatelyLPS
69 Controls PremierLink RTU-MP RTU-Open FIOP or Accessory. If field installed make sure the CRPREMLK001A01 kit was also purchased. It has the harness for LVTB and the TB to install other accessories to.RTU-MPFIOP only and only available through mid-2009Overview training PES on partnersController training PES on PartnersOther information and tools on HVACpartners (CCN Support – Multi-Protocol Controls)RTU-OpenOnly FIOP until 3 Qtr 2009, then the retrofit should be availableReplaces the RTU-MP, direct replacementImproved control and improved networkingFixes battery memory with flash memory, otherwise hardware is the same
70 RTU-Open Support Contact Equipment Product support for: Open release – FIOP around June 2009– Accy around July 2009Contact Equipment Product support for:Specific base unit operation or problemsQuestions/problems with the Controller or how it controls the unit, if it was Factory installed (FIOP)Questions/problems with how the FIOP was installedController operation, start-up, configuration, and troubleshooting questionsContact CCN support for:Network Integration and Communication questions or problemsQuestions/problems with the controller if it was field installed (accessory)Questions/problems with the accessory installation