Presentation on theme: "Technical Training 2011. The thermal energy is measured in kcal (kWh or MWh) 1 kcal = is the energy necessary to raise up 1 °C temperature of 1 kg of."— Presentation transcript:
The thermal energy is measured in kcal (kWh or MWh) 1 kcal = is the energy necessary to raise up 1 °C temperature of 1 kg of water If we want to bring 50 liters (50 kg) of water from 10 °C temperature to 40 °C, we have cp x G x Δt = 1 x 50 x 30 = 1500 kcal = 1,74 kWh It is equal to use one hour radiator of 1500 kcal/h, which is aproximately 0,15 € (for traditional GPL boiler)
The heat Q used it is “counted” by the “heat gauge” The concept Fluid: water Use: Hot and Cold Plant Inlet Outlet
How to deliver the kit The Energy Box module is supplied without flow meters and without liters gauges to avoid any theft in the jobsite. The box is in zinc metal with key lock. + It is necessary to complete it with the DIRECT reading devices or with M-BUS net readers.
Components and operation The motorized 4 ways valves it is operated by a room thermostat. When the thermostat give the signal to open the valve, the water enter in the lodging and the calories meters quantify the energie consumption. The differential by-pass realize the pressure drops as a 4 ways valve completely opened. This in order to stabilize the flow conditions of the centralized plant. The Y filter it is fundamental for the circuit starting for the cleaning of the plant. Might be substituted by a balancing valve (optionl)Successively must be installed the energie meters and calories counters
The heat used in each lodging it is “counted” from the calorie-meter Plant installation sample Single Lodging Energy Box Room Thermostat
It is possible to measure also the thermic energie provided to the boiler or other device. Plant installation sample
The Range – Preassembled modules without manifolds
The Range - Preassembled modules with ¾” manifolds
The Range – Preassembled modules with 1” manifolds
Single Modules for heating/cooling and Hot Sanitary Water
Accessories for the pre-assembled modules The balancing valve (optional) must be fitted as Y filter substitution, for a correct tare of the plant.
Under-boiler Kit complete with energie consumption module. Permits the flow distribution in every lodgings having the MIXING DIRECTLY IN BOX, with possible mixed plant with high/low temperature. The balancing valve (included) permits to regulate the flow of water/heat in each lodgings.
Sanitary Water Underfloor Heating Circuits Heating -Distribution module for heating systems with low and high temperature. -Fixed point regulation for underfloor heating -Complete with consumption modules for heating and sanitary water -Complete with 2 ways DN25 Motorized Valve
Cabinet for heating/cooling and hot/cold sanitary water measuring consumption with several users. The cabinets are available up to maximum 4 lodgings or maximum 6 lodgings. The cabinets can be installed built-in or off-track and wall mounted.
The reading consumption of heating (hot/cold water) and sanitary water (hot/cold water) can be done in two ways: Directly from the display (DIRECT READ) Sending the data to a central station (M-Bus NET)
The MID Directive 2004/22/CE Directive from the European Parliament and 31 March 2004 council related to the measuring instruments. In March of 2004 the European Parliament issued the directive 2004/22/CE (MID). the device water gauges heat gauges The directive is applied to the device and to system with measuring functions which are defined in the specific attachments, related to water gauges, gas gauges and volume conversion, active electric energy counters and measure transformers, heat gauges, continuous and dynamic flow measuring systems different from water, automatic weight measuring systems, taximeters, dimension measuring systems, exhaust gas measuring gauges. The scope of the directive is to protect the final consumer which commercial transactions are connected to this instruments. 2004/22/CE Directive of the European Parliament and 31 March 2004 Council related to the measuring instruments. The directive foresee that the manufacturer accredit the counter gauge with a new mark: CE-M (totally different from CE mark). The CE-M mark certify the quality, the precision, the conformity of the counter gauge and the minimum parameters that grant the constancy of the precision, etc… protecting the consumers and the commercial deals.
A-MAGNETIC: does not get dirty and keep the precision during the time (minimum duration 10 years). LITHIUM BATTERIES: non removable LCD DISPLAY with 8 digits and special characters Direct reading energy device
Main screen level Total energy values in MW/h Reading values (calories and frigories) at certain date Date Test of the display Instantaneous Flow in m 3 /h Total volume (in m 3 ) from the installation date Instantaneous Power in kW Error code
Direct reading energy device Technical level Max Power in kW Max Flow in m 3 /h Inlet Temperature in °C Serial NumberOutlet Temperature in °C Functioning days from the tare day Impulse Values per Liters Difference of the Temperatures There is a Third Level indicating the main statistics data (i.e. reading of the data of the last 15 months).
Direct Read Volumetric Gauge for Hot Water Direct Read Volumetric Gauge for Cold Water
Pipe L=110 mm / L=130 mm Pipe Union Connection Kit Tee Flow Probe Holder
LITIUHM BATTERY non removable DISPLAY: LCD with 8 digits and special characters CABLE: for the connection to the M-Bus Concentrator Energy meter for data transmission A-MAGNETIC: does not get dirty and keep the precision during the time (minimum duration 10 years).
Hot water meter for data transmission Cold water meter for data transmission
It is necessary for the connection of maximum 2 counter liters to the M-Bus net Use 2 wires cables Maximum length: 10 meters Transform a signal arriving from a counter liters (1 impulse = 10 liters) in a M-Bus signal To be configured with MBCONF Software and Micro-Master device Pad A Battery: lasting 18 days/year for 10 years The battery must be activated !!! The adaptor must be activated opening the upper part of the terminal cover and positioning the jumper on both pins It works in case there is a current shot down! Impulse Adaptor
Energy Gauge (hot water only) for high flow rates with threaded connection and data transmission
Energy Gauge (hot water only) for high flow rates with flanged connection and data transmission
The MICRO-MASTER is necessary, joined with a PC with a USB port, for the correct operation and configuration of the system (assignment of the primary addresses). Porbes holder kit Micro - Master
M-Bus concentrator for 60 devices CONCENTRATOR CONCENTRATOR: collect the datas transmitted from the devices and permits the reading from the LCD display or thanks to a PC (with “serial port” or “serial modem 56K”)
Standard Modem Delivered already pre- configurated for the corresponding concetrator. Transformer 230/24 V 35 VA
Cable for data transmission via M-Bus protocol Telephone cable TRR 1 + T with 2 unsheathed twisted wires, complete with ground conductor Kit Modem GSM The kit is composed of: GSM/GPRS Dual-Band (EGSM900/DCS1800), antenna GSM, power supply unit AC/DC, serrial cable 9 pin RS232 for concentrator connection. Use a SIM Card enabled for DATA traffic (not included)
M-Bus net lenght The signal must not be distorted. An important matter is the lenght of the net (The sum of all the cables lenghts). Lower the reading speed of the data (Baud rate), the longer could be the wiring net. Baudrate96002400300 Max net lenght1 km4 km12 km
- Connect the PC to the Micro-Master - Connect the Micro-Master to the device (Impulses Adaptor or Calories Counter), using the “M-Bus net” contacts still free. - Using the MBCONF software, assign a 3 digits code to each periferical items (Liters Counter or Calories Counter). This code is the PRIMARY ADDRESS - The software automatically recognize for each devices the correspondent “serial number” (it is an 8 digit number). This code is the SECONDARY ADDRESS System Configuration
- Connect the PC to the M-Bus net, without using the Micro-Master - Using the software FSERVICE find out each devices - Export the data in an excel file NOTE: the periferical devices transmit the data with a certain speed called BAUD (“changings”/sec). For the searching it is important set up a speed field (baudrate) between 300 and 2400 baud, to have the security to find all the connected devices. Data Read
Your consent to our cookies if you continue to use this website.