Presentation on theme: "Industrial Firefighting Pool (IBP)"— Presentation transcript:
1 Industrial Firefighting Pool (IBP) Ing. Raymond BrasSpecial Projects, Unified Industrial & Harbour Fire Department
2 ? “Largest possible tank surface” ? Startings pointsDecisive fire scenario’s:? “Largest possible tank surface” ?Defined as:Largest tank (mineral: d = 89 m; h = 22 m)Largest tank (polar : d = 65 m; h = 30 m)Existing equipment Unified Industrial & Harbour Fire Department insufficient:Maximum capacity 3 industrial fire trucks + 3 large monitors insufficient: 45 meter diam. ( l/min)
3 Analysis Mobile FiFi system with a capacity of: Mobile – large surface (NFPA 11): 10,4 liter/m2/minMineral: 89 m 6221 m2 65 m3/minuutPolar: m 3318 m2 35 m3/minuutConcentrate ind.: (3%) 2 m3/min 120 m3 (3%) % spareDistance: 115 m to centre of tank at 22 m heightTransportation length: max m from watersideAnd employable within 4 hours
4 FinancesWho?18 companys (by regulations of environmental agency)VolunteersHow?By membershipsThree types: A, B of CA = Only foam concentrateB = A + monitors (Fifi-units)C = Total system
5 Which companies MOT Shell Europoort Nerefco Europoort TEAM KPE Exxon ROPMETNerefco PernisVOPAK EuropoortVOPAK TTRShell SNRLBCESSOVOPAK BotlekShell SNCOdfjellExxon RAPVOPAK Chemiehaven
15 Organisation Testresults very important for: Logistics: Pre-planning ProceduresEducation and trainingLogistics:Agreement with transport companyPreparing special trucksMaintenanceSmart storage
16 Foam concentrateTests to determine if our standard foam concentrate is usable;Method: Like Lastfire suited for IBP;(Crude oil, leaded petrol);Good results with Moussol APS 3/3;Also with 1% induction;120 m3 bought.