2Overview The ZXM10 EISU is an imbedded microprocessor system. It can monitor supervision signals of various base station power equipment and environments in real time, generate alarms, and make corresponding control as required.it is capable of networking downlink base stations, and networking by making effective use of base station communication resources.
3Description of EISU Models The ZXM10 EISU (V1.0) is a series product.
4Description of Common Models of the EISU 1ZXM10 EISU (48)Serial port and network interface for master communication, basic configuration for supervision factor, -48 V2ZXM10 EISU (2E-48)2M ring and front board for master communication, basic configuration for supervision factor, -48 V3ZXM10 EISU (1E-48)Back board for master communication, basic configuration for supervision factor, -48 V4ZXM10 EISU (1E-SS-48)Back board for master communication, extended configuration for supervision factor, -48 V5ZXM10 EISU (1E-SS-BT-48)Back board for master communication, extended configuration for supervision factor, battery capacity analysis function being integrated, -48 V
5FunctionsIn the basic configuration, the ZXM10 EISU provides 12 general AI/DI measurement channels, two general DI measurement channels and four DO channels to implement data collection and control of the unintelligent equipment. If an extended supervision unit is configured, eight general AI/DI measurement channels, two general DI measurement channels and four DO interfaces are added.The ZXM10 EISU has the dedicated sensor interface, where one digital temperature sensor, two battery channels for total voltage and one smog detector can be connected.The ZXM10 EISU provides multiple intelligent equipment protocol resolution interfaces to implement data collection and control of the intelligent equipment. (There are four to six interfaces and 20 intelligent devices can be connected.)The ZXM10 EISU has the picture supervision function. It provides two USB camera interfaces to process, store and forward picture data. The picture resolution is up to 640 480.
6FunctionsThe ZXM10 EISU provides multiple communication interfaces and networking modes. These transmission interfaces contain asynchronous serial ports, Ethernet interfaces and E1 interfaces. They provide the following networking modes: order wire channel, network, 2M protection ring, 2M chain, separate 2M and 2M extracted timeslot.The ZXM10 EISU provides the local storage function. The data within 15 days can be stored locally after the master communication is interrupted.The ZXM10 EISU provides the function of remotely or locally downloading the running program and intelligent equipment communication protocol program.The ZXM10 EISU has the functions of equipment self-diagnosis and fault self-location.The ZXM10 EISU provides the management function of real-time clocks.
7FunctionsThe ZXM10 EISU configured with the extended transmission board provides transparent Ethernet interfaces.The ZXM10 EISU provides the Web browsing function.The ZXM10 EISU supports the intelligent equipment center resolution function.The ZXM10 EISU supports energy saving for air conditioners.
8Panel IndicatorsThere are nine indicators on the EISU panel,
9Jumper and DIP Settings of EISU Basic configuration of EISU includes configuration to EISUP board, EISUM board, ETNM board, and EISUL board.EISUL boardETNM boardEISUP boardEISUS boardEISUM board
10Jumper and DIP Settings on EISUP Board Key components on EISUP board are as follow. In engineering practice,
11Jumper and DIP Settings on EISUP Board the jumper X7 on EISUP board must be at pin 2 and 3. DIP switch S2 use default setting.
12Jumper and DIP Settings on EISUM Board here are two DIP switches on EISUM
13Jumper and DIP Settings on EISUM Board boardS1.1~S1.8 and S2.1~S2.4 are AI type switches, ON means current type, OFF means voltage type.
14Description of External Interfaces-EISUM External interfaces of the EISU can be viewed when the cable cover is removed. The external interfaces are provided by the EISUM, EISUS and ETNM. The interfaces in the lower row are provided by the EISUM, and the interfaces in the upper row by the EISUS and the ETNM. The EISUS can change its location with the ETNM .
16Basic ConfigurationEISU network parameters and security console connection parameters.
17Board ManagementOn Channel Configuration subpage, sensor type, channel type, upper and lower limits of alarm, and return difference, and so on,
18Serial Port/Intelligent Port Management EISU has 7 serial ports in total.
19Intelligent Analysis Settings the red numbers are the order of the steps in setting intelligent analysis function.1. Click the down arrow next to Serial Port box and select 2/COM1.2. Click the down arrow next the Function box and select Intelligent Analysis.3. Click the Smart Port Configuration tab for intelligent port configuration.4. Select Smart DLL file config., click Select DLL File and select the intelligent device protocol file that you want to download.5. Click Set as Smart Port. The configuration program starts downloading the selected protocol file. You will be prompted that the protocol file has been downloaded successfully at the bottom left corner of the window.6. Click Read button.7. Click Modify. A Set Serial Port Parameter dialog box appears, as in shown in Figure 3.2‑13. Input the actual parameter values on the dialog box.8.Set communication protocol mode of serial port, simply select Timeout Receiving Means option button.Please note that the default setting is Header + Frame Tail (HEX). You need to select timeout receiving means by manual.9. Click Set to complete serial port parameters settings.
20USB Video ManagementIf USB device is closed, then all management and operation related to this USB device are unavailable. If USB device is available, relevant operation may be done.Please note that each time you open USB, initializing EISU and setting up parameters of camera that it connects may be required. This process takes about 5 seconds.Description on part of control parametersPeriod of Alarm: When there are successive same alarm messages occurring from a certain channel, if the time interval between any two of them is less than the time period that you set here, they will be recorded as only one alarm.Need for Light Control: Select this check box or clear it to select whether light flashes or not when alarm occurs. If select it, then the number of the related Light DO Channel also should be set.Channels Linked with Alarms: it means the number of channels that need to be handled by EISU. If the number is 0, then no channel is linked. Otherwise, you need to conduct corresponding configuration to each channel. After inputting channel number (generally 1~10)
22External access control mode Connect external access controller with EISU applied in dynamic IP networking.For example, connect CHD805AE in wireless dynamic IP networking or dynamic IP networking.1. Set the serial port connecting the device as soft transparent;2. Set up serial port parameters: baud rate, receive mode.
24Operation steps1.Select the serial port that is specified on engineering drawing in Serial Port box, and select Access Control in the Function box;2.Click Modify button to set serial port parameters.If Baud Rate is 9600, then the Waiting Time after Sending should be set as 2083;If Baud Rate is a value other than 9600, then the Waiting Time after Sending will be automatically set to appropriate value. EISU configuration program above V1.10 supports this function.3.For receive mode, you must select [Header (7E) +Tail (0D)];4.Set Function Parameters of Access Control Port:Server IP and Port No. do not need to be set.5.Door Magnetic Channel must be set as the exact channel that is connected in construction practice.
25Update of Application Program and Driver EISU supports remote downloading application program and driver.1.On the Basic Setting page, click Open button to find the application program file or driver.2.Click Re-download button and wait for downloading complete.