Presentation on theme: "Bulk Electric System John D. Martinsen, P.E."— Presentation transcript:
1Bulk Electric System John D. Martinsen, P.E. Snohomish County Public Utility District (SNPD)
24/11/2017SummaryPart 1“Performance Based” Bulk Electric System (“BES”) definitionBES definition(s)NERC, WECC, and electric industry efforts in defining the BESPart 2Examples of BPA Transmission and Distribution systems
3“Performance Based” BES Definition What function does the facility serve?local distribution service?support a WECC transfer path?If the facilities fail, do they impact other transmission owners and operators?
4Bulk Electric System Definition Task Force (“BESDTF”) 4/11/2017Bulk Electric System Definition Task Force (“BESDTF”)Western Interconnection development of a “performance based” standardFERC support of WECC effort in Order 743-ABPA comments on the revision of the ERO definition of the BES (Docket No. RM )“…Western Interconnection, utilities must use higher voltage facilities, i.e., 115 kV, to accomplish what is effectively a distribution function with in the utility. Where demonstrated, these facilities should be categorized as distribution network components, not as bulk electric system facilities…”“… Bonneville urges the Commission to provide an additional option for the ERO to submit a Regional Entities material impact methodology for Commission approval…”“…Agrees with the need to exempt FAC that have low impact on the BES…”“…Bonneville believes many facilities in the Western Interconnection rated at 100kV and above should not be included in the BES because they have no material impact on the bulk power system reliability…”
5Historic BES Definition 4/11/2017Historic BES DefinitionNERC Bulk Electric System Glossary of Terms approved by both the EC and OC at the July 16, 1996 Joint EC/OC Meeting:“A term commonly applied to the portion of an electric utility system that encompasses the electrical generation resources and bulk transmission system”“Transmission — An interconnected group of lines and associated equipment for the movement or transfer of electric energy between points of supply and points at which it is transformed for delivery to customers or is delivered to other electric systems”“Bulk Transmission — A functional or voltage classification relating to the higher voltage portion of the transmission system”“Subtransmission — A functional or voltage classification relating to the lower voltage portion of the transmission system.”
6Current BES Definition 4/11/2017Current BES DefinitionBES definition, NERC approved 2/8/2005, FERC approved 3/16/2007:“As defined by the Regional Reliability Organization, the electrical generation resources, transmission lines, interconnections with neighboring systems, and associated equipment, generally operated at voltages of 100 kV or higher. Radial transmission facilities serving only load with one transmission source are generally not included in this definition”
7Revised BES Definition at FERC 4/11/2017Revised BES Definition at FERC“Unless modified by the lists shown below, all Transmission Elements operated at 100 kV or higher and Real Power and Reactive Power resources connected at 100 kV or higher. This does not include facilities used in the local distribution of electric energy”With inclusions & exclusions listedApproved by the electric industry’s NERC ballot body and the NERC Board of Trustees
8Load Service Exclusions 4/11/2017Load Service ExclusionsRadial systems: A group of contiguous transmission Elements that emanates from a single point of connection of 100 kV or higher and:a) Only serves Load. Or..Note - A normally open switching device between radial systems, as depicted on prints or one-line diagrams for example, does not affect this exclusion
10Load Service Exclusions 4/11/2017Load Service Exclusions“Local Networks (LN): A group of contiguous transmission Elements operated at or above 100 kV but less than 300 kV that distribute power to Load rather than transfer bulk power across the interconnected system. LN’s emanate from multiple points of connection at 100 kV or higher to improve the level of service to retail customer Load and not to accommodate bulk power transfer across the interconnected system”
11LN Characteristics The LN is characterized by all of the following: 4/11/2017LN CharacteristicsThe LN is characterized by all of the following:b) Power flows only into the LN and the LN does not transfer energy originating outside the LN for delivery through the LN; andc) Not part of a Flowgate or transfer path: The LN does not contain a monitored Facility of a permanent Flowgate in the Eastern Interconnection, a major transfer path within the Western Interconnection, or a comparable monitored Facility in the ERCOT or Quebec Interconnections, and is not a monitored Facility included in an Interconnection Reliability Operating Limit (IROL).
13FERC’s Seven-Factor Test Presented by:Philip HanserJune 13, 2012
14Agenda Overview of FERC’s Seven-Factor Test Application of the Test by State CommissionsApplication of the Test by FERCTakeaways
15FERC’s Seven-Factor Test for Local Distribution Facilities In Order 888, the FERC set out a seven-factor test to distinguish distribution facilities from transmission facilities when establishing whether the delivery component of an unbundled retail power sale was transmission or distribution:local distribution facilities are normally in close proximity to retail customerslocal distribution facilities are primarily radial in characterpower flows into local distribution systems, and rarely, if ever flows outwhen power enters a local distribution system, it is not reconsigned or transported on to some other marketpower entering a local distribution system is consumed in a comparatively restricted geographic areameters are based at the transmission/local distribution interface to measure flow into the local distribution systemlocal distribution systems will be of reduced voltage
16State Case 1 (Iowa Utilities Board): MidAmerican Energy Co State Case 1 (Iowa Utilities Board): MidAmerican Energy Co. Order Issued April 30, 1999In November 1998, MidAmerican filed a petition for an Iowa Utilities Board order recommending delineation of local distribution facilities (subject to Board’s jurisdiction) and transmission facilities (subject to FERC jurisdiction).MidAmerican proposed to classify all lines 69 kV and below as well as certain 161 kV lines as distributionClassification of 69 kV and 161 kV lines was contestedThe Board noted that:In accordance with Order 888, FERC will defer to states’ determinations of which facilities are transmission vs. distribution.Such delineation is only needed when states unbundle retail rates—FERC has said that the delineation is not required when states only implement retail access programs of short length (deemed “pilots” or “experiments”).In administering the Test, “some lines or facilities classified as distribution may not meet all the indicators of distribution lines.”No single factor is determinative and all factors should be evaluated and weighted in establishing the delineation.
17Board’s Discussion of Evidence 161 kV lines (in Waterloo) satisfied all FERC factors except #7:Factors 1 and 5: Lines are in close proximity to retail customers in a comparatively restricted area.Factor 2: Although not radially configured, the lines function and provides service as though they are primarily radial in character.Factor 3 and 4: Power rarely, if ever, flows out of the system and is not transported out to another market.Factor 6: Equipment installed at each interface distinguishes transmission system vs. distribution system power flows.Factor 7: The 161 kV Lines do not appear to meet the reduced voltage test of Factor 7.However, since “the lines meet an overwhelming preponderance of the factors, the Board believes it is most reasonable to classify them as distribution.”69 kV lines satisfied all FERC factors
18FERC Case 1: California Pacific Electric Company (CalPeco) Order Issued October 7, 2010 CalPeco is a California Company formed for the purpose of acquiring the assets and operations of Sierra Pacific Power Company electric distribution system in CA (“California Distribution System”)Due to geographic remoteness of some parts of the service territory, as well as historic interconnections, CalPeco was required to provide “minimal” delivery and reliability services to Sierra to enable Sierra to reliably supply power to its Nevada customersCalPeco made several requests to FERC, including that it declares that all distribution facilities that are acquired by CalPeco are considered to be local distribution facilities.CalPeco argued the application of the seven-factor test confirmed that the California Distribution System should be classified as a local distribution system
19CalPeco’s Arguments Test Factors CalPeco’s Claim # 1local distribution facilities are normally in close proximity to retail customersCustomers are concentrated in the South Lake Tahoe and North Lake Tahoe areas, and virtually all customers are served by distribution facilities within 15 miles.2local distribution facilities are primarily radial in characterAbsent an emergency situation, the system is exclusively radial in nature. Power only flows in one direction. The only generation on the system is Kings Beach, which is used for emergency back-up purposes and limited to producing no more than 1,400 MWh/yr.3power flows into local distribution systems, and rarely, if ever flows outAll power is exclusively consumed by consumers within CalPeco service territory with some exceptions [see next slide]4when power enters a local distribution system, it is not reconsigned or transported on to some other marketNo power entering the system will be transported to electric markets. Power leaving the system will be used by retail customers of other utilities located in close proximity to the system. [see next slide]5power entering a local distribution system is consumed in a comparatively restricted geographic area6meters are based at the transmission / local distribution interface to measure flow into the local distribution systemPerimeter metering will be installed and maintained to measure all flows into and out of the system.7local distribution systems will be of reduced voltage1400 miles of 12.5 kV, 14.4 kV, and 25.9 kV distribution circuits, 75 miles of 60 kV distribution lines, and 19 miles of 120 kV distribution lines. FERC has not established a definition of what constitutes a reduced voltage distribution line. The limited nature of the three 120 kV distribution lines, combined with the fact that the remaining lines are 60kV or below, satisfies Factor 7.
20CalPeco’s Arguments (cont’d) FERC found that:The California Distribution System meets factors 1, 2, 5, 6, and 7The application of factors 3 and 4 is somewhat complicated in this case. CalPeco described four instances, in which power actually flowed out of the California Distribution SystemHowever, power flowing out of the California Distribution System would be for: (1) border communities; or, (2) emergency assistanceBased on the “totality of circumstances” the California Distribution System met the seven-factor test.
21FERC Case 2: City of Pella, Iowa Order Issued February 2, 2011 Pella owns and operates a municipal electric utility in Marion County, IA—the electricity is distributed by Pella to residential, public, and industrial customers with retail boundaries prescribed by the state of Iowa.Pella has been a MISO market participant since 2004 and a network integration transmission service (NITS) MISO customer since Sep (when MidAmerican joined MISO)—prior to that, Pella bought point-to-point transmission as needed.Pella requested that the FERC reclassify its 69 kV facilities as transmission facilitiesFERC noted that, in the late 1990s, MidAmerican asked the Iowa Commission to reclassify all lines 69 kV and below as distribution, including the lines that interconnect with Pella’s 69 kV facilities.The Iowa Commission accepted MidAmerican’s reclassification proposal and the FERC adopted the determination in 2000 [see earlier slides on State Case 1].
22Pella’s Arguments in Support of Transmission Classification #Test FactorsPella’s Claim1local distribution facilities are normally in close proximity to retail customersInterconnections at the Pella West and Pella East Substations support service to areas served by MidAmerican and CIPCO within a 30 mile radius of Pella. The 69 kV facilities are essential to complete imports and exports of power across a wide region and allow for transmission over a broad region.2local distribution facilities are primarily radial in characterThe 69 kV facilities are looped and are interconnected with “other utility transmission” linking them with multiple sources of power and markets. Each of its 69 kV lines serves a number of transmission functions. The facilities together allow power to flow from the facilities of Pella, MidAmerican, CIPCO, and ITC Midwest to the transmission facilities of these and other utilities.3power flows into local distribution systems, and rarely, if ever flows outPower flows across its 69 kV facilities are bidirectional and power flow data establish that power flows into, across, and out of these facilities on a regular basis.4when power enters a local distribution system, it is not reconsigned or transported on to some other marketPower flows across the 69 kV facilities to other markets, including CIPCO and MISO. The facilities enable the sale and purchase of power as well as interchange.5power entering a local distribution system is consumed in a comparatively restricted geographic areaWhile power flows into Pella’s system to serve its load, power also flows through its system to loads connected to the MidAmerican, CIPCO, and MISO systems.6meters are based at the transmission / local distribution interface to measure flow into the local distribution systemPella’s meters are configured to measure bilateral flows and used for billing for transmission by the local balancing authority. These meters are used to validate billing for wholesale transactions among utilities and to determine energy and ancillary services with MISO.7local distribution systems will be of reduced voltageLocal distribution system operate at a reduced voltage (typically kV) compared to Pella’s elevated 69 kV transmission facilities.
23Pella’s Arguments (cont’d) FERC accepted Pella’s arguments that its 69 kV facilities should be classified as transmission facilities and noted that:The 69 kV facilities are not in close proximity to retail customers, but are used to support service to communities across a wide region.Power that enters Pella's 69 kV facilities is transported across its system to other markets and the facilities are “not primarily radial in character”Average of 30 percent of the energy flowing into Pella's interconnection points between 2007 and 2009 flowed out of Pella's facilities.Power that enters Pella's 69 kV facilities is transported across its system to other markets.Power that enters Pella's system is not consumed in a comparatively restricted geographical area.Pella’s meters are used to measure bilateral flows.Pella’s 69 kV facilities operate at a higher voltage than those facilities that Pella uses to serve retail load.
24TakeawaysThe primary functionality of the system plays a substantial role in the application of the seven-factor test:In CalPeco, power was shown to flow out of the system in several types of situations related to reliability, emergency assistance, and serving border communities—the primary function of the system, however, was determined to satisfy the seven-factor testIn MidAmerican, the Board acknowledged that the 161 kV lines do not satisfy factor 7, but ruled that the overwhelming evidence points to a distribution facility classification.In Pella, FERC reclassified MidAmerican’s 69kV lines to transmission on the basis of Pella’s demonstrating they primarily performed transmission functions
25PART 2 Examples of BPA Transmission and Distribution systems 4/11/2017PART 2Examples of BPA Transmission and Distribution systemsBPA Radial SystemBPA Radial (Open Loop)BPA LN (Radial in Character)BPA BES Network (Part of a Transfer Path)BPA BES Network or Distribution?Methodology for Consideration
26BPA Radial System D1=27 miles D2=46 miles D3=19 miles 4/11/2017BPA Radial SystemD1=27 milesD2=46 milesD3=19 milesPower flows into the 115 kV systemOutages on the radial system do not cause adjacent 230 kV 0r 115kV system voltage or thermal violations
27BPA Radial (Open Loop) D1=2 miles D2=2 miles D3=2 miles D4= 2 miles 4/11/2017BPA Radial (Open Loop)D1=2 milesD2=2 milesD3=2 milesD4= 2 milesD5=1 milesD6=16 milesD7=1 milesOpen loop configuration (Normally open switch )Power always flows into the 115 kV systemOutages on the radial system do not cause adjacent 230 kV 0r 115kV system voltage or thermal violations
28BPA LN (Radial in Character) 4/11/2017BPA LN (Radial in Character)D1=11 milesD2=15 milesClosed loop configurationPower flows into the 115 kV systemOutages on the Local Network do not cause adjacent 230 kV 0r 115kV system voltage or thermal violations
29BPA BES Network (Part of a Transfer Path) 4/11/2017BPA BES Network (Part of a Transfer Path)D1=28 milesD2=54 milesClosed loop configuration11 MW flows in and 2 MW flows out of the 115 kV systemPart of a major transfer path within the Western Interconnection
30BPA BES Network or Distribution? 4/11/2017BPA BES Network or Distribution?D1=4 milesD2=38 milesD3=4 milesD4=38 milesD5=38 milesClosed loop configuration60MW flows in and 22 MW flows out of the 115 kV systemNot Part of a major transfer path within the Western InterconnectionOutages on the Local Network do not cause adjacent 230 kV 0r 115kV system voltage or thermal violations under heavy winter base case conditionRequires further “performance based” assessment
31Methodology for Consideration 4/11/2017Methodology for ConsiderationConsistent methodology for reliability and commercial purposesCan the facilities adversely or favorably impact neighboring systems?Radial systems that do not impact neighboring systemsBPA Radial SystemsBPA Radial (Open Loop)BPA Local Network (Radial in Character)Networked system that impact neighboring systemsBPA BES Network (Part of a Transfer Path)Networked system that may or may not impact neighboring systemsUse a “performance based” assessment