Presentation on theme: "Education You Can Build On Emerson 12” Series Thermostats Homeowner Support Hotline: 800-284-2925 Education Central Engage, Apply, Retain Note: This module."— Presentation transcript:
Education You Can Build On Emerson 12” Series Thermostats Homeowner Support Hotline: Education Central Engage, Apply, Retain Note: This module covers common elements. Refer to Specification Sheet or Installation Instructions for detailed information.
Emerson 12” Thermostats Selecting the Right Thermostat for the Job Application Coverage by SystemModel Stages Heat / Cool by System ApplicationsProgramming OptionsPower Source Single Stage (SS) Multi-Stage (MS) Heat Pump (HP1 or HP2) Universal (All) Model Number Single Stage Multi-Stage Heat Pump Gas/Oil/Electric 3-Wire Zone Value Millivolt Compatible Humidity Control Program Days per Week Program Periods per Day Hardwire Battery Power Assist Universal 1F98EZ-1441 Easy Install 1/12/24/2 ✓ H,D7, Ø4, ØH 1F Humidity 1/12/24/2 ✓✓✓ H,D7, 5+1+1, Ø4, 2, ØB,H,PA 1F Commercial 1/12/24/2 ✓✓✓ 7, 5+1+1, Ø2, ØB,H,PA 1F /12/23/2 ✓✓✓ 7, 5+1+1, Ø4, 2, ØB,H Single Stage / Heat Pump 1F /1 2/1 ✓✓✓ 7, 5+1+1, Ø4, 2, ØB,H
Applications Wiring Configuration Programming Featured Products In This Module –1F98EZ Wire Universal –1F Humidity Thermostat, Universal –1F Touchscreen, Universal 12” Series Thermostats Agenda
Staging By System Type Programming Options Applications Terminal Identification Part Number Look at the Box for Detailed Information
A 4 Wire Universal Solution for High Efficiency Upgrades Without Running Additional Wires Large, Easy to Read Display Optional Humidity Control Highest Accuracy gives you the Greatest Comfort Free Homeowner Programming Hotline in English, Spanish and French Dual Fuel Capable with Smart Fuel™ Logic Program or Optional Wired Sensors 12” Series Thermostat Overview Touchscreen offers more features, delivering a new level of comfort to your customers
12” Series Specification Sheets Contain Detailed Information
12” Series Applications ApplicationStagesProgrammingFeatureType Universal 4/27, 0Easy Install 4 Wire1F98EZ /27, 5+1+1, 0Humidity1F /27, 5+1+1, 0Commercial1F /27, 5+1+1, 012" Touchscreen1F Conventional or Heat Pump with Aux 2/17, 5+1+1, 012" Touchscreen1F
12” Series Terminal Designations 12" Series Conv. Or HPUniversal TerminalDescription1F F F F F98EZ-1441 Programming7, 5+1+1, 0 7, 0 W/E Stages2/13/24/2 1 st. Stage Heat (SS1, MS2) or Aux Heat 1st stage (HP) ●● W2 2 nd Stage Heat (MS2) or Aux Heat 2nd Stage (HP) ● Y 1 st Stage Compressor (SS1, MS2 or HP1) ●● Y2 2 nd Stage Compressor (MS2 or HP2) ● GFan Relay●● RH and RC24 VAC Hot (TH) Separate●● C24 VAC Common (TR)●● O and BReversing Valve Separate● O/BReversing Valve Combined ●●● LDiagnostics● +, S, -Remote Sensor Terminals● 6Wet Heat, 3 Wire Zone Valve● Hum, Dehum(2)Humidity Terminals ●● A1Economizer ● Note: Touchscreen Single Stage Touchscreen Mutli-Stage CommercialHumidityWireless
12” Series Heat Pump / Dual Fuel Staging Detail Stage+ HP1 Heat Mode HP2 Heat Mode HP1 w/2 stage Dual Fuel Heat Mode 1 st Y1 Compressor 2 nd W/E Aux, stage 1Y2 Compressor 3 rd W2 Aux, stage 2W/E Aux, stage 1W/E 1 st Stage Gas 4 th W2 Aux, stage 2W2 2 nd Stage Gas Dual fuel option de-energizes any compressor stage when auxiliary heat is energized
Power Stealing Assist extends battery life significantly by drawing “stealing” small amounts of voltage from the heat (W) or cool (Y) circuit. Power Stealing Switches on the back of the thermostat should be left in the “ON" position for most systems. On a small number of heating or cooling systems with high impedance electronic modules you may observe one of the following conditions: –The furnace, draft inducer or fan run or continue running when the thermostat is not calling for operation. Switch the “W” dip switch to OFF. –If the condition continues to occur switch the “Y” dip switch to OFF to disable Power Stealing Assist completely and operate the thermostat on batteries only. Power Stealing Assist Extends Battery Life (1F and 1280 Only) If the Power Stealing Assist method is not compatible with your system both switches can be turned off and the thermostat will operate normally.
12” Series Wiring for Conventional Systems - AC /Furnace (No Heat Pump) * Common connection requited for the 1F98EZ, diagnostic indicator, and outdoor sensor options. Optional on others. ** For two transformer systems remove the jumper #6 Terminal is for a power closed 3 wire zone valve Single Stage (SS) in Red Multi-Stage (MS) add Orange
12” Series Wiring for Heat Pump * Common connection requited for the 1F98EZ, diagnostic indicator, and outdoor sensor options. Optional on others. ** For two transformer systems remove the jumper *** If your system does not provide an E connection, jumper W2 to W/E to use the Auxiliary Heat in the Emergency Mode Dual fuel option de- energizes when auxiliary heat is energized Single Stage Heat Pump (HP1) in Green Multi-Stage Heat Pump (HP2) add Orange
12” Series Navigation Heat/Cool/Off Fan Auto/On Configuration and Programming Touchpad's Temperature or Configuration Adjustment Buttons Actual Room Temperature Desired Temperature Time of Day or Humidity Day of Week Battery Status = Full Charge = Half Capacity = Replace Batteries
12” Series Entering System Configuration Most technical service calls are the result of improper system configuration 1. Press the Menu touchpad 2. Press and hold the Installer Config touchpad for five seconds
12” Application Specific versus Customization—Don’t Go Overboard! MENU ITEM DISPLAY (DEFAULT)OPTIONSCOMMENTS System Configuration(MS 2) SS1, MS2, HP1, HP2 Installer Set Electric Heat Fan(GAS)GAS, ELEInstaller Set 1. Choose System 2. Select Fan Function Options are great but know the difference between application, options, and confusion to the homeowner.
1F Series Configuration Example Refer To Installation Instructions For Other Models Denotes Critical to the Application Menu #PN-P Displayed (Default) Press Δ or to Select From Listed OptionsComments 111SS1HP1, SS1 Selects Single Stage or Heat Pump (1 compressor), on the 1202 and 1202H add MS2 and HP2 to choices 222(ELE)GAS GAS setting: furnace controls blower ELE setting: thermostat controls blower 333Days, (7) P5+1+1 or 0Programs per week. (0 = non-programmable) 44NAPS (4)2Program periods per day 554 Cool-Off- Heat-Auto Cool-Off-Heat, Off-Heat, Cool-Off System switch configuration in single stage 66NAE (On)OFF Selects Energy Management Recovery, E (with programming option on) 775Cr, Heat (FA)SLSelects Adjustable Anticipation, cycle rate, Heat 886Cr, Cool (FA)SLSelects Adjustable Anticipation, cycle rate, Cool 997 Cr/AU, Emer (FA) SL Selects Adjustable Anticipation, cycle rate auxiliary, (This item is only to appear if HP1 is selected above) 10 8CL (OFF)OnSelects Compressor Lockout
Menu #PN-P Displayed (Default) Press Δ or to Select From Listed OptionsComments 11 9dL (On)OFFSelects Continuous Display backlight & intensity 12 10dL (LO)HISelects Backlight Intensity , LO to 4, HISelects Adjustable Ambient Temperature Display 14 12°F°CSelects °F/°C Display (temperature units in Fahrenheit or Celsius) b (On)OFFSelects audible Beeper On/Off 16 14dS (On)OFFSelects Daylight Saving Time calculation 17 15AS, Heat (On)OFF Selects Automatic Schedule for comfort temperature Programming, heat mode 18 16AS, Cool (On)OFF Selects Automatic Schedule for comfort temperature Programming, cool mode CS, (OFF) Cool Savings Selects Cool Saving Feature & amount 1F Series Configuration Refer To Installation Instructions For Other Models
Menu #PN-P Displayed (Default) Press Δ or to Select From Listed OptionsComments HL, Heat (99) 62-98TEMPERATURE LIMIT, HEAT (max heat set point) LL, Cool (45) 46-82TEMPERATURE LIMIT, COOL (min cool set point) OFF Keypad Lockout L (total) P (partial) Selects Keypad Lockout Selects Keypad Lockout Combination (active only if keypad Lockout is selected) FS, Heat (On)OFFFast second stage of heat (not available if SS1 is selected ) 24 22FS, Cool (On)OffFast second stage of cool (not available if SS1 of HP1 is selected) Remote (OFF)OnRemote temperature sensor, enable/disable In, RemoteOutdoor RemoteRemote temperature sensor (Indoor/Outdoor) LS (On)OFF Local temp. Sensor enable/disable (only when Indoor Remote is selected On) dF (5)5-50 Selects Dual Fuel Feature & set point Cd (60)0-99 Selects Compressor delay in seconds (only when dF is selected >5) Change Filter (OFF) OnSelects Change filter feature 200 Hours Change filter, duration hours (in increments of 25 hours) 1F Series Configuration Refer To Installation Instructions For Other Models
Optional Configuration Options MENU ITEM DISPLAY DEFAULTOPTIONSCOMMENTS EMRE (On)Off Programming Mode Only Heat Cycle RateCr HEAT (ME)SL, FASS1, MS2 only Heat Pump Configuration Cycle Rate Cr Heat / A/C (ME) SL, FA Heat Pump HP1, HP2 only A/C Cycle RateCr A/C (ME)SL, FASS1, MS2 only Auxiliary Heat CycleCr AUX Heat (FA)SLHP1, HP2 only
Optional Configuration Options MENU ITEMDISPLAY DEFAULTOPTIONSCOMMENTS Compressor Lock-outCL (OFF)OnInstaller Set System Configuration(Heat, A/C, Off) Heat, Off, Fan/ Heat, Off/ A/C Off Installer Set Compressor Optimization CO (OFF)OnInstaller Set LCD Display LightdL(ON)OFF Temperature Display Adj. Hi (0)1 to 5 Hi or LO °F/°C Selection(°F)°C
Optional Configuration Options MENU ITEM DISPLAY (DEFAULT)OPTIONSCOMMENTS Dual Fuel / ElectricdF (0)1 – 9 Compressor DelayCd (60)00 – 99 O/B Output Configuration On A/C (O)On Heat (B) Application Specific Set By Installer (HP1 or HP)
1F Humidity Thermostat Configuration, Additional Menu Items Menu # SS1 MS2 HP1 HP2 Displayed (Default) Press Δ or to Select From Listed OptionsComments 38 (OFF) HdOnSelects Humidity Display alternate with time. 39 Humidity 00 (Room Humidity) -20 Lo to 20 HISelects Humidity Display adjustment. 40 (OFF) HRLO, HISelects Auto Humidity reduction. 41 (OFF) AHH, C, ASelects Automatic Humidification. 42 (OFF) CHOnSelects Cycle Humidifier. 43 OC (0)od, OFFSelects Optimum Comfort or Optimum Dehumidification or Off. 44 (OFF) Change UV Lamp OnSelects Change UV Lamp feature Days Change UV Lamp duration days. 46 (OFF) Change Pad OnSelects Change Humidifier Pad feature Hrs Change Humidifier Pad duration hours.
12” Series Reset to Factory Defaults Factory Default Reset: to completely reset the programming, clock and Configuration Menu to the Factory Default Settings, press the UP, DOWN, and SYSTEM touchpad's simultaneously. The display will go black for a few seconds, and then all segments will display momentarily. Reset settings for the application.
12” Series Program Worksheet Technical Service has never spoken to anyone who could not program the thermostat once they filled out the schedule worksheet in the manual and KEPT it. Save a call back and fill it out with the homeowner. Ensure they have the Homeowner Support Hotline:
12” Series Set Time, Year, Month and Date 1.Press MENU touchpad to enter installer menu. 2.Press Set Time once to indicate hour and AM or PM designation 3.Press and hold either the PLUS or MINUS touch pad until you reach the correct hour and A or P designation. 4.Repeat step 2 and 3 for minutes, year, month and date. 5.Press Run Schedule to complete
12” Series Automatic Daylight Saving Calculator The Real Time Clock will adjust automatically for daylight savings time, in the following manner: –Increment one hour at 2 AM on the second Sunday of March and decrement one hour at 2 AM on the first Sunday of November. The daylight saving feature can be enabled or disabled in installer configuration mode. Default is dS ON (enabled). After entering installer configuration mode, momentarily press or touch + or -key until the display indicates dS (in actual temperature digits) and on (default – in clock digits). Press the + or - keys to toggle display and operation from On to Off
12” Series Program Copy Button You may copy any daily program to another day or group of days by pressing the Copy touch pad. In 7 day programming mode when the Copy button is pressed, the other 6 days of the week will flash. 1.To copy the current program into the remaining six days, simply press the Copy button again. 2.To copy the current program to another day of the week, press Advance Day to select the day and press Copy to paste the program. In day programming mode the copy function is similar. The weekday (Mon-Fri) program can be copied to Sat and Sun (both flashing) or use Advance Day to choose Sat or Sun and press Copy to paste the program.
12” Series Configure Program Options System must be set for Heat or Cool. Press the Menu button for at least 5 seconds. 1.The display will step #1 in the configuration menu 2.Press the UP button to the appropriate configuration Menu No Select the programs per week by pressing UP/DOWN button –“0” for non-programmable –“5+1+ 1” for Mon through Fri with independent Sat. and Sun programs. –“7” for independent program days 3.Press the UP button to the next configuration Menu No Select the programs per day by pressing UP/DOWN button “2” for Morn/Eve program periods per day “4” for Morn/Day/Eve/Night program periods per day 4.Press Run
12” Series How to Set A Program 1.Press the Menu button and then press Set Schedule. Press SYSTEM button to select either "Heat" or "Cool” in the system switch area indicating the active mode being programmed. 2. The top of the display will show the day(s) being programmed. The time and set at temperature are also displayed. "Morning" will also be displayed to indicate the period. 3. Press PLUS or MINUS touch pad to change the temperature to your selected temperature for the 1st heating period (Morning). 4.Press PLUS or MINUS touchpad to adjust the start time for period. The time will change in 15 minute increments. 5.Press FAN to select Auto or Prog. 6. Press Set Schedule to advance to the next program period. 7.Repeat steps 2 through 6 until all of the program times and temperatures are set for all program periods on that day. 8.Press "Advance Day" to change to the next day and repeat steps 2 through 8. 9.Press Run Schedule To complete programming.
12” Series Automatic Scheduling This feature provides a method to program every day with the most popular time and temperature profile using one key press. For this feature to be available, the Auto schedule options (AS Cool or AS Heat) should be set on in the installer configuration. –Select the desired “Comfort Temperature” in the setpoint. When the Auto Schedule touch key is pressed, it will start flashing indicating that it is now ready to insert the displayed temperature setpoint as the “Comfort Temperature” for the selected system mode currently in (Heat/Cool). –A second press of the Auto Schedule touch key will complete the process. A 6 °F setback temperature will also be inserted for the night step. –Once complete, the touch key display Auto Schedule will disappear disabling any further operation of Auto Schedule touch key. If desired it can be enabled again in the installer configuration menu.
12” Series Entering Fan Program In the Set Schedule mode, the FAN key is used to select the fan operation during a program period. The default state of the Fan key is FAN Auto (fan runs during a call for cool but not on a call for heat). It can be changed to FAN Prog (fan runs during a program period). Each press of the FAN key will change the mode of the fan between Auto and Prog. In the Run mode, when a program period that has FAN Prog begins, the fan will turn on and stay on during the complete period. The display will show FAN On Prog. Pressing the FAN key will change FAN On Prog to On (fan running continuously) or Auto. To return to FAN On Prog, press Run Schedule.
12” Series Dual Fuel Settings This feature is applicable only in heat pump modes and an outside remote sensor is installed, the thermostat can monitor the outside temperature. –When the outside temperature falls below the selected setpoint temperature, dF, the thermostat will switch to gas heat and shut down the compressor. The eliminates the need for a fossil fuel kit. –Use the or PLUS or MINUS touchpad's to select the desired setpoint temperature in the range of 5° F to 50° F –Factory default is 5, which disables this feature. See Dual Fuel Temperature and Setpoint in Programming section. Select Compressor Delay – When dF is enabled, the shut down of the compressor(s) is delayed for a time period after the auxiliary stage is energized. This delay, Cd, is factory set at 60, but can be set in the range of 0 to 99 seconds by using the PLUS or MINUS touchpad's.
12” Series Wired Remote Sensing One remote temperature sensor can be installed indoor or outdoor and connected to the thermostat by a maximum cable length of 100 meters (300 ft). Three terminals, +, S & - are provided on the terminal block to connect to the White- Rodgers standard wired remote sensor. This sensor will be read by the thermostat only when 24 VAC is present. When used as indoor sensor, the readings can be weighted with the local sensor for specific program periods. User can enable or disable the remote sensor in the installer configuration mode and also the outdoor temperature can be selected to show on the display. In the installer configuration mode, momentarily press the PLUS or MINUS touchpad until display indicates Remote (at the top left of the LCD) and OFF (default – in clock digits). –Pressing PLUS or MINUS touchpad will toggle the operation and display from Remote OFF to Remote On. –When Remote On is selected, press the PLUS touchpad for the display to indicate Remote In (for indoor remote). The or keys will toggle the operation and display from Remote In to Outdoor Remote. When any remote is selected the temperature will display in the clock digits for one second alternating with the current time for three seconds when in Run Schedule mode. Outdoor Remote will indicate at the top left of display for outdoor remote reading. Only Remote will show at top left for indoor remote reading. (°F or °C will not indicate with remote temperature readings). Sensing Range: –Outdoor temperature range is -40 to 140°F –Indoor temperature range is 32 to 99 °F
12” Changing Humidity Settings Heat (Humidification) – Press SYSTEM key to select HEAT. –To change the humidity setting when System On appears and the heating system is running press the HUMIDITY* button once. –Press UP or DOWN to adjust the humidity level setpoint range. (Humidity setpoint can be adjusted from 5 to 50%.) Hum On will appear indicating it is calling for the humidifier. Cool (Dehumidification) –Press SYSTEM to select Cool. –To change the humidity setting when System On appears and the cooling system is running press the HUMIDITY* button once. –Press UP or DOWN to adjust the dehumidification level setpoint range. (Humidity setpoint can be adjusted from 5 to 50%.) DeHum On will appear indicating it is calling for the humidifier. –If the room humidity is lower than the adjustment range, press DOWN to 40% and hold for 4 seconds. This will force the DeHum On for one complete cooling cycle to test the dehumidification equipment. *Note: If Auto Schedule is displayed instead of Humidity, Auto Schedule must be turned off in the Configuration Menu.
12” Emergency Mode for Heat Pumps Emergency Heat (System EM Position) bypasses the Heat Pump to use the heat source wired to terminal W/E, W2 on the thermostat. EM is typically used when compressor operation is not desired, or you prefer back-up heat only. 1.Press SYSTEM key to select EM. “EM Heat Mode” will flash on the display. 2.Press UP or DOWN to adjust thermostat setting above room temperature. –The Emergency heating system will begin to operate. The display will show “System On” flashing “EM Heat Mode” and “Heat” to indicate that the Emergency system operating. 3.Adjust temperature setting to 3° above room temperature. –Any additional stages of auxiliary heat should begin to operate and the display will show "System On +2". 4.Press UP or DOWN to adjust the thermostat below room temperature. –The heating system should stop operating.