Presentation on theme: "Sources of water (RAIN)"— Presentation transcript:
1Sources of water (RAIN) Surface SourcesGround SourcesStreamsSpringsLakesInfiltration GalleriesPondsInfiltration WellsRiversWells and Tube wellsImpounded ReservoirsOceans
2Springs Natural outflow of GW @ earth’s surface. Gravity springs : GW table rises high & water overflows though the sides of a natural valley or depression.Surface springs : an impervious obstruction supporting underground storages becomes inclined causing water table to go up & get exposed to ground surface.Artesian Springs : when water flowing through some confined aquifer is under pressure.
9WellsA water well is a hole usually vertical, excavated in the earth to bring GW to the surface.Open Wells / Tube Wells.
10Open Wells (Dug Wells)Open masonry wells, 2 – 9 m dia, less than 20 m depth. Discharge 5 L/sWalls built of brick or stone masonry or precast concrete ringTo improve yield of well, 10 cm dia centre of well is made (Shallow well/Deep Wells)Shallow well rests in a pervious strata.Deep well rests on an impervious ‘mota’ layer & draws its supply from the pervious formation lying below ‘mota’ layer.A shallow well might be having more depth than a deep well
11Tube Wells Yield from std. tube well 40-45 L/s. A long pipe or tube, bored deep into the ground, intercepting one or more water bearing strata.Tube wells in Alluvial soils / Hard Rocky soils.Deep tube wells : m depth, yield 200 L/s. (50,000 No. in India)Shallow tube wells : m depth, 20 L/s yield
15Tube Wells Yield from std. tube well 40-45 L/s. A long pipe or tube, bored deep into the ground, intercepting one or more water bearing strata.Tube wells in Alluvial soils / Hard Rocky soils.Deep tube wells : m depth, yield 200 L/s. (50,000 No. in India)Shallow tube wells : m depth, 20 L/s yield
16Infiltration Galleries (Horizontal Wells) Horizontal tunnels (with holes on sides) constructed of masonry walls with roof slabs to tap GW flowing towards rivers/lake.shallow depths (3-5m) along the banks of river either axially along or across GW flow.Width (1m), depth (2m) , length (10 – 100m)If large GW quantity exists, porous drain pipes are provided and they are surrounded by gravel and broken stone.Yield, 15,000 L/day / Meter lengthA collecting shore end of gallery serves as sump from where water is pumped.
24Infiltration WellsThey are shallow wells constructed under beds of rivers.Deposits of sand exist at least 3m deep in river beds. As the water percolates down, impurities are removed. Quality of water is better than river water.They are sunk in series in the bank of the river.They are top & open & bottom. Manholes are top for inspection.They are constructed of brick basonry with open joints.Various infiltration wells are connected by porous pipes to sump called jack well.
28Intakes Structures used to withdraw water from various sources. Lake / Reservoir / River /Canal/ Intake.
29Lake Intakes Submersible intake. A pipe laid in the bed of the lake. One end is in the middle of the lake & is fitted with bell – mouth opening covered with a mesh & protected by concrete crib.Water enters in the pipe through bell-mouth opening & flows under gravity to the bank where it is collected in a sump – well & then pumped to TP.
32River IntakesA circular masonry tower (4-7m dia) constructed along bank of the river.Water enters in the lower portion of the intake (i/e sump – well) from penstocks.Penstocks are fitted with screens to prevent entry of floating solids.No. of penstock openings are provided in intake to admit different levels.Opening & closing of penstock valves is done with wheels pump – house floor.
33a) Wet Intakes Constructed inside river @ suitable place. A concrete circular shell filled with water upto water level inside the river.Water enters through openings provided on outer circular shell, as well as on inside shell.Water is taken to the bank of the river through the withdrawal conduit in the sump well from where it is pumped to WTP.
34b)Dry Intake towerIn wet intake tower, water enters first in the outer shell then it enters in the inner shell.In dry intake, water enters directly withdrawal conduit.
39Reservoir Intake An intake tower constructed on the slope of the dam. Intake pipes are different level to withdraw water at all variations of water level.All inlet pipes are connected to one vertical pipe inside the intake well.Screens are mouth of all intake pipes to prevent entry of floating matter.Water entering the vertical pipes is taken to other side of the dam by means of an outlet pipe.
40At the top of intake tower, sluice valves are provided to control flow of water. Valve tower is connected to the top of the dam by means of foot-bridge gang- way.For earthen dams, intake towers are separately constructed.For RCC masonry dams, intake tower is constructed inside the dam it self.
45Canal IntakeNo need to provide multiple ports, as water level in canal remains constant.A pipe placed in a brick masonry chamber constructed partly in the canal bank.On one side of chamber, opening is provided with coarse screen for entrance of water.A bell mouth fitted with a hemispherical fine screen is the mouth of the pipe.Outlet pipe carries water to the other side of the canal bank from where it is taken to TP.One sluice valve operated by a wheel from top of masonry chamber is provided to control flow of water in the pipe.