Presentation on theme: "Technical sheet LF1-2-3 Published : September 2012 Version : V01 Seismic version."— Presentation transcript:
Technical sheet LF1-2-3 Published : September 2012 Version : V01 Seismic version
Schneider Electric - Energy BU - Primary Lob 2 - Presentation : The major difference between LF seismic version and standard version concerns the opening and closing releases. There is an additional part called "masselotte" mounted on the standard coils. The function of this part is to bring a counterweight at the coil. If there are vibrations, metal rod of the coil does not move and keep its initial step. A seismic tests have allowed validating our LF2-LF3 in MCset cubicle (test report n°990878)
Schneider Electric - Energy BU - Primary Lob 3 -
5 - Second difference is Anti-pumping Relay ●On standard version of LF range there is an electronic anti-pumping relay KNE (see diagram). ●On seismic version there is a OLD VERSION of anti-pumping relay - electromechanical relay KN (see diagram). ●KN is confirmed for NPP application for EMC, also it allows to use closing coil circuit continuity supervision.
Schneider Electric - Energy BU - Primary Lob 6 - KNE anti-pumping relay KNE
Schneider Electric - Energy BU - Primary Lob 7 - KN anti-pumping relay KN
Your consent to our cookies if you continue to use this website.