Overall objectives Detailed analysis of the energy use in a certain equipment, activity, installation, building, campus: – Where energy is used – When energy is used – How energy is used Through an audit it is possible to: – identify/model the required energy services – Design a solution to improve the energy use and supply Equipment replacement, process change, user behaviour change
Energy Audit Phases Preparing and Planning Facility inspection Field Work Data analysis Energy audit reporting Energy Action Plan
Action Plan An action plan is a strategy plan to increase the energy efficiency of the facility – It describes the solutions – It describes the efficiency objectives – It describes the implementation plan This plan results from the energy audit
Tasks Collect data regarding energy use – Energy bills (3 or more years if available) Collect data regarding building envelope and equipment's – Location and weather data – Building description (blueprints, bill of materials, etc.) – Characteristics of the main equipment's – Functional organization Preliminary data analysis – Find any awkward result
Preliminary visit Visit together with the facility manager to see how the facility operates Collect missing data (if available) Observe the building envelope Identify “low-hanging fruit” savings
Objective Detailed analysis of the collected data – Evaluate energy consumption baseline (normalize climate data) – Prepare energy balance – Identify energy services Characterize equipment's performance
Main Equipments Heating and cooling – Hot water and steam boilers – Chillers and cooling towers – Ait treatment units – Ventilation units – Pumps and pipes – Air conditioning units – Air conditioning controllers Hot Water – Tankers Lighting – Lights – Ballasts – Controllers
Other Equipments Elevators and other mechanical transportation systems Specific equipment's of the building – Monitors in hospitals, TVs in restaurants Refrigeration equipment's in kitchens, laundries, pools Energy generation systems (solar, co-generation) The efficiency of every heat generation system should be verified
Field Work Plan With the collected data and the characterization of the facility, prepare the field work: – The list of equipments that will be measured – The list of equipments that needs to be used for measurement – The measuring procedure (one point measure, long data collection) – Interviews to be done to complete information
Main activities Measure energy consumption of main sectors/equipments – Productive systems, hot water, heating and ventilation – Identify lack of maintenance Verify electric installations Verify HVAC and lighting controllers Continuous monitoring or main consumption points of energy to obtain load diagrams – One day – One week
Complementary activities Complementary measurements to collect information – Room temperatures – Room luminance Characterize schedule of main equipments (interviews, observations) Characterize the envelope in detail and how users interact with it (interviews, observations) Characterize utilization patterns
Audit Equipment Thermometer Thermo-hygrometer Lux meter Current Clamp Network analysers Thermography
Objectives Disaggregation of energy consumption by energy services – Complete energy balance Develop load diagrams – Daily, weekly and if possible annual evolution Evaluate energy indicators, specific consumptions – Deviation form disaggregation and indicators should provide hints regarding energy efficiency measures
Activities Evaluate efficiency of the equipments and installations and estimate savings from equipment replacement, process change or behaviour change or installation of generation equipments Evaluate technical feasibility of doing equipment replacement, process change of behaviour change Due the economic evaluation of implementing such measures Determine facility energy class
Energy balance The energy balance disaggregation should be in an annual basis – Consider average consumption of the last 2/ 3 years, suing information from energy bills – Consider the information gathered in the audit Equipment's use schedule Equipment's characterization Equipment's measurements Simulation (software)
Simulation Objective is to obtain the energy consumption considering the utilization, the equipments, the envelope The model should be adjusted to the field measurements The calibrated simulation will enable: – Testing different energy efficiency measures
Energy bills Evaluate the average consumption across the year – With more than one year, the influence of weather of activity may be filtered Verify correctness of tariffs Evolution of used power – Impact of equipments or activity change
Objective Describe the energy demand of the installation and the costs Describe the equipment status Identify energy efficiency measures, the investment and its potential payback – Substitution or retrofit of equipment – Use of more efficient controllers – Installation of energy management systems – Introduction of renewable resources generation Identify upcoming changes in regulations that may impact on the current energy use
Action Plan From the different measures proposed in the energy audit, identify an implementation plan – Investment plan – Schedule Low cost measures should be the first to be implemented The return of investment period should be the indicator used to prioritize the measures in the plan This should be done closely with the energy manager and the board
Gestão de Energia Energy services Carlos A. Santos Silva Professor Associado Convidado Cátedra WS – Energia Departamento de Física email@example.com
Outlook Space Heating and Cooling – Thermal balance – Heat transfer – Internal gains – Solar gains – Climate – Comfort – Insulation Hot water Cooking Food Conservation Lighting Entertainment Work House keeping Communication
Thermal Balance (1) Applying the 1st law of thermodynamics – Balance between all the gains and losses Solar (S) Internal(I) Conduction, convection and radiation through envelope (T) Air mass balance/ventilation (V)
Thermal balance – closed system (3) 1st law of thermodynamics – Internal energy variation Mass includes air, walls, furniture, etc… – Heat Transfer through windows, walls, et… Generation and absorption – Occupants – Appliances (work consumption)
Thermal balance – open system (4) 1st law of thermodynamics – Ventilation – Air leakages (infiltrations)
Heat transfer gains Conduction Convection Radiation
Electric appliances – Computers Heat generation in power sources, processor – Lighting Radiation and convection – Occupants Radiation, convection, latent heat (water vapour) We do not consider here the heat generation from radiators, fireplaces, AC
Degree Days Simple and direct method (though incomplete) to characterize the climate of a certain region – It measures the product between the number of days and the number of degrees that the interior temperature is lower (heating) or higher (cooling) than a certain comfort temperature Heating degree days (HDD) Cooling degree days (CDD)
Comfort temperature “mind state that expresses satisfaction about the thermal environment” Human comfort depends on the ability to control the body temperature between 36 and 37 º C It depends on the balance between heat exchange – It is not only about air temperature It depends on the humidity (evaporation/transpiration) – It depends on the activity, clothes, etc…
Comfort conditions Temperature: 20 to 27 º C Relative humidity: 30 to 60%
Hot Water Water used for – Showers – Washing (dishes, clothes, house cleaning) Important Variables Litters of water Final temperature (Hot) Initial temperature (Cold) Energy
Water usage Reducing water usage reduces energy water consumption
Water Temperature The Final Temperature has two conflicting constraints – Skin scalding (5s at 60ºC) – Bacterial Contamination (e.g. Legionella) The European Guidelines for Control and Prevention of Travel Associated Legionnaires’ Disease recommend that hot water should be stored at 60 °C (140 °F) and distributed such that a temperature of at least 50 °C (122 °F) and preferably 55 °C (131 °F) is achieved within one minute at points of use The Initial Temperature – Depends on the ambient temperature
Measuring “Light” Luminous Flux – quantity of light emitted by a luminous source in all possible directions (lm) Luminous Efficacy – Ration between the luminous flux and the power of the source (lm/W) Luminous intensity – Luminous flux per unit of solid angle (cd) Illuminance – ration of luminous flux by the area of incidence (lux=lm/m2) Luminance – ration between luminous intensity emitted in a given direction and the apparent area of the luminous
Visual Comfort Visual comfort is a subjective impression related to quantity, distribution and quality of light. Visual comfort is reached when objects can be seen clearly, without tiredness and in a pleasantly colored environment – The level of illumination of the visual task; – The luminous distribution in the space (light repartition, luminance ratio and embarrassingly shading); – The sight towards outside; – The colour rendering and the colour of the light source; – The absence of glare.
Glare Visual conditions in which there is excessive contrast or an inappropriate distribution of light sources that disturbs the observer or limits the ability to distinguish details and objects (CIE) Difficulty to see in the presence of bright light (natural or artificial) – caused by a significant ratio of luminance between the task and the glare source. – Depends on the angle between the task and the glare source and eye adaptation
Power in AC (P=UI) Inductance and capacitance elements cause energy flow changes (AC) – Capacitance introduces a 90º lead between current and voltage – Inductance introduces a 90º lag between current and voltage RC RL R C L
Definition Process to quantify the savings associated with the implementation of energy efficiency measures – Measures energy, not the cost – It is necessary to evaluate economic savings – It is based in the application of a methodology International Performance Measurement and Verification Protocol (IPMVP) ASHRAE Guideline 14:Measurement of Energy and Demand Savings eeMeasure
Energy Conservation Measure (ECM) An activity or set of activities designed to increase the energy efficiency of a facility, system or piece of equipment. – ECMs may also conserve energy without changing efficiency. Several ECM's may be carried out in a facility at one time, each with a different thrust. An ECM may involve one or more of: – physical changes to facility equipment, – revisions to operating and maintenance procedures, – software changes, – or new means of training or managing users of the space or operations and maintenance staff. An ECM may be applied as a retrofit to an existing system or facility, or as a modification to a design before construction of a new system or facility.
Savings The reduction in energy use or cost. – Physical savings may be expressed as avoided energy use or normalized savings – Monetary savings may be expressed analogously as “cost avoidance” or “normalized cost savings” Savings, as used in IPMVP, are not the simple difference between baseline and reporting period utility bills or metered quantities.
Normalized Savings The reduction in energy use or cost that occurred in the reporting period, relative to what would have occurred if the facility had been equipped and operated as it was in the baseline period but under a normal set of conditions. These normal conditions may be a long term average, or those of any other chosen period of time, other than the reporting period. Normal conditions may also be set as those prevailing during the baseline period, especially if they were used as the basis for predicting savings. If conditions are those of the reporting period, the term avoided energy use or just savings, is used instead of normalized savings.
Estimate A process of determining a parameter used in a savings calculation through methods other than measuring it in the baseline and reporting periods. These methods may range from: – arbitrary assumptions – engineering estimates derived from manufacturer’s rating of equipment performance. – Equipment performance tests that are not made in the place where they are used during the reporting period are estimates, for purposes of adherence with IPMVP.
Baseline Period The period of time chosen to represent operation of the facility or system before implementation of an ECM. This period may be as short as the time required for an instantaneous measurement of a constant quantity, or long enough to reflect one full operating cycle of a system or facility with variable operations. – Baseline Energy: The energy use occurring during the baseline period without adjustments – Adjusted-baseline energy: The energy use of the baseline period, adjusted to a different set of operating conditions.
Reporting Period The period of time following implementation of an ECM when savings reports adhere to IPMVP. This period may be : – as short as the time for an instantaneous measurement of a constant quantity; – long enough to reflect all normal operating modes of a system or facility with variable operations; – the length of the financial payback period for an investment; – the duration of a performance measurement period under an energy performance contract; – or indefinite.
Adjustments Routine Adjustments: The calculations shown in the M&V Plan to account for changes in selected independent variables within the measurement boundary since the baseline period. – Independent Variable: A parameter that is expected to change regularly and have a measurable impact on the energy use of a system or facility. Non-Routine Adjustments: The individually engineered calculations to account for changes in static factors within the measurement boundary since the baseline period. – When non-routine adjustments are applied to the baseline energy they are sometimes called just “baseline adjustments” Baseline Adjustments: The non-routine adjustments arising during the reporting period from changes in any energy governing characteristic of the facility within the measurement boundary, except the named independent variables used for routine adjustments.
Measurement Boundary A notional boundary drawn around equipment and/or systems to segregate those which are relevant to savings determination from those which are not. All energy uses of equipment or systems within the measurement boundary must be measured or estimated, whether the energy uses are within the boundary or not
Savings Savings = Baseline-Period Use / Demand – Reporting-Period Use / Demand ± Routine Adjustments ± Non-Routine Adjustments
M&V Design Define a M&V plan (duration, accuracy) according to the available budget and needs Gather relevant energy and operating data from the baseline period and record them in away that can be accessed in the future After the ECM is installed, ensure it has the potential to perform and achieve savings by conducting operational verification Compute and report savings