Download presentation

Presentation is loading. Please wait.

Published byRaven Yeo Modified over 2 years ago

1
From an Oil Field Waste Stream - Electrical Power 3 rd B.C. Unconventional Gas Technical Forum Lyle A. Johnson, PE, RMOTC, U.S. DOE

2
2 RMOTC Location 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C.

3
3 Geothermal Potential 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C. 17-WX-21 Madison and Tensleep Possibly 35 MBWPD flowing 57-WX-3 Madison and Tensleep Possibly 10 MBWPD flowing TENSLEEP PRODUCING AREA OTHER POSSIBLE TENSLEEP SOURCE WELLS AND DEEPENING CANDIDATES Precambrian granitic basement structure

4
4 Water Treatment Pond 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

5
5 Water Treatment Ponds 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

6
6 Project Goals 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C The project is to validate the use of a binary geothermal power generation system that uses hot produced oilfield water to produce electricity. Test the system for a minimum of 1 year Provide a technical and economic analysis of the process Testing partner: ORMAT Nevada, Inc.

7
7 Projected Generator Performance Flow Rate:40,000 bpd (6,358 m 3 /d) Inlet Temperature: 170 ° F (77 °C) Outlet Temperature: 152 ° F (67 °C) Ambient Temperature: 50 ° F (10 °C) Generator Gross Power:180 kW Net Power Output:132 kW 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C Unit designed and built by Ormat Systems Ltd, Yavne, Israel.

8
Barrel Tank Moving 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

9
Barrel Tank Moving 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

10
10 Setting of Vaporizer 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

11
11 Setting of 2 nd Condenser 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

12
12 Cooling Fan Motor 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

13
13 Cooling Fans 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

14
14 Working Fluid Piping 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

15
15 Return Vapor Piping 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

16
16 Completed Unit 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

17
17 Operational Trends 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

18
18 Daily Power Fluctuation 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

19
19 Daily Ambient Temperature 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

20
20 Operational Summary On Line Total, Total (Actual)days161 (151) Inlet Brine Temperature°F °C Inlet Brine Volume Barrels3,047,370 m 3 484,493 Net Power Producedkilowatt hour586,574 Overall On line percentage%91 Average net powerkilowatt159 Overall w/o Field Downtime On line percentage%97 Average net powerkilowatt171 Avg. Net Power Jan-Feb 2009kilowatt200 3 rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

21
21 Future Plans Perform equipment checkout, maintenance and repair, to include: Change system control to a source control loop with an additional control valve, and Install vapor bypass line around turbine to ease unit starting, and Install a vibration monitoring system, and Heat trace all oil lines to prevent oil thickening. Continue testing of the unit until at lease September rd B.C. Unconventional Gas Technical Forum, Victoria, B.C

Similar presentations

© 2017 SlidePlayer.com Inc.

All rights reserved.

Ads by Google