Download presentation

Presentation is loading. Please wait.

Published byHallie Ha Modified over 3 years ago

1
PV System Design and Installation LO 8 – PV Electrical Design

2
Electrical Design (8% of test questions) Task/Skill 8.1. Determine series/parallel PV array arrangement based on module and inverter specifications 8.2. Select BOS components appropriate for specific system requirements 8.3. Determine voltage drop between major components

3
Step 1 Determine inverter “constraints” a) Maximum DC Input Voltage b) MPPT Range PV Array String Sizing

4
Step 2 a) For maximum number of modules in a string use the “Coldest Record Temperature” b) For minimum number of modules in a string need Average Monthly High Temperature plus 30 degree F Avg High Tempurature Record Low Tempurature Determine OperatingTemperature Conditions

5
Temperature conversion formulas Tc = (5/9)*(Tf-32) Tf = (9/5)*Tc+32 Tc = temperature in degrees Celsius Tf = temperature in degrees Fahrenheit

6
Step 3 Apply NEC Voltage Temperature Correction Factor to Open Circuit Voltage (Voc) of PV Module PV module string size must not exceed maximum DC input voltage (usually 500V or 600V). In Albany, Record Low Temp = -22 F, therefore must use a temperature correction factor of 1.25 Vmax string = Voc x Temp x Modules in String Correction Factor Reference Class Book by Dunlop Determine Maximum String Size

7
Step 4 Determine Minimum String Size Apply Manufacturer’s Temp Correction Factor to Maximum Power Point Voltage (Vmp) Make sure that Vmp (temp corrected) stays within MPPT tracking range of inverter. For example, temperature correction factor for SunPower Modules is -0.1368 V Vmin = Vmp + (High Temp – 25 C) x Modules in String Where, High Temp = Average High Temperature + 17 C Reference Class Book by Dunlop Determine Minimum String Size

8
Step 5 Power = Series String Voltage (Vmp) x Parallel String Current (Imp) Where, Parallel String Current = Number of Strings in Parallel Determine Number of Strings necessary to achieve PV array capacity requirements (kW)

9
Choose inverter In general, PV array DC input (watts) can be up to 1.2 x Inverter AC output (watts) rating in Upstate New York Max Number < I max DC input of inverter of strings I max string current For example, using SunPower SPRm 5000 inverter, using 230W module (Imp = 5.61 amps) Max Number < 21 amps = 3.74 strings of string 5.61 amps PV Array Size Maximum (3 strings x 8 modules) = 24 x 230W = 5.52 kW

10
On-line inverter configuration tools

11
Wire Sizes Look at wire layout board in HVCC lab

12
Voltage Drop (volts) = Current (amps) X Resistance (ohms) V = I x R % Voltage Drop = 0.2 x D x I x R V D= One-way distance in feet I= Current (use Imp for solar circuits) R= Resistance of conductor (Ohms/1,000 feet). From NEC Chapter 9, Table 8 V= Voltage (use Vmp x the # of modules) Voltage Drop Calculations Typically design for less than 1 % voltage drop NEC Requirements Maximum from Service to the Load of 5% Maximum from final overcurrent protection device to the load of 3%

Similar presentations

OK

Lesson Measuring and Calculating Electricity. Interest Approach § Have you or your parents ever been using several appliances in the kitchen and had a.

Lesson Measuring and Calculating Electricity. Interest Approach § Have you or your parents ever been using several appliances in the kitchen and had a.

© 2018 SlidePlayer.com Inc.

All rights reserved.

To ensure the functioning of the site, we use **cookies**. We share information about your activities on the site with our partners and Google partners: social networks and companies engaged in advertising and web analytics. For more information, see the Privacy Policy and Google Privacy & Terms.
Your consent to our cookies if you continue to use this website.

Ads by Google

Ppt on 60 years of indian parliament fight Ppt on college website Ppt on climate of rajasthan Ppt on formal education system Ppt on online shopping project Ppt on pf and esic Ppt on artificial intelligence and robotics Ppt on festivals of france Ppt on digital media broadcasting company Ppt on us time zones