5 CONTROLS New codes for electrical board and panel CMSPCM KCMS/PCM CMS KCMSKPCM
6 New electronic board KCMS CMS OLDmarioSCR ECO digital input don’t change, SIC EIR change their positionNew digital input DI5 (not available for Frend and Idrowall) for new function:OCCUPANCY function (NC) only for KICM panel, (by modifying board parameters (P45=8;P93=3) trough installer password on the KPCM control panel)
7 New electronic board KCMS CMS OLDOLDNEWNew digital output CCH CCA
9 FUNCTIONS SETTING FUNCTIONS Full auto Cool Dry KICM Fan KPCM Heat KTCM Heat + heaterFull Auto + heaterNOVELTYFull AUTO: the desired temperature is showed on the display. The unit, according to the room temperature and the setting temperature, sets the working mode (cool/heat).User set temperatureLegendmoderoom temperatureHEATOFFCOOLP02=2°CP03=2°CP04=0,5°C
10 FUNCTIONS ATTENTION COMFORT FUNCTIONS KICM KPCM KTCM Orienting/swing (on Idrowall)ClockTimerSleepHot startToo coolMemoryEconomy (ECO)Lock function / Blocco remoto (KICM)ON/OFF remote control (SCR)Summer/Winter remote control (EIR)Security control (SIC)Occupancy (only KICM) newProbe IN/OUTContinuous ventilationAlarmMASTER/SLAVEPeriodic ventilationConfort control newBlocco tastiera (solo KTCM)KICMKPCMKTCMATTENTIONThe following functions aren’t available with KICM control panel:Orienting/swing - Clock - Timer - Continuous ventilation (by key) – Keybord stopProbe IN/OUT function is available for:KICM trough DIP SWITCH (DIP6) settingKPCM trough key on the panelNot used with the remote control KTCM (the probe is always set in the unit)The periodic ventilation is always disabled with KPCM and KICM with Probe In function activated (probe into the unit)Confort control (by modifying board parameters P36=1 trough installer password on the KPCM control panel).
11 COMFORT CONTROL FUNCTION Comfort control (by parameters)When the set-point is decided by a system manager (supervision), the Comfort Control function gives the possibility to increase or reduce the Set-point (+-3°C) in the room with the UP-DOWN bottoms.(The function have to be enable modifying board parameters P36=1 trough installer password on the KPCM control panel.)The set value is 22 °CUser set temperature22°CLegendmoderoom temperatureHEATOFFCOOLP02=2°CP03=2°CP04=0,5°C
12 LOCK FUNCTION FUNCTION Attention: to obtain the changing set-point ±3°C must be set the Confort Control Function
13 DIP-SWITCHESChanges to the DIP-Switches must be made with the board disconnected from the power supply.The DIP-Switches on the electronic board (see right figure) can be changed using a sharp tool. The DIP-Switches can be changed correctly by following the instructions present on the component and in the following table.OLDNEW
14 DIGITAL INPUT/FUNCTION: OCCUPANCY (NOT FOR IDROWALL FREND* ) ONLY x KICMIn case of supervising system (BMS) with OCCUPANCY function it is possible to activate 3 different working modes (by modifying board parameters P45=8; P93=3 trough installer password (60) on the panel):Not booked room = OFFOccupied room = Comfort modeBooked and not occupied room = Stand-by/Economy modeNot occupied OFFOccupied Comfort modeThere is a person in the room. The fancoil works with desired temperature value for fixed time (15 min).Set-point = desired temperature valueThe occupancy status can be activated:By one of the keys in the panel (not ON/OFF) for a set period of time (parameter P94=15 min). At the end of the time periods (15 min) the occupancy status can be enabled againWith movement sensor on DI5 digital inputPressing Sleep key for 5 sec the Occupancy function continues up to unit switch-offBooked and not occupied Stand-by/Economy modeThere is no person in the room. The fancoil works with economy set-point for energy savingsSet-point = economy* Only with ECO (DI4, parameter P44=8)NOTA BENE Con funzione Occupancy abilitata non utilizzare l’ingresso igitale ECONOMY
15 DIGITAL OUTPUT: FUNCTION CCHChiller input, chilled water required from the thermostat (NO)CCH –Chiller input
16 DIGITAL OUTPUT: FUNCTION CCABoiler input, hot water required from the thermostat (NO)CCA – Boiler input
Your consent to our cookies if you continue to use this website.