We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byPierce Speakman
Modified over 2 years ago
©Consultnet Limited Safe Use of Cylinder Gases
©Consultnet Limited Presentation Contents Introduction to Gas Cylinder Safety Main causes of Accidents Main Hazards Rules for Safe Working with Gas Cylinders Gas Regulators Flashback Arrestors Hoses, Piping, Blow Pipes and Torches Acetylene –unique properties Handling Gas Cylinders Transporting Gas Cylinders Safe Storage Cylinder Incident Response Gas Cylinders Hazards in Your Workplace Conclusions
©Consultnet Limited Introduction Compressed gases used in a variety of industrial and laboratory situations Compressed gases present a unique hazard. Depending on the particular gas, there is a potential for simultaneous exposure to both mechanical and chemical hazards Gases can be: –Flammable or combustible –Explosive –Corrosive –Poisonous/toxic –Inert –Cryogenic –Pyrophoric(burns on contact with air) –or a combination of hazards
©Consultnet Limited Introduction Introduction Common Industrial Gases Oxidants support combustion e.g. air & oxygen Inerts do not generally react with other materials, asphyxiants(leak displace air) e.g. nitrogen, argon, helium Flammables when mixed with oxidant and ignition source will burn e.g. acetylene, hydrogen, propane Toxics toxic in small concentrations e.g. ammonia, chlorine, carbon dioxide Corrosives react with materials causing reactions e.g. chlorine, sulfur dioxide Pyrophorics ignite spontaneously in air e.g. silane, phosphine
©Consultnet Limited Main Causes of Accidents Inadequate training and supervision Poor installation Poor maintenance Faulty equipment and/or design(e.g badly fitting valves or regulators) Poor handling Poor storage Inadequately ventilated working conditions
©Consultnet Limited Main Hazards Impact from the blast of a gas cylinder explosion or rapid relase of compressed gas Impact from parts of gas cylinders that fail or any flying debris Contact with the released gas or fluid(such as chlorine) Fire resulting from the escape of flammable gas or fluids such as LPG Impact from falling cylinder
©Consultnet Limited Safe Working with Gas Cylinders: Identification and Properties Read the label to see what gas you are dealing with and double check tha the cylinder/gas is right for th eintended use No compressed gas cylinder should be accepted for use that does not legibly identify its contents by name If the labeling on a cylinder becomes unclear or an attached tag is defaced to the point the contents cannot be identified, the cylinder should be marked "contents unknown" and returned directly to the manufacturer Never rely on the color of the cylinder for identification. Color coding is not reliable because cylinder colors may vary with the supplier. Additionally, labels on caps have little value because caps are interchangeable If there is a mismatch between the color of a cylinder and the label. Do not use, contact the supplier immediately Know the properties of the gas (read Material Safety Data Sheets available from your Supervisor) The cylinders contents should be identified at all times as well as the cylinder status (full, empty or in service)
©Consultnet Limited Safe Working with Gas Cylinders Safe Working with Gas Cylinders Work Practices Securely restrain cylinders to prevent them falling over Close the cylinder valve and replace dust caps when cylinder not in use Before connecting a gas cylinder to equipment or pipework make sure regulator and pipework are suitable for the gas and pressure being used Never drop a gas cylinder Never tamper with cylinders or subject them to abnormal mechanical shocks which could damage the valve or safety device Never re-paint, change markings or identification or interfere with threads Never disguise damage to a cylinder or valve. Label as faulty and contact the supplier Never attempt to repair a cylinder Never scrap a cylinder Never subject cylinders to abnormally high or low temperatures Never mix gases in a cylinder Never try refill a cylinder Never transport by rolling them on the ground or use them as rollers or supports Never pick them up by magnetic lifting Never subject to abnormal mechanical shocks whuch could damage the valve or safety device
©Consultnet Limited Safe Working with Gas Cylinders Safe Working with Gas Cylinders Daily Inspection Cylinders should be inspected daily and prior to each use for corrosion, leaks, cracks, etc. Inspection should include the cylinder, piping, safety relief devices, valves, protection caps and stems. Leaking regulators, cylinder valves or other equipment should be taken out of service.
©Consultnet Limited Safe Working with Gas Cylinders Maintenance of cylinders and their valves or relief devices shall be performed only by trained personnel. An emergency response plan shall be developed and implemented wherever compressed gas cylinders are used, handled or stored. Never smoke around compressed gas cylinders. Valve protection caps must remain in place at all times except when cylinders are secured and connected to dispensing equipment Only wrenches or tools provided by the cylinder supplier should be used to open or close a valve. At no time should pliers be used to open a cylinder valve. Never apply PTFE tape, jointing compounds or any other sealing material to the valve in an attempt to achieve a tight seal, if a gas tight seal cannot be achieved metal to metal, replace the regulator or change the cylinder
©Consultnet Limited After the regulator is attached, the cylinder valve should be opened just enough to indicate pressure on the regulator gauge (no more than one full turn) and all the connections checked with a soap solution for leaks. Never use oil or grease on the regulator of a cylinder valve. Before a regulator is removed from a cylinder, the cylinder valve shall be closed and the regulator relieved of gas pressure.The valve cap shall be replaced, the cylinder clearly marked as "empty," and returned to a storage area for pickup by the supplier Regulators, gauges, hoses and other apparatus shall not be used on gas cylinders having different chemical properties Valve outlet thread size is different for different products but the same products from different gas suppliers will have the same thread Gas Cylinder Use
©Consultnet Limited Gas Cylinder Regulators A regulator is a device that receives gas at a high pressure and reduces it to a much lower working pressure Precision instruments and MUST be handled with care to avoid damage to their sensitive springs, diaphragms, valve seals etc. Equipment should display the relevant European/British Standard number and the pressures up to which it can operate Leave the pressure adjustment knob/screw fully out when the regulator is not in use (this ensures a minimum of tension on the springs and diaphragms) Cylinders should be placed with the valve accessible at all times. The main cylinder valve should be closed as soon as it is no longer necessary that it be open, it should never be left open when the equipment is unattended or not operating This is necessary not only for safety when the cylinder is under pressure, but also to prevent the corrosion and contamination resulting from diffusion of air and moisture into the cylinder after it has been emptied.
©Consultnet Limited Flashback Arrestors Flashback is the result of mixture of fuel gas and oxygen burning within the hose, flame travels and burns its way towards the gas source at great speed, can result in force of explosion in either cylinder Flashback arrestors must be fitted on both oxygen and fuel gas regulators If flashback arrestor is dropped/damaged replace immediately Flashback arrestors should oinly be used with the gas they are labelled for and the presuure thay are designed for Coomon reasons for flashback: incorrect purging of hose/torch prior to use, incorrect gas pressure, incorrect nozzle, damaged torch valves, gas passages blocked within the torch, kinked or trapped hose
©Consultnet Limited Hoses Correct hose bore size, pressure rating, length and color coding are essential for safety BS EN 559 Blue – oxygen, Red - acetylene and other fuel gases(except LPG) Black – inert and non combustible gases Orange – Liquified Petroleum Gas Never use hoses that are longer than necessary Never use equipment while hoses are wrapped around the cylinders or trolley Length of hose should be suitable for the task Keep hoses in good condition Examine the hose for cracks, deterioration, damage and test the hose for leaks before use Do not repair hoses unless you have the skill and means to test hem in accordance with BS En 1256 Purge hose thoroughly before lighting torch Do not put wrapping tape around hosing as this contains combustible hydrocarbons Do not use copper piping with acetylene hoses as it is potentially explosive Protect hosing from heat, oil, grease or mechanical damage
©Consultnet Limited Piping Distribution lines and their outlets should be clearly labeled as to the type of gas contained Piping systems should be inspected for leaks on a regular basis Special attention should be given to fittings as well as possible cracks that may have developed
©Consultnet Limited Blow Pipes and Torches Leaks are a serious hazard as they are closest to the operator Always check condition before use, ensure tip is free of obstruction Signs of heat damage around the blow pipe or torch may indicate the equipemnt has sufferd interal damage and is leaking and should be replaced immeidately No sign of sideways movement of the cutting leaver as this could cause gas leaks within the body of the torch that are difficult to detect Always fit the correct size nozzle for the job( hole size and pressure set at regulator determine gas flow and gas velocity exiting the nozzle, manufacturer gives a pressure rating for the nozzle being use, if the gas exit velocity is slower than the combustion velocity backfire and flashback may occur Replace blow pipe or torch if Broken bent or loose gas control valve Bent mixer, misshapen cutter head Bent cutter tube Broken of bent cutting oxygen lever Leak test all connections and valves prior to use If replacing O ring seals always use the correct materials
©Consultnet Limited Acetylene Acetylene Unique properties Acetylene gas under excess pressure becomes unstable Cylinders should never be subject to intense heat or physical impact as the rise in temperature and pressure may cause the acetylene to thermally decompose Prior to moving a cylinder that has been subject to heat or severe impact contact trained emergency personnel who can check for temperature rise and apply correct procedures The cylinder may appear normal but if it is moved it may detonate with fatal consequences
©Consultnet Limited Handling Gas Cylinders Wear PPE: gloves, protective footwear, eye protection Correct way to move cylinders is to: keep upright, secure and with valves uppermost Use mechanical aids such as a trolley where reasonably practicable( do a risk assessment) Use suitable cradles, slings, clamps or other effective means when lifting with a hoist or crane For short distances on even ground the practice of milk-churning (manually moving cylindres) can be used only by trained personnel and never for longer distances, in uneven ground, wet or icy conditions, poor lighting, or at speed a trolley should be used All personnel involved should have completed manual handling training Never roll cylinders along the ground Never transport cylinder with valve and pressure regulator attached or with the valve open Never attempt to catch a falling cylinder just get out of the way Never lift a cylinder by its cap, valve or guard/shroud Remember that a cylinder is never empty
©Consultnet Limited Transporting Cylinders Transporting Cylinders Carriage of Dangerous Goods Regulations apply If possible carry in open vehicles or trailers If they must be carried in closed vans/cars ensure good ventilation at all times If the load compartment is not separated from the driver do not carry toxic gas cylinders (those with a toxic gas label and having yellow as a colour on the cylinder) Secure cylinders properly so they cannot move or fall in transit or do not project beyond the edges of the vehicle, normally in the upright position unless instructions for transport state otherwise Ensure gas cylinders are clearly labelled to show contents and associated hazards Fit suitable protective valve caps and covers to cylinders
©Consultnet Limited Transporting Cylinders Transporting Cylinders Carriage of Dangerous Goods Regulations apply Disconnect hoses and regulators from cylinders Carry propane cylinders upright and do not carry flammable gas cylinders in the same compartment as toxic gas cylinders Do not smoke while carrying cylinders inside vans/cars Unload the cylinders as soon as possible and move to a well ventilated storage area If you suspect it is leaking, park the vehicle, investigate the fault and contact the supplier If you are involved in an accident advise, any emergency services involved what gas cylinders are being carried
©Consultnet Limited Safe Storage Safe Storage Each Storage area should be subject to unique risk assessment It is best to store gas cylinders in the open and on concrete in a fenced compound with some weather protection In storage areas oxygen cylinders must be stored at least 3 metres away/separated by a fire wall from fuel gases such as acetylene, propane, methane etc. Full cylinders should be stored separately from empties and empty oxygen cylinders should be segregated from empty fuel gas cylinders Other products should not be stored in the gas storage areas especially not oil or corrosive liquids, sources of ignition or flammable materials Ease of access into and around storage area, such as provision of aisle >0.6m to prevent domino effect LPG cylinders have special requirements including storage 3m away from other gases Pyrophoric and toxic gases should be stored seperately in locked, suitable ventilated storage areas with restricted access Protect gas cylinders from external heat sources which may adversely affect their mechanical integrity Cylinders should be secured and properly restrained, secure with straps or chains connected to a wall bracket or other fixed surface, or by use of a cylinder stand Cylinders should be clearly labelled to show contents and associated hazards
©Consultnet Limited Safe Storage Store all cylinders upright and secure on a level surface to prevent them from falling Acetylene and propane must never be stacked horizontally either in storage or in use Storage arrangements should ensure turnaround of stock in adequate time Storage areas with gas cylinders must have more than one exit Cylinders should be located away from any heat/source of ignition and if possible away from the fire exits, elevators, walkways, building egresses, unprotected platform edges, or in locations where heavy moving objects may strike or fall on them Storage arrangements should be clearly described in the emergency plan Storage area must have good housekeeping and adequate warning signs with fire fighting equipment as necessary
©Consultnet Limited Cylinder Incident Response Report any damaged/leaking cylinder to supplier If a cylinder is leaking but the leak has not ignited and it is safe to do so having considered the gases specific properties: Eliminate all sources of ignition Ensure the valve is closed but do not over-tighten it Put the cylinder in a safe place that is well-ventilated – keep it upright Mark the cylinder as faulty and not to be used Warn everyone in the area of the gas leak Inform the supplier Ensure the work area is thoroughly ventilated before continuing with any work If a hydrogen cylinder is involved be aware that hydrogen burns with an invisible flame so seek expert assistance
©Consultnet Limited Cylinder Incident Response Report any damaged/leaking cylinder to supplier If a cylinder is leaking and it has ignited it could explode Call the emergency services and evacuate the area to a minimum distance of 100 metres Where a cylinder has been damaged If it has been dropped or physically damaged check it for leakage and deal with as for a leaking cylinder For handling acetylene cylinders should not be moved unless it is clearly established that there is no thermal disassociation Clearly mark any cylinder that has been exposed to excessive heat or physical impact and contact the supplier
©Consultnet Limited Cylinder Incident Response Cylinder Incident Response If a flashback has occurred: Close both blowpipe valves oxygen first Close both cylinder valves Check the temperature of the acetylene cylinder for thermal decomposition Check the blowpipe has not overheated Check the nozzle is not damaged Open both blowpipe valves oxygen first to vent the system Unwind the pressure adjustment screw on each pressure regulator Before starting up again, check the integrity of the whole system
©Consultnet Limited Cylinder Incident Response Gas Cylinders on Fire Depends on the gas, whether the gas is alight at the cylinder valve or if the cylinder has been subject to severe pressure as a result of the heat from the fire. Nature of hazard will determine procedure to be applied If cylinder has been involved in fire do not approach, evacuate the area to 100m minimium to 300m Call fire brigade Use large quantities of water to cool the cylinders if safe to do so (do not aim high pressure water direct at the cylinders) from a safe location and await the arrival of trained emergency personnel ( Emergency plan training should address ) Remove any cylinders not involved in fire to safe place, ensure valves are closed if safe to do so Inform gas supplier, If cylinder contents are unknown, treat as acetylene
©Consultnet Limited Look Out for Gas Cylinders: In Your Workplace Look Out for Gas Cylinders: In horizontol position/on the ground In contact with electrical cords Not protected from falling – chain not secure Damaged In an area where could be subject to impact such as near operating forklift Stored near combustibles Oxygen and acetylene stored together Without valve caps Deal with these Hazards IMMEDIATELY
©Consultnet Limited Conclusions Compressed gases present a unique hazard. Depending on the particular gas, there is a potential for simultaneous exposure to both mechanical and chemical hazards Inadequate training and supervision, poor installation, poor maintenance, faulty equipment and/or design(e.g badly fitting valves or regulators), poor handling, poor storage, inadequately ventilated working conditions When working with compressed gases you need to know the properties of the gas, safe use procedures and what to do when things go wrong For detailed use of individual gases you should now review the relevant Material Safety data Sheet (MSDS) for each gas used on your site Always Treat Gas Cylinders with Respect For additional information which could be used as presentation handouts visit UK HSE information on Gas Safety for a whole series of leaflets on the topicGas Safety
©Consultnet Limited Presented by: Wajeeha Kiran 2008-chem-51 Ambreen Akram 2008-chem-17 Sana Arif 2008-chem-47 Aiman Fatima 2008-chem43 Safe Use of Cylinder.
East Carolina University Compressed Gas Safety Training Program Presented by the Office of Environmental Health and Safety.
Copyright Progressive Business Publications Blue Ridge Safety Association Safety Presentations Compressed Gasses.
Compressed Gas Cylinder Safety. Industrial, manufacturing, repair shops, fabrication shops and construction operations require the use of compressed gases.
Compressed Gas Cylinder Safety Environmental Health & Safety Chemical Safety Division University of Texas Health Science Center at San Antonio.
Compressed Gases. © Business & Legal Reports, Inc Session Objectives You will be able to: Identify compressed gases by the labels Safely transport,
OXYFUEL WELDING. INTRODUCTION Oxyfuel welding is a welding process where the heat for fusion is supplied by a torch using oxygen and a fuel gas. Several.
Tulane University - Office of Environmental Health & Safety (OEHS) COMPRESSED GAS CYLINDERS FOR EMPLOYEES WHO HANDLE, TRANSPORT, STORE OR USE COMPRESSED.
COMPRESSED GASES. Compressed Gases Chemicals include oxygen, argon, nitrogen, helium, acetylene, hydrogen, nitrous oxide, carbon dioxide, ammonia, chlorine,
Compressed Gases. Stories of Compressed Gases Employee killed when cylinder turned into a rocket because its valve was knocked off Employee suffocated.
Copyright Business & Legal Reports, Inc. BLRs Safety Training Presentations Compressed Gases.
General Rules Compressed gases and cylinders must be properly stored, transported and used to prevent injury and accidents. Compressed gases and cylinders.
Oxy/fuel gas welding and cutting equipment. Safety Presentation.
Compressed Gases WAC Part K 2 Stories of Compressed Gases Employee killed when cylinder turned into a rocket because its valve was knocked off.
Copyright © 2010 Delmar, Cengage Learning. ALL RIGHTS RESERVED. Unit 23 Using Gas Welding Equipment.
Using Gas Welding Equipment Ag I Ag Mechanics Unit 2.
Compressed Gas Cylinder Safety Oklahoma State University.
1 Risk Management Department Compressed Gas Safety April, 2008.
Compressed Gases. Compressed gas description Definition of a compressed gas – any gas, or mixture of gases, that is pressurized and contained in a cylinder.
1926 Subpart J Establishes the requirements for welding and cutting in the construction industry Establishes requirements for equipment, fire protection,
Oklahoma State University Many industrial and laboratory operations require the use of compressed gases for a variety of different operations. Return.
Occupational Health and Safety Program Compressed Gas Cylinder Safety.
PROCEDURE FOR USE OF OXY-ACETYLENE EQUIPMENT (Revision 2 – 20th January 2011) Toolbox Talk.
Ag Metals I Using Gas Welding Equipment. Objectives Identify major part of oxyacteylene welding equipment Change oxygen and acetylene cylinders Turn on.
The University of Tennessee Office of Environmental Health & Safety 1 Compressed Gas:
1/05 Welding, Cutting, and Brazing. 2 Notice This presentation is provided to all Educational Service District 101 (ESD 101) schools at no cost. This.
Tulane University - Office of Environmental Health & Safety (OEHS) GAS CYLINDERS FOR TULANE LABORATORY OR FACILITY EMPLOYEES WHO USE OR WORK AROUND GAS.
OXY-ACETYLENE TORCHES Protect your head and eyes by wearing proper welding goggles or face shields equipped with a minimum shade 5 lens. Protect your.
Compressed Gas Safety for Laboratories Stanford University Environmental Health & Safety Occupational Health & Safety Program, ,
FIRE PREVENTION. Fire Of the many hazards on site or at work, fires are the worst kind. They do a great deal of damage every year. All fires, however.
1 Welding Module 10. 2Objectives After this module you should be able to – identify the most common welding hazards – take the necessary steps to avoid.
Welding and Cutting for construction. Welding safety program guidelines Person responsible Accountability and enforcement Job hazard assessment Special.
Compressed Cylinder Safety NCMAQB Subject to damage from other activities in the vicinity Cylinder laying in a horizontal position. Electrical cord in.
Safety talk about compressed gases 02/05/2013 Source: EHS (512) Airgas (866) (training = OH204) 1.
Unit: Oxy-Acetylene; Welding, Brazing, Cutting & Heating Lesson: Oxy-Acetylene General Safety Rules.
Many industrial and laboratory operations require the use of compressed gases for a variety of different operations. INTRODUCTION.
Welding, Cutting, and Brazing. Welding safety program guidelines v Determine who is accountable for enforcement of welding operations v Hot work permitting.
Oxyacetylene torches Harkness career center. Complete torch assembly.
Standard 29 CFR Part Welding, Cutting and Brazing Training.
Shop safety (General). Safety comes first! l Always wear safety glasses. l When working with heated objects, always wear gloves. l No running or horseplay.
The Welding/Cutting Torch Objective 25.0 Demonstrate proper procedures for oxyacetylene processes.
Oxygen And Acetylene Safety Rules to Live By. Acetylene Cylinders Acetylene is a very unstable gas that becomes dangerous in pressures that exceed 15psi.
Welding and Cutting Safety Safety Unit Lesson 5. Oxy-Fuel Welding & Cutting Oxy-fuel welding and cutting are the most common causes of fires in the welding.
Electrical Safety. Why is it so important to work safely with or near electricity? The electrical current in regular businesses and homes has enough power.
1 Welding Module DISCLAIMER This material was produced under grant number SH from the Occupational Safety and Health Administration, U.S.
1. Compressed gases present a unique hazard. Depending on the particular gas, there is a potential for simultaneous exposure to both mechanical and chemical.
GRPE ISO GROUP MEETING, MUNICH, JANUARY 22th, 2003 GAS CYLINDERS USE OF PRESSURE RELIEF DEVICES Hervé BARTHELEMY AIR LIQUIDE PARIS.
© 2017 SlidePlayer.com Inc. All rights reserved.