We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byDonovan Guess
Modified over 2 years ago
© 2003 ABB STOTZ-KONTAKT GmbH Gerd Schlag Folie 1 AN INTRODUCTION TO DALI
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 2 What is DALI ? (1) The subject DALI is a synonym for a standard, independent of the manufacturer to control electronic ballast devices (ebd`s) and lamps the digital way
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 3 This standard (DALI) is supported by the worldwide leading manufacturers of ebd`s since There is a working group ( Activity Group DALI – ag.org) to establish the DALI Standard.www.dali- ag.org Since October 2003 ABB Stotz Kontakt is a member of AG DALI and therefore authorised to assemble and sell DALI compatible devices with DALI Logo. Members of working group AG DALI: ABB, BAG, CEAG, DELMATIC, DIAL, ECKERLE, ERC, ERCO, ETAP, GEWISS, GITRONICA, HADLER, HELVAR, HÜCO, INSTA, JOHANSON CONTROLS, LIGHTOLIER, LUTRON, LUXMATE, MAY&CHRISTE, NIKO, OSRAM, PHILIPS LIGHTING, SANDER, TRIDONIC, TROLL, UNIVERSAL LIGTHING TECHNOLOGIES, VOSSLOHGIES, VOSSLOH-SCHWABE, WILA What is DALI ? (2)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 4 What is DALI ? (3)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 5 Task of working group DALI - worldwide adoption of DALI - Securing the convertibility of DALI devices - Support of application of DALI No Certification or Registration of DALI devices necessary DALI Logo indicates the compatibility of DALI components DALI is a stand-alone System. It is a digital control and a subsystem for lighting technology and not a bussystem Specification is documented in DIN IEC What is DALI ? (4)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 6 DALI is a digital interface in lighting technology, used as a subsystem in building technology It is supported by all manufacturers of electronic ballast devices (ebd`s) A standard independent of the manufacturer Specification is documented in DIN IEC DALI - the Standard for Lighting Technology
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 7 DALI is more and more in use in non residential buildings Modern and smart Lighting technology is with DALI feasible, including coulored light For all types of lamps (e.g. halogen lamps, fluorescent lamps, bulbs, LEDs) are appropiated ballast devices available The product range of DALI components will extend on L&B 2004 DALI-Gateways for superior building installation systems like EIB / KNX, LON... are available Where is DALI today (1)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 8 Architects for Illumination accept DALI as ideal tool for lighting technology DALI is specified in many cases for Light moods (e.g. Doctor`s surgery) Light effects (e.g. Show rooms) Functional Light control (e.g. Office buildings) Supervision (e.g. Building with Facility-Management) Where is DALI today (2)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 9 2 wires cable – no polarity The DALI control line can be installed together with mains cable (e.g. by using a 5 wires standard cable) L N DALI DALI Technology (1)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 10 DALI relates to DIN IEC 60929, which defines a digital dim interface for elektronic ballast devices (ebd`s). Standardised is: Technical items (Current, Voltage, Timing...) Data protocol Test conditions for ebd`s DALI Technology (2)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 11 Technical Data Data speed 1200 Baud (Bit/Sek.) Master-Slave System without collision control Control line with 2 wires Interface voltage 16V (9,5V bis 22,5V) Interface current 250mA DALI devices needs max. 2mA No SELV – no special cable needed max. 64 DALI components in one system Up to 16 groups Up to 16 light scenes DALI Technology (3)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 12 Functionality Switching (ON/OFF) Set of brightness values Dimming via logarithmic characteristic curve (like human eye) Fading times for scenes Control of individual devices or groups Synchronised dimming of all components Simultaneous control of all devices (Broadcast-Mode) max. / min. Dimming limits) Status feedback (Lamp on/off, topical Brightness value, Lamp-, ebd fault) Operation with emergency power DALI Technology (4)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 13 The Intelligence of DALI is not centralised. A lot of adjustments and brightness values are stored in the EBD Individual adress Assignment to groups Light scenes Speed of Dimming Switch on brightness in case of voltage recovery Brightness value in case of emergency power supply DALI Technology (5)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 14 Feedback of Lamp fault and EBD Status Feedback Device 100% Communication control unit => device: ok DALI control unit o.k. device DALI control unit Communication control unit => device: Dim up to 100% Communication control unit => device: Lamp fault DALI control unit Lamp fault Device
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 15 Address Group 1 Address 2Group 2 Address...Group... Address 63 Group 2 Address 64Group 16 System of DALI Control Adress Group Light scene 64 individual adresses each EBD
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 16 2 Addres Group 1 Addres 2Group 2 Address...Group... Address 63 Group 2 Addres 64Group 16 Adress Group Light scenes 16 individual groups each EBD System of DALI Control
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 17 3 Adress Group 1 Address 2Group 2 Address...Group.... Address 63 Group 2 Address 64Group 16 Adresses Groups Light scenes Up to 16 Light Scenes in each EBD S3 S2 S3 System of DALI Control
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 18 Benefits of DALI vs. other Lighting System (1...10V) VDALI Potential free control input 2 wires control line Controlled by bussystems (EIB or others) Dimming range 1…100%, linear characteristic curve No feedback No adresses Potential free control input 2 wires control line Controlled by bussystems (EIB or others) Dimming range 1…100%, logarithmic characteristic curve Individuell feedback Group-, individual- and Broadcast adresses Memory for Scenes Programmable Dim times Synchronized Dimming Integrated Relays (ON/OFF)
© 2003 ABB STOTZ-KONTAKT GmbH G. Schlag- Folie 19
A Specifiers View of DALI June 4, :00 PM Seminar #18 Richard Miller, PE, LC Hellmuth, Obata + Kassabaum, Inc. Sponsored by The International Association.
Is it Time to Get a DALI? Brian Liebel, PE, LC AfterImage + s p a c e Rick Miller, PE, LC RNM Engineering.
Taking the Byte out of Bits: Lighting Design, Installation, and Operation in the Digital Age Seminar #21 May 7, :00 PM Richard Miller – RNM Engineering.
Masterclass 2001: Safety Integrated Excellencein Automation&Drives: Siemens Folienthema/Folie 1/Jahreszahl Name & Department AS-Interface Safety now included!
| 1 © 2013 Universal Lighting Technologies ULT Marketing Converting from T12 to T8 or T5 Efficiency Upgrades Presented by: Your Name HERE.
The I 2 C Bus. 2 of 40 The I 2 C Bus What is the I 2 C Bus and what is it used for? Bus characteristics I 2 C Bus Protocol Data Format Typical I 2 C devices.
1 Uniflair pCO1 Small / Medium. 2 1.Introduction …………………………… page 03 2.Technical features …………….………………………..page 07 3.Application.
DALI Installation: A Case Study LightFair Seminar 22 May 8, :30 AM Owner - HOK Daryl Dalling - Dynalectric Pete Horton – The Watt Stopper Richard.
L ON W ORKS Network Design Overview. Welcome! 1-2.
Network+ Guide to Networks 5 th Edition Chapter 6 Network Hardware.
LED Drivers Al Marble Manager, Sales & Market Development January 2010.
PRESENTATION iNELS. CHARACTERISTICS i: iNELS ® is a smart wiring system designed especially for: switching dimming control and measurement.
1 Product Overview. Klik om de opmaak van de overzichtst ekst te bewerken Tweede overzich tsnivea u Derd e over zicht snive au Vi er d e ov er zi.
UBI >> Contents Chapter 14 Communications Introduction MSP430 Teaching Materials Texas Instruments Incorporated University of Beira Interior (PT) Pedro.
Automation and Drives QUADLOG DP/IO Bus Link 1 Copyright © Siemens AG 2009 All Rights Reserved Features & Benefits DP/IO Bus Link Architectures Ordering.
Doc.: IEEE /0653r0 Submission July 2003 Andy Gowans - UK RA Update from UK (DVB and DTG) on Wireless Home Networking Projects Andy Gowans Private.
Automation and Drives Safety at Work AS-i SIGNUM Extension Plug Low Voltage Switchgear Burns Master Configuration K60 ATEX Analogue modules Analyser.
KNX Association ETS4 for Experts December KNX Association Page No. 2 October 2010 KNX: The worldwide STANDARD for home & building control 3. Its.
Fostering worldwide interoperabilityGeneva, July 2009 ETSI Green Agenda Jonas SUNDBORG ETSI Board Vice Chairman, ETSI OCG Chairman, ETSI Green Agenda.
Advanced HAI Lighting Control (HLC) May As a courtesy to all, please set your cell phones to silent. There will be a break to return phone calls.
Chapter 4 Internet Architecture. Awad –Electronic Commerce 1/e © 2002 Prentice Hall 2 OVERVIEW What is a Network? IP Addresses Networks Information Transfer.
2694 Bishop Drive, Suite 275 San Ramon, CA
National and Regional ITS Architectures Courtesy of Bart Cima, IBI Group.
Interface Products Business Line System Management Product Line Designing with I2C Fm+ January 2014 Peter Stonard – Applications Engineer.
Teldat Security VisorALARM & MIP Alarm transmission over IP networks.
©Ian Sommerville 2000 Software Engineering, 6th edition. Chapter 2Slide 1 Chapter 2 Computer-Based System Engineering.
Digital Alarm Annunciator with event recorder. Description Alarm annunciator for use with all types of digital inputs that provide a voltage signal. Features.
© ABB STOTZ KONTAKT ABB MCB Tripping – Characteristics MCB´s Knowhow ABB STOTZ KONTAKT.
XFEL 2D Pixel Clock and Control System Train Builder Meeting, DESY 22 October 2009 Martin Postranecky, Matt Warren, Matthew Wing.
1 EC Fans. 2 Leonardo Evolution units offer the possibility to choose between two different types of Backward Curved Fans: Standard Asynchronous Fans.
© 2016 SlidePlayer.com Inc. All rights reserved.